2 CONTACT INFORMATION Pamela West Pipeline Safety Specialist U.S. Department of Transportation PHMSA Inspector Training and Qualifications Main: (405) My Office: (405)
3 GENERAL Each segment must be maintained in accordance with this Subpart. Each unsafe segment must be repaired, replaced or removed. Hazardous leaks must be repaired promptly.
4 TRANSMISSION LINES: PATROLLING (a) Must look for; Leaks, construction activity, and other factors affecting safety.
5 TRANSMISSION LINES: PATROLLING (b) When establishing frequencies, must consider; Operating pressures, Class location, Terrain, Weather, Other relevant factors.
6 TRANSMISSION LINES: PATROLLING (c) Maximum interval between patrols: Class 1,2 Hwy & RR All Other Locations At least twice each calendar year, not to exceed 7 1/2 months. At least once each calendar year, not to exceed15 months.
7 TRANSMISSION LINES: PATROLLING (c) Maximum interval between patrols: Class 3 Hwy & RR All Other Locations Class 4 Hwy & RR All Other Locations At least four times each calendar year, not to exceed 4 ½ months. At least twice each calendar year, not to exceed 7 ½ months. At least four times each calendar year, not to exceed 4 ½ months. At least four times each calendar year, not to exceed 4 ½ months.
8 TRANSMISSION LINES: PATROLLING
9 TRANSMISSION LINES LEAKAGE SURVEYS Transmission lines must be leak surveyed once each calendar year, not to exceed fifteen months. Except class 3 & 4 areas transporting un-odorized gas, must use leak detection equipment. Class 3 = Twice each calendar year not to exceed 7 ½ months. Class 4 = Four times each calendar year not to exceed 4 ½ months.
10 LINE MARKERS FOR MAINS AND TRANSMISSION LINES (a) Marker must be Placed & Maintained as close as practical; At each crossing of public road & railroad; and
11 (a) LINE MARKERS FOR MAINS AND TRANSMISSION LINES Wherever necessary to identify the location of the transmission line or main to reduce possibility of damage or interference.
12 (b) LINE MARKERS FOR MAINS AND TRANSMISSION LINES Exceptions: Mains and transmission lines located offshore, at crossings of or under waterways or bodies of water. Mains in class 3 & 4 locations where a damage prevention program is in effect;
13 LINE MARKERS FOR MAINS AND TRANSMISSION LINES (b) Exceptions continued; Transmission lines in class 3 & 4 areas where placement of a line marker is impractical.
14 LINE MARKERS FOR MAINS AND TRANSMISSION LINES (c) Pipelines Above ground Markers must be installed and maintained in areas accessible to the public.
15 LINE MARKERS FOR MAINS AND TRANSMISSION LINES (d) Must Have the word Warning, Caution, or Danger Followed by Gas (or name of gas) Pipeline Letters must be at least 1 high with ¼ stroke. Must have Operator name and 24 hr. phone number. TQ Pipeline Co
16 TRANSMISSION LINE RECORDKEEPING The date, location, and description of each repair to pipe or pipe-to-pipe connections must be retained for as long as the pipe remains in service.
17 TRANSMISSION LINE RECORDKEEPING Records for the following must be retained for 5 years or until the next survey, inspection, or test is completed, whichever is longer: Repairs to parts of the pipeline other than pipe Leakage Surveys Patrols Inspections & tests required by Subparts L & M
18 (a)(1) TRANSMISSION LINES: REPAIR PROCEDURES Immediate temporary measures to protect public when a line operating at 40% SMYS or greater has a leak, imperfection, or damage that impairs serviceability: and
19 TRANSMISSION LINES: REPAIR PROCEDURES (a)(2)(b) If it is not feasible to make permanent repairs at the time. An operator shall make permanent repairs as soon as feasible. Conditions covered by Subpart O, Gas IM, must be remediated as prescribed in (d) Welded patches are not allowed except as provided by (b)(3).
