# VLT 2000 Series. How to size your VLT

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 Selection of frequency converter Usually the size of frequency converter is chosen on the basis of the shaft output, as this may be the only value known. However, if the data are known for both the application, the motor and the frequency converter, it is recommended to make a more accurate sizing. The values must be based on the rated motor speed. VLT 2000 only operates according to the CT (constant torque) characteristic Sizing on the basis of the apparent power S M [kva] consumed by the motor Exercise A motor must yield constant torque at continous operation. Usually the necessary values will appear from the motor plate or from the motor catalogue. Solution From the table on the next page you can see that VLT type 2025 can yield 2.0 kva (415 V) at continuous operation. The solution is therefore VLT type Sizing when you know the motor current Exercise Conveyor plant with a 1.1 kw, V motor. At continuous operation the motor current is 2.5 A ( V). Solution From the table on the next page you can see that a VLT type 2025 can yield 2.8 A at continuous operation. The right solution is therefore VLT Read values Motor current = 2.5 A (3 415 V) s M = U I [kva] = [kva] 1000 = 1.8 kva Sizing on the basis of the power requirement P VLT [kw] of the motor Exercise A machine tool is driven by a 3 kw motor. The power requirement is indicated to be 2.4 kw. The motor efficiency η is 0.80, cos ϕ = 0.81 and the motor voltage is 3 x 415 V. η and cos ϕ are measured at 3 kw output. We estimate η and cos ϕ to be approximately the same at 80 % load. Solution From the table on the next page you can see that VLT type 2040 can yield 4.0 kva (415 V) at continuous operation. The right solution is therefore VLT type S VLT = P m η cos ϕ = 2.4 kw = 3.7 kva 30 MG.20.B6.02 VLT is a registered Danfoss trademark

2 Which one to choose? Mains: 1 220/230/240 V, 3 208/220/230/240 V VLT type Typical shaft output Constant output current I VLT,N Constant output power at 230 V [kw] [A] [kva] *) *) *) VLT types 2040 and 2050: only three-phase mains supply. Mains: 3 380/400/415/440/460 V *) VLT type Typical shaft output Constant output current I VLT,N Constant output power at 415 V [kw] [A] [kva] *) *) VLT type 2060: 3 380/400/415 V Section 1 Section 2 Section 3 MG.20.B6.02 VLT is a registered Danfoss trademark 31

3 Product range The VLT 2000 Series is available in a single-phase/ three-phase version (1 x V or 3 x V) in the power range kw and a three-phase version (3 x V) in the power range kw. A three-phase version (3 x V) in the power range kw is also available. All units are delivered in an IP 20 enclosure. How to find the right code number When you have found the right VLT size you can find the code number to be ordered in the table below. Example: VLT type 2020 (3 x V) three-phase without display with brake has the code number 195H3400. As appears from the table a VLT 2000 single/three phase can be delivered with various options and modules such as brake function, RFI filter and motor coils. VLT 2000 Series, single-phase/three-phase ( V / V) (3 x V) VLT 2010 VLT 2015 VLT 2020 VLT 2030 VLT 2040 VLT 2050 Without display 195H H H H H H3110 With display 195H H H H H H3111 Without display with brake 195H H H H H H3210 With display with brake 195H H H H H H3211 RFI and motor filter module 195H H H H6525 IP 20 1-phase RFI and motor filter module 195H H H H6522 IP 20 3-phase RFI-filtermodul IP 20 (VBG-4)* H H6528 Motor coil module IP H H H H6510 Motor coil module IP 10 (VBG-4) 195H H H H6521 LC and RFI filter module 195H H H H6526 IP 20 3-phase * Schaffner RFI-filter type FN351-16/29 VLT 2000 Series, three-phase (3 380/460 V). Note: VLT 2060: 380/415 V VLT 2020 VLT 2025 VLT 2030 VLT 2040 VLT 2050 VLT 2060 Without display 195H H H H H H3310 With display 195H H H H H H3311 Without display with brake 195H H H H H H3410 With display with brake 195H H H H H H3411 RFI and motor filter module IP 20** 195H H H H H H6522 Motor coil module IP 10 (VBG-4) 195H H H H H H6521 LC and RFI filter module IP 20** 195H H H H H H6526 **Only 380/415 V 32 MG.20.B6.02 VLT is a registered Danfoss trademark

