HOW TO PLAN AN UNDERGROUND IRRIGATION SYSTEM

Size: px
Start display at page:

Transcription

1 HOW TO PLAN AN UNDERGROUND IRRIGATION SYSTEM CHECK THE AVAILABILITY OF WATER MEASURE THE WATER PRESSURE Close all household taps. Fit a pressure gauge to an outdoor tap, then open it completely (STATIC pressure). Ask your plumber to lend you a pressure gauge, or hire one. Take the measurement at different times during the day and night. Container capacity (e.g. 10 litres) Q= x 60= 10 x 60=30 litres/min Time taken (e.g. 20 seconds) 20 Q= flow MEASURE THE AVAILABLE WATER FLOW Simply time how long it takes to fill a recipient with known volume. PLANNING Use a compass to mark the circumference or circle sectors reached by each sprinkler, until the entire surface is covered. For best results, position the 90 sprinklers in the corners of the patches to be watered, s along garden strips, and 360 sprinklers in open spaces. The examples given in this booklet show the arrangement necessary to cover long and narrow areas evenly. The circumferences, as seen in the examples, meet to guarantee total coverage of ground and the even distribution of water in all points. When arranging the sprinklers, refer to the recommended spacing indicated in the tables on page 40. DIVIDE THE AREA INTO CIRCUITS Referring to the sprinkler output table, write in the water consumption (in l/min.) next to each sprinkler. Group the sprinklers into distinct areas (use different colours), summing progressively the water consumption. Make sure that the water consumption in each area does not exceed the available flow. You should aim at creating a well-balanced system, i.e. each circuit should have the same water consumption.

2 43 MARK THE LAYOUT OF TUBES Starting from the point where the solenoid valves controlling each single circuit will be installed, mark in the tube connecting each valve to the sprinklers (previously grouped into areas), thereby drawing independent valve circuits. Since trenches will have to be dug to lay the pipes, mark in straight lines, avoiding as far as possible driveways, terraces and other obstacles. The diagrams on the following pages give examples of the positioning of sprinklers. Bear in mind that: - 90 sprinklers should be positioned in garden corners; - s should be positioned along garden strips; - adjustable sprinklers are best used for 270 or irregular angles; sprinklers should be positioned in central open spaces. 90 sprinkler adjustable sprinkler adjustable sprinkler Irrigatori a sprinkler adjustable sprinkler 90 sprinkler

3 FLOW RESISTANCE Don't forget pipe FLOW RESI- STANCE: refer to the pressure loss table indicating the values to be subtracted from the original static pressure available. The DYNAMIC pressure obtained should be sufficient to guarantee correct sprinkler operation. FLOW RESISTANCE IN 3/4" AND 1" DIAMETER TUBES (IN BAR) FOR EVERY 10 METRE LENGTH Flow l. / min Int. diam. 3/4" Int. diam. 1" PRACTICAL DIY INSTALLATION Go into the garden and turn your project into an efficiently operating reality. A set of solenoids controls the opening and closing of irrigation circuits. The water supply line to the valves is subject to the entire amount of static pressure (when the circuit is closed); for this reason it should be made from a watertight metal pipe. As a rule, the diameter of the tube connecting the valves to the service line should not be less than the diameter of the valves. It is also a good idea to fit a gate valve upstream to shut off the entire system when necessary, for example when maintenance work is required.

4 Once the solenoid valves have been connected to the main water supply pipe, take your plan and mark the path of tubes of each sprinkler circuit. Plant a stake at each point where a sprinkler is to be installed. Now join the stakes with string (or with chalk powder on the ground) to trace the line of each circuit tube, from the solenoid valve to the sprinklers. Unroll the polyethylene coil, from the valves to the stakes, along the marked path. Put the T or connector couplings and the drainage valves in the position for installation. Straighten the tube properly before cutting it to length (better too long than too short). Use a hacksaw to cut the tube; clean cut ends with a scraper before fitting compression connectors to ensure a completely watertight connection. 45 To avoid damaging the lawn, heap the dug earth on plastic sheeting, then remove when finished. Use a spade to dig a trench at least cm deep. This won t take much of an effort, and should be enough to protect the pipes against winter frost. At each stake, place a sprinkler and the threaded bracket extension coupling (before applying the extension, drill a hole in the tube with a 10 mm bit) on the ground.