20 (a) TRANSMISSION LINES: PERMANENT REPAIRS Imperfections or damage on a line operating at 40% SMYS must be: (1) Removed by cutting out and replacing a cylindrical piece of pipe; or (2) Repaired by a method that reliable engineering tests and analyses show can permanently restore the serviceability of the pipe.
21 (b) TRANSMISSION LINES: REPAIR PROCEDURES Operating pressure must be at a safe level during repair operations.
22 TRANSMISSION LINES: REPAIR PROCEDURES (a) Removing the leak by cutting out and replacing a cylindrical piece of pipe; or (b) Repairing the leak by one of the following methods:
23 TRANSMISSION LINES: REPAIR PROCEDURES (b) (1) Install a full encirclement welded split sleeve of appropriate design, unless the transmission line is joined by mechanical couplings and operates at less than 40 percent of SMYS. (2) If the leak is due to a corrosion pit, install a properly designed bolt-on-leak clamp.
24 (b) TRANSMISSION LINES: REPAIR PROCEDURES (3) If the leak is due to a corrosion pit and on pipe of not more than 40,000 psi (267 Mpa) SMYS, fillet weld over the pitted area a steel plate patch with rounded corners, of the same or greater thickness than the pipe, and not more than one-half of the diameter of the pipe in size.
25 (b) TRANSMISSION LINES: REPAIR PROCEDURES (4) If the leak is on a submerged offshore pipeline or submerged pipeline in inland navigable waters, mechanically apply a full encirclement split sleeve of appropriate design.
26 (b) TRANSMISSION LINES: REPAIR PROCEDURES (5) Apply a method that reliable engineering tests and analyses show can permanently restore the serviceability of the pipe.
27 (a) TRANSMISSION LINES: TESTING OF REPAIRS Replacement pipe must be tested to the pressure required for a new line in the same location.
28 (b) TRANSMISSION LINES: TESTING OF REPAIRS Each repair made by welding must be examined in accordance with
29 DISTRIBUTION: PATROLLING The frequency of patrolling mains is determined by the severity of conditions which could cause a hazard to public safety. Areas subject to physical movement or external loading where failure could result must be patrolled at least: At least 4 times each calendar year not to exceed 4 ½ mo. in business districts. At least 2 times each calendar year not to exceed 7 ½ mo. outside business districts.
30 DISTRIBUTION LEAK SURVEYS (b) Type and scope of leakage control program must be determined by local conditions, but must meet the following minimums:
31 DISTRIBUTION LEAK SURVEYS (b)(1) Business Districts Once each calendar year not to exceed 15 months. Must check: Manholes Pavement & sidewalk cracks; and Other potential venting locations. Must use leak detection equipment.
32 DISTRIBUTION LEAK SURVEYS (b)(2) Outside of business district as frequent as necessary, but at least once every 5 calendar years at intervals not to exceed 63 months; or Pipe that is not cathodically protected and subject to (e) must be surveyed at least once every 3 calendar years at intervals not to exceed 39 months
33 TEST REQUIREMENTS FOR RE-INSTATING SERVICE LINES Each disconnected service must be tested in the same manner as a new service. Each temporarily disconnected service must be tested from the point of disconnection to the service line valve.
34 ABANDONMENT (b) Each pipeline abandoned in place must be; Disconnected from all sources of gas, purged, and sealed. Offshore must be filled with water or inert materials and sealed at the ends. Purging is not required if the volume of gas is so small that it does not present a hazard.
35 ABANDONMENT (d)(e) When service to a customer is disconnected, the operator must do one of the following; Close and lock the valve. Install a mechanical device or fitting in the service line or meter to prevent the flow of gas. The customers piping must be physically disconnect from the gas supply and the ends sealed. If purged with air, insure a combustible mixture is not present after purging.
36 (f) ABANDONMENT Each abandoned vault must be filled with compacted materials.
37 (a) COMPRESSOR STATIONS: INSPECTION AND TESTING OF RELIEF DEVICES. Except for rupture discs, each pressure relieving device in a compressor station must be inspected and tested in accordance with and , and must be operated periodically to determine that it opens at the correct set pressure.