4 VLT 2000 Series built-in RFI filter EN A: VLT Series 2000, single-phase (1 x V) VLT 2010 VLT 2015 VLT 2020 VLT 2030 Without display 195H H H H3606 With display 195H H H H3607 Without display / With brake 195H H H H3706 With display / with brake 195H H H H3707 Motor coils, IP20, three-phase 195H H H H6529 VLT Series 2000, three-phase (3 x V) VLT 2020 VLT2025 VLT2030 VLT 2040 VLT 2050 VLT 2060 Without display 195H H H H H H3810 With display 195H H H H H H3811 Without display / With brake 195H H H H H H3910 With display / with brake 195H H H H H H3911 Motor coils, IP20, three-phase 195H H H H H H6529 The VLT 2000 with built-in RFI filter in IP 20 enclosure, is designed to be built directly into control panels., EMC demands are fulfiled without any extra component. - RFI filter to reduce electromagnetic interference. - The VLT 2000 units meet all necessary EMC VLT 2000 Series built-in compact RFI filter For technical data, see page 12. VLT Series 2000, single-phase (1 x V) VLT 2010 VLT 2015 VLT 2020 With display / without brake 195H H H3114 Accessories/options to the VLT Series 2000: Remote control (option) 175H1788 PC program (VLS Dialog 2)(Danish Danish) 175H2877 PC program (VLS Dialog 2)(English English) 175H2850 PC program (VLS Dialog 2)(German German) 175H2876 Brake function All units can be delivered with built-in brake function (factory-mounted). The brake resistors for the brake function must be connected according to the connection diagram on page 42. immunity standards as laid down in the IEC The VLT 2000 units meet the EMC emission requirements as laid down in the EN 55011, Group 1 Class A. The EMC emission specifications are complied with by using up to 40 m unscreened cable, see page 88. Specifications VLT VLT VLT VLT V V V V Max. current 5.5 A 16 A 5.5 A 7.5 A Min. brake voltage 372 V DC 372 V DC 747 V DC 646 V DC Max. brake voltage 382 V DC 382 V DC 764 V DC 661 V DC P-band 4 V 8 V 8 V 8 V Overcurrent fuse None None None None Min. brake resistance 70 Ohm 25 Ohm 140 Ohm 90 Ohm Section 1 Section 2 Section 3 MG.20.B6.02 VLT is a registered Danfoss trademark 33

5 Motor coils (module) The IP 20 enclosure (also with mains filter) is available with integrated motor coils or as an IP 00/IP 10 module for external mounting. Motor coils in IP 00 and IP 10 enclosure contain only one motor coil, making it possible to use long motor cables up to 300 m. These motor coils must be installed separately (not for co-building with the VLT frequency converter). Technical data V/IP V/IP V/IP V/IP 10 Max. current 3 2.2/4.0/7.5 A A A 3 10 A Max. cable length (unscreened) 150 m 300 m 150 m 300 m Max. cable length to fullfill EN 55011, Group 1, Class A100 m m - Unscreened Max. cable length (screened) 75 m 150 m 75 m 150 m Inductance 3 75 µh 75 µh 120 µh 240 µh Outside dimensions 100x110x180 mm - 100x110x180 mm - Code no. 195H6523,6524, H H H6521 Additional litterature: MI.20.CX.02 - Moter coil, IP 10 MI.20.BX.52 - Moter coil, IP 00 MD.65.BX.XX - Brake resistors RFI and motor filter (module) The RFI and motor filter module in IP 20 enclosure is designed to be built in with the VLT frequency converter itself. The filter contains the following: - RFI filter to reduce electro-magnetic interference. - Motor coils making it possible to use long motor cables. - Motor filter (motor RFI filter) to reduce the electromagnetic interference from the motor cable. LC and RFI filter (module) The LC and RFI filter module in IP 20 enclosure is designed to be built in with the VLT frequency converter itself. The filter contains the following: - RFI filter to reduce electro-magnetic interference - LC filter to reduce the acoustic noise level from the motor and make it possible to use long motor cables up to 300 m. - Motor filter (motor RFI filter) to reduce the electromagnetic interference from the motor cable. The VLT 2000 Series basic units meet EMC immunity requirements as laid down in the IEC standards, but do not meet any EMC emission requirements. Equipped with the IP 20 RFI and motor filter (195H6522, 195H6523, 195H6524, 195H6525), the VLT 2000 Series meets the EN 55011, Group 1, Class A requirements of EMC emission. The EMC emission specifications are complied with by using up to 100 m unscreened motor cable. Equipped with the IP 20 LC and RFI filter (195H6526 and 195H6527), the VLT 2000 Series meets the EN 55011, Group 1, Class A requirements of EMC emission. The EMC emission specifications are complied with by using up to 100 m unscreened motor cable. Code nr. 195H H6526 VLT basic unit VLT 2020, 2025, 2030 VLT 2040, 2050, 2060 Enclosure IP 20 IP 20 Outside dimensions (H x W x D) 170 x 110 x 180 mm 170 x 110 x 180 mm Built-in fan Yes No Mains voltage V V Current (max.) 4.0 A 9.7 A Cut-out frequency No limit No limit EMC immunity IEC 801 Series IEC 801 Series EMC emission EN Group 1, Class A EN Group 1, Class A Max. cable length to fullfill EN 55011, Group 1, Class A 100 m 100 m Unscreened Max. temperature (full load) 40 C 40 C 34 MG.20.B6.02 VLT is a registered Danfoss trademark

6 Dimensions VLT VLT built-in compact RFI filter single-phase, V/three-phase, V single-phase, V converters: 100 mm mounting). VLT with module With 100 mm module: With 170 mm module: A = 362 mm a = 337 mm A = 432 mm a = 407 mm converters: 100 mm. mounting). single-phase, V/three-phase, V Section 1 Section 2 Section 3 MG.20.B6.02 VLT is a registered Danfoss trademark 35

7 Dimensions (cont d) VLT VLT three-phase, /460 V three-phase, V converters: 100 mm. mounting) VLT with module three-phase, /460 V with 100 mm module: With 170 mm module: A = 462 mm a = 437 mm A = 532 mm a = 507 mm converters: 100 mm. mounting) 36 MG.20.B6.02 VLT is a registered Danfoss trademark

8 Dimensions (cont d) VLT with built-in RFI filter, single-phase, V converters: 100 mm. mounting) VLT with built-in RFI filter, three-phase, V converters: 100 mm. mounting) Section 1 Section 2 Section 3 MG.20.B6.02 VLT is a registered Danfoss trademark 37

9 Technical data Mains: 1 220/230/240 V, 3 208/220/230/240 V 3 x 208/220/230/240 V Meets the international standards, UL/ cul 4 ) VLT type Constant load (CT): Output current I VLT.N [A] I VLT.MAX [A] (60 s) Output S VLT.N [kva] S VLT.MAX [kva] (60 s) Typical shaft output P VLT.N [kw] Max. cable cross section [mm 2 ] Max. motor cable length [m] 40 (with motor coils IP 10: unscreened cables 300 m, screened cables 150 m) Output voltage U M [%] 0-100% of mains voltage Output frequency f M [Hz] or 0-500; programmable Rated motor voltage U M,N [V] 200/208/220/230/240 Rated motor frequency f M,N [Hz] 50/60/87/100 Thermal motor protection during operation Built-in thermal motor protection (electronic) Switching on the output Unlimited (frequent switching may cause cut-out) Ramp times [s] VLT type Max. input current I L,N [A] (5.3/3.5) (8.5/5.6) (10.6/7.1) (18/12) (-/10) (-/16) Max. cable cross section [mm 2 ] Max. prefuses [A] Bussmann Fuse type KTN-R 250 V AC 5 ) [A] Mains supply voltage [V] 1 x 220/230/240 ±10 % 3 x 208/220/ 3 208/220/230/240 ±10 % 230/240±10 % Mains supply frequency [Hz] 50/60 Power factor/cos. ϕ 1 Without mains filter:0.50/ / /1.0 With mains filter:0.65/1.0 Efficiency >0.94 at rated load Switching on the input times/min. 5 VLT type Weight [kg] IP Weight [kg] with built-in RFI filter IP Power loss at max. load CT [W] Enclosure IP 20 IP 20 IP 20 IP 20 IP 20 IP 20 Vibration test [g] 0.7 Relative humidity [%] Max. 95 IEC 721 (according to VDE 0160) Ambient temperature [ C] at full-load operation 2 ) (according to VDE 0160) [ C] , storage/transport Frequency converter protection Grounding and short-circuit proof 3 ) EMC applied standards Emission EN 55011, Group 1, Class A, (see page 90) CISPR 11 (with RFI and motor filter) Immunity IEC UL file-number E ) In the range C the unit can start and run, but the display indications and certain operating characteristics will not meet the specifications. 3 ) Brake option without protection 4 ) Units with built-in RFI filter are not UL-approved. 5 ) For the North American market 38 MG.20.B6.02 VLT is a registered Danfoss trademark

10 Technical data (continued) Mains: V (VLT type 2060: V) Meets the international standards, UL/cUL 4 ) VLT type ) Constant load (CT): Output current I VLT.N [A] I VLT.MAX [A] (60 s) Output S VLT.N [kva] S VLT.MAX [kva] (60 s) Typical shaft output P VLT.N [kw] Max. cable cross section [mm 2 ] Max. motor cable length [m] 40 (with motor coils IP 10: unscreened cables: 300 m, screened cables: 150 m) Output voltage U M [%] in % of mains voltage Output frequency f M [Hz] or 0-500; programmable Rated motor voltage U M,N [V] 380/400/415/440/460 Rated motor frequency f M,N [Hz] 50/60/87/100 Thermal motor protection during operation Built-in thermal motor protection (electronic) Switching on the output Unlimited (frequent switching may cause cut-out) Ramp times [s] VLT type ) Max. input current I L,N [A] Max. cable cross section [mm 2 ] Max. prefuses [A] Bussmann Fuse type KTN-R 250 V AC 5 ) [A] Mains supply voltage [V] V ±10% 2060: V ±10% Mains supply frequency [Hz] 50/60 Power factor/cos. ϕ 1 > 0.90/1.0 at rated load Efficiency > 0.97 at rated load Switching on the input times/min. 5 VLT type ) Weight [kg] IP Weight [kg] with built-in RFI filter IP Power loss at max. load CT [W] Enclosure IP 20 IP 20 IP 20 IP 20 IP 20 IP 20 Vibration test [g] 0.7 Relative humidity [%] Max. 95 IEC 721 (according to VDE 0160) Ambient temperature [ C] 0 +40, at full load operation 2 ) (according to VDE 0160) [ C] , storage/transport Frequency converter protection Grounding and short-circuit proof 3 ) EMC applied standards Emission EN 55011, Group 1, Class A (see page 90) CISPR 11 (with RFI and motor filter) Immunity IEC UL file no. E ) VLT 2060 has not been UL approved. 2 ) In the range C the unit can start and run, but the display indications and certain operating characteristics will not meet the specifications. 3 ) Brake option without protection Section 1 Section 2 Section 3 4 ) Units with built-in RFI filter are not UL-approved. 5 ) For the North American market MG.20.B6.02 VLT is a registered Danfoss trademark 39