38 COMPRESSOR STATIONS: INSPECTION AND TESTING OF RELIEF DEVICES (b)(c) Any defective or inadequate equipment found must be promptly repaired or replaced. Each remote control shutdown device must be inspected and tested at least once each calendar year, at intervals not exceeding 15 months to determine that it functions properly.
39 COMPRESSOR STATIONS: STORAGE OF COMBUSTIBLE MATERIALS Flammable or combustible materials in quantities beyond those required for everyday use, must be stored a safe distance from the compressor building. Above ground oil or gasoline storage tanks must be protected in accordance with National Fire Protection Association Standard No. 30.
40 COMPRESSOR STATIONS: GAS DETECTION (a) Each compressor building in a compressor station must have a fixed gas detection and alarm system, unless the building is- Constructed so that at least 50 percent of it s upright side area is permanently open; or Located in an unattended field compressor station of 1,000 horsepower or less.
41 COMPRESSOR STATIONS: GAS DETECTION (b) Except when shutdown of the system is necessary for maintenance under paragraph (c), each gas detection and alarm system must- Continuously monitor the compressor building for a concentration of gas in air of not more than 25 percent of the lower explosive limit; and If that concentration of gas is detected, warn persons about to enter the building and persons inside the building of the danger.
42 (c) COMPRESSOR STATIONS: GAS DETECTION. Each gas detection and alarm system required by this section must be maintained to function properly. The maintenance must include performance tests.
43 PRESSURE LIMITING AND REGULATING STATIONS: INSPECTION AND TESTING (a) Each pressure limiting station, relief device (except rupture discs), and Pressure regulating station and its equipment must be inspected and tested at least once each calendar year at intervals not exceeding 15 months to determine that it is In good mechanical condition. Adequate from the standpoint of capacity and reliability of operation.
44 PRESSURE LIMITING AND REGULATING STATIONS: INSPECTION AND TESTING (a) Except as provided in paragraph (b), set to control or relieve at the correct pressure consistent with the pressure limits of (a). Properly installed and protected from dirt, liquids, or other conditions that might prevent proper operation.
45 PRESSURE LIMITING AND REGULATING STATIONS: INSPECTION AND TESTING (b) For steel pipelines whose MAOP is determined under (c), if the MAOP is 60 psi gage or more, the control or relief pressure limit is as follows: MAOP Hoop Stress Greater than 72% SMYS Less than 72% SMYS Unknown % SMYS Pressure Limit MAOP plus 4% MAOP plus 10% ( (a)(2)) Pressure that will prevent unsafe operation considering MAOP, operation, & Maint. History.
46 PRESSURE LIMITING AND REGULATING STATIONS: TELEMETERING OR RECORDING GAGES (a)(b) Each distribution system supplied by more than one district pressure regulating station must be equipped with telemetering or recording pressure gages to indicate the gas pressure in the district. On distribution systems supplied by a single pressure regulating station, the operator shall determine the necessity of telemetering or recording gages, considering the number of customers supplied, operating pressures, capacity of the installation, and other operating conditions.
47 PRESSURE LIMITING AND REGULATING STATIONS: TELEMETERING OR RECORDING GAGES (c) If there are indications of abnormally high- or lowpressure, the regulator and auxiliary equipment must be inspected and the necessary measures employed to correct any unsatisfactory operating conditions.
48 (a) PRESSURE LIMITING AND REGULATING STATIONS: CAPACITY OF RELIEF DEVICES Pressure relief devices at pressure limiting stations and pressure regulating stations must have sufficient capacity to protect the facilities to which they are connected. Except as provided in (b), the capacity must be consistent with the pressure limits of (a), and must be determined at least once each calendar year not to exceed 15 months, by testing the devices in place or by review and calculations.