### Prewired position switches FA series

2 Prewired position switches FA series Selection diagram 01 08 10 11 1 15 1 02 external rubber gasket external rubber gasket 1 51 52 54 55 56 5 ACTUATORS adjustable lever safety adjustable lever 41 45

### TECHNICAL DESCRIPTION

TECHNICAL DESCRIPTION Exhaust Hose Reel ser. 865, electric motor driven No. 981118101 Description Limit switches, for hose coiling and uncoiling integrated in drive unit. Motor turns drum via a planetary

### Position switches FP series

A Position switches FP series Selection diagram 0 08 8 9 0 0 0 Ø 8 mm Ø, mm external rubber stainless steel stainless steel fiber glass rod gasket sphere sphere adjustable lever safety adjustable lever

### Prewired position switches FA series

Prewired position switches Technical data Housing Made of metal, coated with baked epoxy powder 2 m wired cable with 5x0,5 mm 2 wires marked SEV and IMQ Protection degree: IP6 General data Ambient temperature:

### Evaporating Pressure Regulating Valve Type KVQ REFRIGERATION AND AIR CONDITIONING. Technical leaflet

Evaporating Pressure Regulating Valve Type KVQ REFRIGERATION AND AIR CONDITIONING Technical leaflet Contents Page Introduction...3 Features...3 Technical data...4 Ordering...4 Sizing...5 Valve selection...5

### Pressure switch KP-E. Data sheet

Data sheet Pressure switch KP-E KP-E pressure switches for use in refrigeration and air conditioning systems are equipped with SPDT gold plated contacts and stainless steel bellows. The high pressure switches

### Gas density monitor With integrated transmitter Model GDM-100-TI

SF 6 gas solutions Gas density monitor With integrated transmitter Model GDM-100-TI grid Products WIKA data sheet SP 60.05 for further approvals see page 5 Applications Gas density monitoring of closed

### Pressure switch Type BCP

Data sheet Pressure switch Type BCP The BCP type is a series of dedicated switches for safety and monitoring of steam and hot water boilers. The BCP incorporates a single-pole changeover microswitch where

### Differential pressure controls, Type MP 54, 55 and 55A

MAKING MODERN LIVING POSSIBLE Technical brochure Differential pressure controls, Type MP 54, 55 and 55A MP 54 and oil pressure controls are used as safety switches to protect refrigeration compressors

### Limit switches OsiSense XC Special For material handling applications, type XC1 AC

Presentation For material handling applications, type XC C b XC C with slow break contacts v With head for linear movement () 00_ 00_ 000_ Page / 00_ 00_ XCC XCC Page / XCC XCC / General characteristics

### TeSys protection components

Presentation, description -pole thermal overload relays TeSys D Presentation TeSys D thermal overload relays are designed to protect a.c. circuits and motors against: b overloads, b phase failure, b excessively

### EPP4 Pressure Regulator Basic G 1/4"

EPP4 Pressure Regulator Basic G 1/4" Flow Curve 1/4" Dimensions Outlet pressure - bar 9 8 7 6 5 4 3 2 1 0 0 20 40 60 70 80 100 120 Flow rate - Nm 3 /h The male connector adopted on the EPP4 is a standard

### Operating instructions Safety Rope Emergency Stop Switches ZB0052 / ZB0053 ZB0072 / ZB0073

Operating instructions Safety Rope Emergency Stop Switches UK ZB0052 / ZB0053 ZB0072 / ZB0073 7390878 / 02 03 / 2011 Contents 1 Safety instructions...3 2 Installation / set-up...4 2.1 Applications...4

### Differential pressure switch MP 54, MP 55 and MP 55A

Data sheet Differential pressure switch MP 54, MP 55 and MP 55A MP 54 and MP 55 oil differential pressure switches are used as safety switches to protect refrigeration compressors against low lubricating

### Data sheet Pressure switch type CS December 2001 DKACT.PD.P10.A B1119

Pressure switch type CS December 2001 DKACT.PD.P10.A2.02 520B1119 Introduction Pressure switch type CS is part of the Danfoss pressure control range. All CS pressure switches have a built-in pressure-operated,

### Differential Pressure Control Types MP 54, MP 55 and MP 55A

MAKING MODERN LIVING POSSIBLE Data sheet Differential Pressure Control Types MP 54, MP 55 and MP 55A MP 54 and MP 55 oil differential pressure controls are used as safety switches to protect refrigeration

### HYBRID STEPPING MOTORS HY / HS / HN Series

HYBRID STEPPING MOTORS HY / HS / HN Series Long Life Compact Design Bipolar / Unipolar Models Holding Torque up to High Performances Series HS and HN Several Options available (Encoders, Gearboxes,Cables,