49 (b)(c) PRESSURE LIMITING AND REGULATING STATIONS: CAPACITY OF RELIEF DEVICES If review and calculations are used, the calculated capacity must be compared with the rated or experimentally determined relieving capacity of the device for the conditions under which it operates. After the initial calculations, subsequent calculations need not be made if the annual review documents that parameters have not changed. If a relief device is of insufficient capacity, a new or additional device must be installed to provide the capacity required by paragraph (a) of this section.
50 (a) VALVE MAINTENANCE: TRANSMISSION LINES Each valve that might be required during an emergency must be inspected and partially operated at least once each calendar year not to exceed 15 months.
51 (b) VALVE MAINTENANCE: TRANSMISSION LINES Prompt remedial action is required to correct any valve found inoperable, unless an alternative valve is designated.
52 (a) VALVE MAINTENANCE: DISTRIBUTION SYSTEMS Each valve, necessary for safe operation of a distribution system, must be checked and serviced once each calendar year, not to exceed 15 months.
53 VALVE MAINTENANCE: DISTRIBUTION SYSTEMS (b) Each valve, necessary for safe operation of a distribution system, must be checked and serviced: At least once each calendar year not to exceed15 months. Prompt remedial action is required to correct any valve found inoperable, unless an alternative valve is designated.
54 (a) VAULT MAINTENANCE Vaults containing pressure regulating or limiting equipment, greater than 200 cubic ft. must be inspected each calendar year not to exceed 15 months for physical condition and ventilation.
55 VAULT MAINTENANCE (b)(c)(d) If gas is detected, inspect for and repair leaks. Inspect ventilating equipment. Inspect integrity of vault covers.
56 PREVENTION OF ACCIDENTAL IGNITION Each operator must minimize danger of accidental ignition. Remove ignition sources Provide fire extinguishers Post Warnings Don't weld around combustible mixtures.
57 CAST IRON: CAULKED BELL AND SPIGOT JOINTS (a) Each cast iron caulked bell and spigot joint that is subject to pressures of more than 25 psi gage must be sealed with: A mechanical leak clamp; or A material or device which: Does not reduce the flexibility of the joint; Permanently bonds, either chemically or mechanically, or both, with the bell and spigot metal surfaces or adjacent pipe metal surfaces; and,
58 CAST IRON: CAULKED BELL AND SPIGOT JOINTS (a)(b) Seals and bonds in a manner that meets the strength, environmental, and chemical compatibility requirements of (a) and (b) and Each cast iron caulked bell and spigot joint that is subject to pressures of 25 psi gage or less and is exposed for any reason must be sealed by a means other than caulking.
59 PROTECTING CAST IRON PIPELINES (a) When an operator has knowledge that the support for a segment of a buried cast-iron pipeline is disturbed: That segment of the pipeline must be protected, as necessary, against damage during the disturbance by: Vibrations from heavy construction equipment, trains, trucks, buses, or blasting; Impact forces by vehicles;
60 PROTECTING CAST IRON PIPELINES (a)(b) Earth movement; Apparent future excavations near the pipeline; or Other foreseeable outside forces which may subject that segment of the pipeline to bending stress. As soon as feasible, appropriate steps must be taken to provide permanent protection for the disturbed segment from damage that might result from external loads, including compliance with applicable requirements of (a), , and (b)-(d).