### ASM. Asynchronous Spindle Motors. SEM Limited Faraday Way Orpington, Kent BR5 3QT United Kingdom

NE ASM Asynchronous Spindle Motors SEM Limited Faraday Way Orpington, Kent BR 3QT United Kingdom Tel: +44 ()189 8847 Fax: +44 ()189 884884 Email: sales@sem.co.uk Web: www.sem.co.uk Version 4 August 2 Asynchronous

### Watts. xppower.com. Input. General. Environmental. Output. EMC & Safety. Output Voltages from 2.5 V to 48 V. Non-standard Outputs Available

-0 Watts AEH Series s from. V to 8 V xppower.com Non-standard s Available Universal Input Single & Multiple Versions 0 C to +60 C Operating Temperature Efficiency up to 80% Non-standard Connectors Available

### WF STEUERUNGSTECHNIK GMBH. INFORMATION and TECNICAL DESCRIPTION

1 INFORMATION and TECNICAL DESCRIPTION 14 2 AIRLEADER Professional Compressor Management + Compressed Air Visualisation + Alarm Service Management + AIRLEADER - has been the effective answer for compressed

### Solenoid valve type EVR for Hydrocarbons

MAKING MODERN LIVING POSSIBLE Technical brochure Solenoid valve type EVR for Hydrocarbons EVR for Hydrocarbons is a direct or servo operated solenoid valve especially designed for liquid, suction, and

### Miniature controls. Contactors. Overload relays. Starters. Control relays

Contactors Overload relays Starters Control relays Description General features Wiring terminations available include plugon connectors, wire pins for PC board mounting and solder connections Low power

### Level transmitter LT 100

KROHNE 09/2001 7.02363.21.00 GR/PRINTO Level transmitter LT 100 Status: 10/99 Variable area flowmeters Vortex flowmeters Flow controllers Electromagnetic flowmeters Ultrasonic flowmeters Mass flowmeters

### Dimensions. Technical Data General specifications Switching element function DC Dual NC Rated operating distance s n 3 mm

Dimensions 65 GW2 40 35 9 5 GW1 14 11 9 5.4 M20 x 1.5 0102 Model Number S M12 x 1.5 Features 77.5 LED V Direct mounting on standard actuators Compact and stable housing with terminal compartment connection

### TABLE OF CONTENTS 2 TALAS DRYER 4 TALAS MEASURER 7 TALAS PORTABLE DRYER 9 TALAS LEAKER 11 TALAS STARTER 14 TALAS AUXILIARY 17 APPENDICES

TABLE OF CONTENTS 2 TALAS DRYER 4 TALAS MEASURER 7 TALAS PORTABLE DRYER 9 TALAS LEAKER 11 TALAS STARTER 14 TALAS AUXILIARY 17 APPENDICES ALL PICTURES SHOWN ARE FOR REFERENCE ONLY ACTUAL PRODUCT MAY VARY

### Electric regulating valves Type CCMT 2 - CCMT 8 / CCMT 16 - CCMT 42

Data sheet Electric regulating valves Type CCMT 2 - CCMT 8 / CCMT 16 - CCMT 42 The CCMT is an electrically operated valve designed specifically for operation in CO 2 systems. The CCMT valve concept is

### Technical leaflet. Pressure and Temperature Regulators. January 1999 RC.4X.B1.22. Danfoss A/S

Technical leaflet Pressure and Temperature Regulators January 1999 RC.4X.B1.22 Danfoss A/S 01-99 1 Pressure and Temperature Regulators Contents Evaporator Pressure Regulators Page Type KVP... 3 Type PKV/PKVS...

### PLEASE READ CAREFULLY BEFORE INSTALLING OR USING MEGA POOL SAVER MPS 1100

MPS-1100 User Manual Mega Pool Saver Ltd PLEASE READ CAREFULLY BEFORE INSTALLING OR USING MEGA POOL SAVER MPS 1100 For further up to date instructions on how to install Mega Pool Saver MPS 1100, please

### Digital electro-pneumatic regulators Series ER100

CATALOGUE > Release 8.2 Digital electro-pneumatic regulators Series ER100 TREATMENT > Digital electro-pneumatic regulators Series ER100 Port G1/4» Compact design» Digital display» Analog and digital input»

### JUMO dtrans p30 Pressure Transmitter

609 Fulda, Germany Postal address: 605 Fulda, Germany Phone: +49 661 600-0 Fax: +49 661 600-607 Phone: +44 179 6 55 Data Sheet 40466 Page 1/6 JUMO dtrans p0 Pressure Transmitter General application Pressure

### Engineering Data RPM: 3000 HP: Serv. Factor: 1,0 KW:,37 Form Factor: 1,00 Amps: 20 KW2: Form Factor 2: FLA2: Volts: 24. Frame: 71D

Product Features Catalog No: L085/O043/098066.00 Model: CI42D34FT7C Engineering Data RPM: 3000 HP: Serv. Factor: 1,0 KW:,37 Form Factor: 1,00 Amps: 20 KW2: Form Factor 2: FLA2: Volts: 24 Frame: 71D Max