61 INFORMATION WEBSITES PHMSA Training and Qualification PHMSA Pipeline Safety Regulations
OQ Task Name Task 39.0 Backfill 1.0 Task Description This task applies to the process and material to backfill or cover a buried pipeline which has been excavated or otherwise exposed, Backfilling shall
December 4, 2009 Dry Systems 123a 1. DESCRIPTION The Anti-flood Device is required when Viking accelerators are installed on dry systems according to Viking Model E-1 Accelerator Trim Charts. In the SET
Practice Test FOR GAS POSITIONS APTITUDE BATTERY INTRODUCTION The purpose of this Practice Test is to help you prepare for the Gas Positions Aptitude Battery placement exercise. A sample of questions based
Dry 131h 1. DESCRIPTION The Viking Model G-1 Maintenance Air Compressor is an electric motor-driven, aircooled, single-stage, oil-less compressor. The unit is equipped with a check valve and provides a
173.306 Limited quantities of compressed gases. (a) Limited quantities of compressed gases for which exceptions are permitted as noted by reference to this section in 172.101 of this subchapter are excepted
Environmental Health and Safety Compressed Gas Cylinders - Guideline Date of Issuance: 1/10/18 Revision Number: Initial Revision Date: Prepared by: EH&S 1. Purpose Carnegie Mellon University has developed
Operation and Maintenance Plan For Master Meter Gas Distribution Systems MASTER METER SYSTEM A natural gas pipeline system for distributing natural gas for resale within, but not limited to, a distinct
PSM SOLUTIONS: AMMONIA SCR SYSTEMS 1 Issues that surround the storage of anhydrous ammonia 1. Government Audit/Citation Exposure a. OSHA i. NEP ii. PQV b. EPA 2. Safety Issues a. Burns b. Respiratory c.
References: a. 46 CFR Part 54 Pressure Vessels S. T. Brady, CDR, Chief, Engineering Division b. ASME Boiler and Pressure Vessel Code (BPVC), Section VIII, Division 1, (1998 Edition) c. Navigation and Inspection
Page 1 1.0 Scope and Application The following procedures describe safe operating practices in confined spaces. These may be sewers, pipelines, tanks, boiler compartments, ducts, vaults, pits, vats, bins
Design Manual Chapter 4 - Water Mains 4C - Facility Design 4C-1 Facility Design A. General Water mains and appurtenances, including hydrants and valves, should be provided along all streets including connections
Title: Safe Storage, Handling, Use and Disposal Procedures of Compressed Gas Cylinders Effective Date: November 2005 Revision Date: March 1, 2017 Issuing Authority: Responsible Officer: VP, Capital Projects
DEPARTMENT OF TRANSPORTATION Pipeline and Hazardous Materials Safety Administration OFFICE OF PIPELINE SAFETY PIPELINE SAFETY REGULATIONS PART 192 TRANSPORTATION OF NATURAL AND OTHER GAS BY PIPELINE: MINIMUM
FUNDAMENTALS OF PRESSURE RELIEF VALVES IN NATURAL GAS INSTALLATION - OPERATION - MAINTENANCE Gary S. Beckett Flow Safe Supply 10727 Tower Oaks Boulevard Houston, Texas 77070 What Are They and Why Are They
APCO ARV CLEAN WATER AIR RELEASE VALVES Model 50A Instruction D12013 February 2017 Instructions These instructions provide installation, operation and maintenance information for APCO ARV Clean Water Air
6.6 Relief Devices Introduction Relief devices are used to help prevent a catastrophic failure of equipment and/or minimize the effects of any unanticipated or uncontrolled events. As such, relief devices
Introduction To use compressed gas cylinders safely, it is important that they are stored properly, handled correctly, used with the correct equipment, and that the properties of the gases they contain
Hot Work Program University of Wisconsin-Platteville Reviewed 4/2016 The purpose of the Hot Work Program is to establish safety procedures for employees, contractors, and subcontractors engaging in any
Instruction Manual D100343X012 Type 1367 November 2017 Type 1367 High-Pressure Instrument Supply System with Overpressure Protection TYPE 252 FILTER 2ND-STAGE TYPE 67CF FILTER-STYLE REGULATOR INLET TYPE
Commandant United States Coast Guard 2703 Martin Luther King Jr. Ave. SE Washington DC 20593-7501 Staff Symbol: CG-FAC-2 Phone: (202) 372-1145 Email: HQS-PF-fldr-CG-FACfirstname.lastname@example.org NAVIGATION AND VESSEL
DelVal Flow Controls Private limited (A DIVISION OF DelTech CONTROLS LLC, USA) DelVal Series 50/5, 5A/5B Butterfly Valves INSTALLATION, OPERATION AND MAINTENANCE MANUAL ENGINEERING DATA SHEET E.D.S. NO
Compressed Gas Safety Program Purpose: The purpose of this safety policy and procedure is to establish guidelines for the protection and safety of this company s employees who handle and use compressed
250C-IG COMPRESSOR KIT 12V PART NO. 25050 250C-IG COMPRESSOR KIT 24V PART NO. 25058 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual
1550650/4 IM-P155-07 ST Issue 4 and Diffusers Installation and Maintenance Instructions 1. Safety information 2. General product information 3. Installation 4. Commissioning 5. Operation 6. Maintenance
250C-IG COMPRESSOR KIT 12V PART NO. 25050 250C-IG COMPRESSOR KIT 24V PART NO. 25058 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual
Odorization of Gas Subpart L Wayne St. Germain Pipeline Safety Specialist Phone (405) 954 7219 Live Person (405) 954 8575 Direct Line Fax (405) 954 0206 Email email@example.com Odorization of Gas
Pulsed Eddy Current (PEC) Inspection through Insulation Inspection through insulation opens unexpected opportunities Shell Global Solutions in Amsterdam has developed over the past few years an inspection
3 GALLON, OILLESS PANCAKE COMPRESSOR INSTRUCTIONS Item #31289 The EASTWOOD 3 GALLON, OILLESS PANCAKE COMPRESSOR, with an Integral Air Regulator, efficiently supplies all compressed air requirements for
Page 1 of 15 1.0 PURPOSE 1.1. Axiall, Plaquemine Complex, has developed this Hot Tap Permit Program to eliminate potential accidents, injuries, and to enhance employee protection. 1.2. To provide for the
Leticia Santos Hernández Pipeline Safety Specialist U.S. Department of Transportation PHMSA Inspector Training and Qualifications Email: firstname.lastname@example.org Office: 405-686-2310 192.605(b) Gas Reports
January 6, 2012 Preaction 348a 1. Description Viking supervised Surefire Preaction Systems utilize the Viking G-6000P Valve. The small profile, lightweight, pilot operated Viking G-6000P Valve comes complete
AIR COMPRESSOR OPERATING INSTRUCTION AND PARTS LIST OIL-LESS TYPE IMPORTANT: PLEASE READ CAREFULLY BEFORE STARTING OPERATIONS. THE CONTENTS ARE FOR GENERAL INFORMATION OF ALL THE SIMILAR MODELS. Record
5040050 / 2 IM-P504-02 CH Issue 2 MF2M Monnier Miniature Compressed Air Filter Installation and Maintenance Instructions 1. Safety information 2. General product information 3. Installation and commissioning
Certified to CSA International 4.96 US For Outdoor Gas Fireplaces A HIGHER STANDARD IN QUALITY AND APPEARANCE SAFE AND BEAUTIFUL OUTDOOR LARGO FIRE PIT FOR PROPANE AND *NATURAL GAS OWNER S MANUAL WARNING:
January 6, 2012 Preaction 331a 1. Description Viking supervised Double-Interlocked Electric/Pneumatic Release Preaction Systems utilize the Viking G-3000P Valve. The small profile, lightweight, pilot-operated
Preaction 346a 1. Description The 6 Model G-6000P Electric Release Preaction System Riser Assembly can be used as a Single Interlock Preaction System with Electric Release, or as a Double Interlock Preaction
Confined Space Entry Learning Outcome When you complete this module you will be able to: Describe procedures needed to enter into, or work safely in confined spaces. Learning Objectives Here is what you
Purchase API Spec online at www.api.org/publications 7.2 Pressure and temperature ratings The nominal pressure (PN) class or the ASME rating class shall be used for the specification of the required pressure