### 2-Phase Filters(Direct IEC Connector) RoHS. 250V AC 50/60Hz 1,2,3,6,10A KC, UL, CSA, VDE+ENEC, TÜV, CQC, 25 / 85 / 21

2-Phase Filters(Direct IEC Connector) IG IM IL IX ID Rated Voltage/ Frequency 1,2,3,6,10A KC, UL, CSA, VDE+ENEC, TÜV, CQC, Climatic Category IG, IX, ID : IM, IL : Plastic Case IG, IX, ID : Screw and PCB

### Circuit breakers PR 60

Circuit breakers PR series are mechanical switching devices able to switch, conduct and switch-off the current under normal conditions and able to switch, conduct and automatically switch-off the current

### Electro-Pneumatic Converter YT-940 SERIES

Electro-Pneumatic Converter YT-940 SERIES PRODUCT MANUAL VERSION 1.00 Contents 1. Introduction 3 1.1 General information for the users. 3 1.2 Manufacturer Warranty 3 1.3 Explosion Proof Warning. 4 2. Product

### Meta-MEC Manual Motor Starters

www.lsis.biz Meta-MEC Manual Motor Starters LS Meta-MEC Manual Motor Starters provide completed ranges up to 100A 45 mm 55 mm 32AF 2 45 mm 70 mm 63AF 100AF 3 LS Meta-MEC Manual Motor Starters deliver more

### Pressure switches for air and water CS

Data sheet Pressure switches for air and water CS CS pressure switches have a built-in pressure operated, three-pole switch. The contact position of which depends on the pressure in the connector and the

### IPH 2 & IPX 2. Features Type 4X & Explosion-Proof Current-to-Pressure (I/P) Transmitters. Approved for Use with Natural Gas.

February 2018 Description These 2-wire (loop-powered) I/P transmitters accept a current signal (such as 4-20mA) from a DCS, PLC or PC-based control system. They convert the current signal to a pneumatic

### RP series Rotor Pumps

ontact etails RP series Rotor Pumps Nomenclature Features Low noise Substantial reduction of the operation noise, by to db (comparison with aikin products), and improved sound quality are achieved by adopting

### The Limit Switch with Better Seal, Shock Resistance, and Strength. General-purpose Limit Switch. Model Number Structure

General-purpose Limit Switch CSM_DA-_N_DS_E The Limit Switch with Better Seal, Shock Resistance, and Strength A double seal on the head, a complete gasket cover, and other features ensure a better seal

### FMAC Sine FMAC Sine DCL

emc Sine Output Filter www.schurter.com/pg8 FMAC Sine FMAC Sine DCL -Phase Filters Sine wave output filter Description - Design corresponding to UL 128, CSA 22.2 No. 8, IEC/EN699 - Standard versions include

### Solenoid gas valve. The solenoid gas valve is also applicable as a main gas valve Pilot gas valve for forced draft burners

7 634 VGS1... with AGA67 connector VGS2... with AGA67 connector Solenoid gas valve VGS The solenoid gas valve is also applicable as a main gas valve Pilot gas valve for forced draft burners The VGS and

### LMP 307. Stainless Steel Probe. Stainless Steel Sensor. accuracy according to IEC 60770: standard: 0.35 % FSO option: 0.25 % / 0.

LMP 07 Stainless Steel Sensor accuracy according to IEC 60770: standard: 0.5 % FSO option: 0.5 % / 0. % FSO Nominal pressure from 0... mho up to 0... 50 mho Output signals -wire: 4... 0 ma -wire: 0...

### SonoMeter 30 Energy Meters

Data Sheet SonoMeter 30 Energy Meters Description The Danfoss SonoMeter 30 is a range of ultrasonic, compact energy meters intended for measuring energy consumption in heating and cooling applications

### TOMAHAWK 1025 & 1538 OPERATOR S MANUAL IM /2016 REV06 ENGLISH

TOMAHAWK 1025 & 1538 OPERATOR S MANUAL IM2014 04/2016 REV06 ENGLISH Lincoln Electric Bester Sp. z o.o. ul. Jana III Sobieskiego 19A, 58-263 Bielawa, Poland www.lincolnelectric.eu Declaration of conformity

### KERN EG/EW Version /02

E KERN EG/EW Version 1.5 07/02 Operating Instructions Electronic Precision Balances Contents 1 TECHNICAL DATA... 20 2 UNPACKING AND STANDARD ACCESSORIES... 23 3 SETTING UP THE BALANCE... 23 4 EXTERNAL

### Sensor for Air Bubble Detection at Liquid Filled Tubes. SONOCHECK Type ABD06.xx. Operating Manual

Sensor for Air Bubble Detection at Liquid Filled Tubes SONOCHECK Type ABD06.xx Operating Manual Manufacturer: Model: Type: SONOTEC Ultraschallsensorik Halle GmbH Air Bubble Detector ABD06.xx SONOTEC Ultraschallsensorik