Maintenance and Troubleshooting of Pneumatic Conveying Systems for Sand in a Foundry Article Takeaways: Chris Doerschlag President ALB Klein Technology Group www.albkleinco.com 1. Troubleshooting Guide
notifies the control room or other Maintenance Safer & Easier remote locations that a probe column The system s intelligence can BOILER INSPECTION GUIDELINES FOR distinguish dirty probes from BOILER INSPECTION
HYDROGEN PEROXIDE RAILCAR UNLOADING BY SELF-PRIMING PUMP INTRODUCTION All equipment used for storage and handling of hydrogen peroxide must be dedicated exclusively to hydrogen peroxide service and must
Un-Pressurized Orefice Fittings FIO EZ Parts List and Operation Instructions TECHNICAL MANUAL Dn 2-6 Class 150-600 Lbs US US 2 FIO EZ - MT 108-US - 05-2016 FIO EZ Important Instructions US Pietro Fiorentini
About This Online Training This online training material was designed to be used as a guide only and does not replace federal, state, local, or company codes. The user of this material is solely responsible
Installation, Operation and Maintenance Manual for Back Pressure Regulator Model 8860 2009 Groth Corporation IOM-8860 Rev. B 12541 Ref. ID: 95565 Page 2 of 13 Table of Contents I. INTRODUCTION 3 II. DESIGN
Subparts AA and BB - The Other RCRA Air Rules Beginners aabb 1 Background Subpart AA - Process vents Subpart BB - Equipment leaks Subpart CC - Tanks, surface impoundments, containers. Also includes Subpart
COMPRESSED GASES SAFETY Last Modified: APR 2015 1 of 6 Compressed Gasses Safety 1 PURPOSE To provide guidelines for transport, storage, handling, and use of cylinders containing compressed gas. 2 SCOPE
University of Pittsburgh 1 Hot Work Program July 2003. UNIVERSITY OF PITTSBURGH HOT WORK PROGRAM All hot work can create conditions with high probability for fire related injury or property loss. Hot work
Purchase API Spec online at http://www.techstreet.com/api Annex G (normative) G.1 General Requirements for Nondestructive Examination This annex specifies the requirements for NDE that shall be performed
Installation Instructions For Flat Seated Bolted Type RAH Series Disk Holders RA Series Rupture Disks 1. WARNING a) Read the complete instructions before attempting to install the rupture disk and holder
This information is proprietary and shall not be disclosed outside your organization, nor shall it be duplicated, used or disclosed for purposes other than as permitted under the agreement with Kinetics
Developing a Policy for Auto Transportation of Medical Oxygen in High Pressure Cylinders and Cryogenic Vessels Since 1993, Applied Home Healthcare Equipment LLC has published numerous publications, videos,
200 PSI HIGH-FLOW AIR SOURCE KIT 50% Duty Compressor on 2.0 Gallon Air Tank PART NO. 20008 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of
g DEH 40050 Instructions Three-Phase, Platform-Mounted Distribution Transformers Introduction The equipment covered by these instructions should be operated and serviced only by competent technicians familiar
CUT OFF TOOL MODEL: CAT113 Part No: 3120135 ASSEMBLY & INSTRUCTION MANUAL LS0309 INTRODUCTION Thank you for purchasing this CLARKE product Before attempting to use the product, it is essential that you
CLASS PROGRAMME Type approval DNVGL-CP-0183 Edition December 2015 The electronic pdf version of this document, available free of charge from http://www.dnvgl.com, is the officially binding version. FOREWORD
Deutsche Akkreditierungsstelle GmbH Annex to the Accreditation Certificate D-IS-11027-03-00 according to DIN EN ISO/IEC 17020:2012 Period of validity: 14.02.2017 to 13.02.2022 Date of issue: 08.06.2017
Confined Space Entry Purpose The purpose of this chapter is to establish methods to identify confined spaces, classify them according to their risks, and establish guidelines necessary for the safe preparation,
April 2017 The evolution of the Ex-proof flame path As written in previous dissertation, the most critical part of a flameproof enclosure 'Ex d' is the flame path. Although the Standards are divided into
Safety and Health Policy and Procedure Manual WELDING, CUTTING, and BRAZING PROGRAM Section 0140 I. INTRODUCTION II. SCOPE III. STANDARD IV. GENERAL REQUIREMENTS A. Basic Precautions for Fire Prevention
1 Vibration and Pulsation Analysis and Solutions Brian Howes, M.Sc., P.Eng. Beta Machinery Analysis Ltd. Problems created by excessive vibration in machinery can have serious economic impact. Frequently
GAP.17.4.1 A Publication of Global Asset Protection Services LLC BASIC OXYGEN FURNACES INTRODUCTION Most steelmaking facilities use basic oxygen furnaces (BOFs) to produce molten steel. GAP.17.4.0 describes
22. Specialty Valves. a. Types of Specialty Valves. 1) Use of the following specialty valves is covered in this section: Altitude Valve, Pressure Reducing Valve, Pressure Relief Valve, Swing Check Valve,
Installation Sheets Manual 121 Gas Combustion Combination Controls and Systems Section G Technical Bulletin GM Issue Date 0297 GM Series Dual-Block Multi-Function Gas Control Valves Figure 1: GM Series
Flange Bolt Torquing for Resistoflex Plastic-Lined Piping Products Torquing When assembling flange connections, always use a full complement of clean, new high strength A193-B7 bolting. If using stainless
CALL BEFORE YOU DIG POLICY AND PROCEDURE Prepared By: Triumvirate Environmental Developed: December 2012 Updated: Program Approval Associate Vice President of Public Safety & Administrative Services Associate
OQ Task Name Task 5.1 Examine for Mechanical Damage on Buried or Submerged Pipe 1.0 Task Description Each time a pipeline is exposed, the operator must perform an inspection/examination of the pipe and
I&M V9629R1 Solenoid Valves used in Safety Instrumented Systems Operating Manual in accordance with IEC 61508 ASCO Valves Page 1 of 7 Table of Contents 1 Introduction...3 1.1 Terms and Abbreviations...3
Confined Space Entry Safety Program Table of Contents SCOPE...2 DEFINITIONS..2 PROGRAM ELEMENTS...3 SPACE EVALUATION...4 IDENTIFICATION AND CLASSIFICATION...4 POSTING...4 RECLASSIFICATION OF PERMIT SPACE...4
Part 6: Pressure and Leak Testing QA/CI Dept. PS Committee/Chair 11/06/15 11/06/20 1.0 6:1 of 6 1 Pressure and Leak Testing The primary reason for pressure testing is to confirm the integrity of a pressure
R-1450 R6 Safety Relief Valve T H E G A S I N D U S T R Y Purpose Safe practice in the transmission, distribution and utilization of gas requires a device to limit line pressure to a predetermined safe
BPZM-MRD Nitrogen Injection System (Transformer protector) Overview BPZM-MRD Nitrogen Injection Explosion Prevention & Fire Protection System became more advanced fire protection and explosion prevention
PSK Standards Association PSK 4917 Appendix 14 1 (6) Manufacturer: Yritys Oy RESULTS OF ANALYSIS ACCORDING TO DIRECTIVE 97/23/EY (PED) Address: Purchaser: Tilaaja Oy Document identification: 127860178623-
For use with select HPC Fire Pits ONLY- refer to product catalog or website. 100K BTU Maximum : FOR OUTDOOR USE ONLY Small Tank LP Kit (STLPK) Installation & Operation Instructions Installation We suggest
PRESSURE TEST PUMP Model No: PTP00 Part No: 06020 OPERATING & MAINTENANCE INSTRUCTIONS GC0/09 INTRODUCTION Thank you for purchasing this CLARKE Pressure Testing Pump. Before attempting to use the product,
PERMA-CYL 230/450/1000/1500/2000 Installation Manual Manual #11630833 - Revision B TABLE OF CONTENTS SAFETY 3 THE PERMA-CYL FAMILY 4 CONDUCTING A SITE EVALUATION 5 OUTDOOR INSTALLATION EXTERNALLY SITED/GAS
CLEANING, INSPECTION, AND TESTING OF SEWERS PART 1 - GENERAL 1.01 SECTION INCLUDES A. Cleaning, Inspecting, and Testing Sanitary Sewers B. Cleaning, Inspecting, and Testing Storm Sewers C. Cleaning and