### Electric expansion valves Types AKV 10, AKV 15 and AKV 20

Data sheet Electric expansion valves Types AKV 10, AKV 15 and AKV 20 AKV are electrically operated expansion valves designed for refrigerating plants. The AKV valves are normally controlled by a controller

### A4 Operation Manual. Fig.1-1 Controller Socket Diagram

A4 Operation Manual Safety Instruction Please read this manual carefully, also with related manual for the machinery before use the controller. For installing and operating the controller properly and

### Protection of motor circuits

Protection of motor circuits Circuit breaker/contactor coordination A circuit supplying a motor may include one, two, three or four switchgear or When a number of devices are used, they must be coordinated

### Tightness controls TC 1 3 and TC 4

Tightness controls TC 1 3 and TC 4 Test of both safety valves Short test period thanks to logical decision-making in the program sequence Adjustable test period which can be adapted to different systems

### Pressure switch and Thermostat CAS

Data sheet Pressure switch and Thermostat CAS The CAS Series consists of a series of pressure controlled switches and temperature controlled switches. In this series, special attention has been given to

### ECL Comfort 110, application 131 (valid as of software version 2.00)

Operating Guide ECL Comfort 110, application 131 (valid as of software version 2.00) English version www.danfoss.com How to navigate? Adjust temperatures and values. Switch between menu lines. Select /

### HUMOR 20. High-precision Humidity Calibrator HUMOR 20. Operation

High-precision Humidity Calibrator The role of humidity calibrations that are accurate, reproducible, and documentable is becoming more and more important. ISO quality guidelines and regulations according

### Technical Data. Dimensions

0102 Model Number Features 10 mm flush Shielded PUR cable for oil and gas sector Accessories BF 30 Mounting flange, 30 mm Technical Data specifications Switching function Normally closed (NC) Output type

### better measurement Simply a question of SCHMIDT Flow Sensor SS The cost-effective alternative in pressurised systems up to 10 bars.

Simply a question of better measurement SCHMIDT Flow Sensor SS 20.261 The cost-effective alternative in pressurised systems up to 10 bars. Compressed air technology Industrial processes A cost analysis

### A4s Operation Manual

A4s Operation Manual Safety Instruction Please read this manual carefully, also with related manual for the machinery before use the controller. For installing and operating the controller properly and

### Pressure transmitters EMP 2

Data sheet Pressure transmitters EMP 2 The high accuracy pressure transmitter EMP 2 is designed for monitoring and control in marine and industial applications and offers a reliable pressure measurement,

### Differential pressure switch / Lube oil protection control MP 54 and MP 55

Data sheet Differential pressure switch / Lube oil protection control MP 54 and MP 55 MP 54 and MP 55 oil differential pressure switches are used as safety switches to protect refrigeration compressors

### Customer Responsibilities

Thank you for purchasing an Agilent instrument. To get you started and to assure a successful and timely installation, please refer to this specification or set of requirements. Correct site preparation

### Technical Data. Dimensions

0102 Model Number Features Comfort series 15 mm non-flush Stainless steel housing Accessories BF 30 Mounting flange, 30 mm Technical Data specifications Switching element function NAMUR, NC Rated operating

### Pressure Measurement Single-range transmitters for general applications

Siemens A 207 Overview Application The SITRANS P Compact pressure transmitter is designed for the special requirements of the food, pharmaceutical and biotechnology industries. The use of high-grade materials

### Level transmitters and indicators Series LU Ultrasonic level transmitter and indicator for liquids and solids

Level transmitters and indicators Series LU Ultrasonic level transmitter and indicator for liquids and solids No contact with the product Compact design with polycarbonate housing (electronics and display).

### Evaporator pressure regulator Type KVP

Data sheet Evaporator pressure regulator KVP The KVP is mounted in the suction line after the evaporator and is used to:. Maintain a constant evaporating pressure and thereby a constant surface temperature

### Aquavar SOLO 2 Frequently Asked Questions

Aquavar SOLO 2 Frequently Asked Questions How do I size the Aquavar SOLO 2 for the appropriate pump/motor combination? Can I use a 208 Volt motor? Can I run the Aquavar SOLO 2 up to 80HZ? What are the

### Visualize Nitrogen Gas Consumption

Air Flow Monitor EWA2 SERIES Conforming to EMC Directive (all models) & Pressure Equipment Directive (AEWA2150/2200 only) Visualize Nitrogen Gas Consumption Small pipe size as Well as Air Consumption!

### Programmable pressure and temperature transmitters PTM/RS485

Programmable pressure and temperature transmitters PTM/RS485 Version: 03-28-2012 Technical Specifications Pressure measuring range (bar) 0.1... 0.5 > 0.5 2 > 2 25 Overpressure 3 bar 3 x FS ( 3 bar) 3 x

### Pressure controls for hydro carbons, zone II applications, Type KPE

MAKING MODERN LIVING POSSIBLE Technical brochure Pressure controls for hydro carbons, zone II applications, Type KPE KPE pressure controls for use in refrigeration and air conditioning systems with hydrocarbons

### Technical information

Technical information 1.1 Design Elektror medium pressure blowers of the RD range are radial ventilators with double-wall impellers made from sheet aluminium respectively from sheet steel. They are directly

### Installation and Operation Manual

Manual Static pressure transducer with controller Differential static pressure transducer with analog output and optional PI control mode Large diaphragm element with differential transformer Transducer

### Ultrasonic level transmitter and indicator

Ultrasonic level transmitter and indicator No contact with the product Compact design with polycarbonate housing (electronics and display). Remote display available on request Very good resistance in corrosive

### SonoSelect 10 and SonoSafe 10 energy meters

SonoSelect 10 and SonoSafe 10 energy meters Description The Danfoss SonoSelect 10 and SonoSafe 10 are ultrasonic compact energy meters intended for measuring energy consumption in heating and cooling applications

### Customer Responsibilities

Thank you for purchasing an Agilent instrument. To get you started and to assure a successful and timely installation, please refer to this specification or set of requirements. Correct site preparation

### PRODUCT SPECIFICATION

MINI-FIT SR. SERIES 1.0 SCOPE This specification covers the 10.00 mm / (.394 in.) centerline tin and gold plated connector series, single and dual row versions in wire to wire and wire to printed circuit

### Programmable Submersible Level Transmitters

Programmable Submersible Level Transmitters PTM/N/RS485 CUSTOMER BENEFITS High flexibility due to scalalbe pressure range Digital (RS485) and analogue (4-20mA) output signal in one sensor Available as

### E2K-L. Liquid Level Sensor That Is Unaffected by the Color of the Pipe or Liquid. Liquid Level Sensor. Ordering Information

Liquid Level EK-L CSM_EK-L_DS_E 3 Liquid Level That Is Unaffected by the Color of the or Liquid Mount to bypass pipes. Fit a wide range of pipe diameters: 8 to mm or to mm Built-in Amplifiers to save space.

### 2/2-Way Solenoid Control Valve

2/2-Way Solenoid Control Valve Excellent range (1:200) Very good response Compact valve design Orifice sizes 0.05... 2.0 mm Port connection 1/8 or sub-base Type 2871 can be combined with Type 8605 Digital

### RS 2-75 D 109 D RSF 87 D 127 D with direct drive

Screw compressors RS 2-75 D 109 D RSF 87 D 127 D with direct drive Made in Germany Motor size: 75 127 kw RENNER GmbH Kompressoren Success Rooted in Tradition. RENNER GmbH Kompressoren have been known for

### Pressure Automated Calibration Equipment

GE Measurement & control Pressure Automated Calibration Equipment Safety Instructions and User Guide - K0447 PACE5000 PACE6000 K0447 Issue No. 9 1 10 1 PACE5000 1 2 3 4 5 PACE6000 2 6 7 8 3 4 5 6 7 8 9

### Sorensen DCS Series. 1 3 kw V A. General Purpose Systems Power Supply

Sensen DCS Series General Purpose Systems Power Supply High power density / low ripple and noise High programming resolution with Ethernet interface Constant voltage and current mode Remote sensing Isolated

### 2/ Port G1/4

CATALOGUE > Release 8.8 > Series ER100 digital electro-pneumatic regulators Series ER100 digital electro-pneumatic regulators Port G1/4 Compact design Digital display Analog and digital input Programmable

### Level switches Series LD Vibrating fork level switch for liquids and solids

Level switches Series LD Vibrating fork level switch for liquids and solids Robust and compact Suitable for liquids (model LD61) and solids (model LD60) No moving parts, low maintenance Corrosion resistant

### High Pressure Breathing Air Compressors

High Pressure Breathing Air Compressors [ Full variety for different applications] MSA offers a comprehensive range of high pressure breathing air compressors for both the firefighting and diving market,

### Miniature flowmeters DK 46, DKR 46 DK 47, DK 48, DK 800

KROHNE 1/22 7.236.22. GR Miniature flowmeters DK 46, DKR 46 DK 47, DK 48, DK 8 Variable area flowmeters Vortex flowmeters Flow controllers Electromagnetic flowmeters Ultrasonic flowmeters Mass flowmeters

### TH-1800-T TRX-700-CNG Converter

TH-1800-T TRX-700-CNG Converter low detector The CNG fuel gas flowmeter is so accurate as to meet a demand of measuring the CNG directly by making the most use of our well-established mini-thermal flowmeter

### Control and Automation

GE Consumer & Industrial Power Protection Control and Automation Electronic relays GE imagination at work Electronic relays Order codes F.3 Series DM Single voltage electronic timers. 22.5mm module F.4

### Level switches Series LD Vibrating fork level switch for liquids and solids

Level switches Series LD Vibrating fork level switch for liquids and solids Robust and compact Suitable for liquids (model LD61) and solids (model LD60) No moving parts, low maintenance Corrosion resistant

### High-performance submersible pressure transmitter For level measurement Model LH-20

Electronic pressure measurement High-performance submersible pressure transmitter For level measurement Model LH-20 WIKA data sheet PE 81.56 Applications Deep well and borehole measurements Groundwater