5 between the sprinklers and the valves. Fix the sprinklers in a vertical position (tie them to the stakes with string), then open the valve (in sequence) to test circuit operation. Shift the sprinklers as required to achieve perfect coverage of the watered ground. Once the desired coverage is obtained and the circuits have been arranged, lay the tube in the trenches. Make sure that the sprinklers are positioned flush to the terrain surface; the threaded extension supporting the sprinkler can be segmented to adjust sprinkler height. Now connect up all tube lengths At the end of installation, the circuit should be emptied of all residues and earth. To do so, simply unscrew the head from each sprinkler and open the valves; the water pressure will flush the circuit clean. Screw the heads back on the sprinklers, then fill in the trenches and level to the surrounding area (and the upper edge of the sprinklers). Your irrigation system is now complete and ready for operation, controlled by an automatic watering timer.

6 UNDERGROUND IRRIGATION Reasons for choosing a Claber Rainjet underground irrigation system There are a lot of good reasons for installing an underground automatic irrigation system: the convenience of having your garden automatically watered, even when you re away or on holiday (no need to find someone to come and look after the garden); the knowing that all areas of the garden will get the necessary amount of water, without waste, assuring maximum economy; no hoses above ground to get in the way of the lawn mower sprinklers are flush to the level of the lawn and are hardly noticeable; silent operation, causing no disturbance to neighbouring homes; increased property value no well-tended lawn can today afford to do without an automatic irrigation system. WATCH OUT FOR THE COLD! In areas subject to frosts, a drainage valve should be fitted at the lowest point of each irrigation line. When the circuit is closed and no water is circulating, the valve automatically opens to release residual water, which otherwise if left to freeze could damage the hose. When water flows through the hose, the drainage valve automatic locks.

Underground irrigation

Prograers Turbines and Pop-ups Solenoid valves ittings Accessories and Hoses 70 Irrigation located in set areas, and the only time that you need to invest into it, is the time it takes to set it up, then

175 m2 (1,880 sq ft) Kit

175 m2 (1,880 sq ft) Kit Your Kit Components 1 x 50m 2 Complete Kit Tap Assembly 5 x Auto-flushing valve (spinlock) 2 x 50m 2 Extension Kit 3 x Straight joiner (spinlock) 4 x Tee joiner (spinlock) 1 x

Blue Points 1 ¼ WELL POINT INSTALLATION INSTRUCTIONS

Blue Points 1 ¼ WELL POINT INSTALLATION INSTRUCTIONS This brochure is designed to provide step-by-step instructional assistance to the individual who wishes to install a shallow water well system for residential

Valves. Controllers. Valves Two Types

Hydraulics Taking the Irritation out of Irrigation My plants are getting irrigated, so I m all set, right? Marcus Duck Academic Advisor, Instructor & Program Coordinator MSU s 2-year Horticulture Programs

How Do I Install My Garden Master Bucket Garden?

How Do I Install My Garden Master Bucket Garden? 1. On the arrival of your Bucket Garden open the bucket and remove the 4 screws from the outside of the bucket rim and pull the 2 buckets apart. Check the

IMPORTANT PLEASE READ BEFORE COMMENCING INSTALLATION This Fitting Guide is designed to assist in the Installation of your Reverse Osmosis System. Some of the parts that are supplied with each system may

Putting it All Together: Making Sense of Drip Irrigation UC Master Gardener Conference August 24, 2017

Putting it All Together: Making Sense of Drip Irrigation UC Master Gardener Conference August 24, 2017 Chuck Ingels Farm & Horticulture Advisor caingels@ucanr.edu http://ccag-eh.ucanr.edu/ http://sacmg.ucanr.edu/

TANDEM MODULATOR FOR OUTLET GAS FLOW: STEPPED (836 TANDEM) - CONTINUOUS (837 TANDEM) SERVO-CONTROLLED PRESSURE REGULATOR

SIT Group 836-837 TANDEM MULTIFUNCTIONAL GAS CONTROL MODULATOR FOR OUTLET GAS FLOW: STEPPED (836 TANDEM) - CONTINUOUS (837 TANDEM) SERVO-CONTROLLED PRESSURE REGULATOR ALL ADJUSTMENTS ACCESSIBLE FROM ABOVE

Instructions For: Installing A Fence to Keep out Raccoons and Woodchucks

Instructions For: Installing A Fence to Keep out Raccoons and Woodchucks A hybrid barrier/electric fence Height: 18 Inches Includes directions on how to augment an existing barrier fence with an electric

Product Manual B-Safety ClassicLine & PremiumLine Emergency Eyewash and Eye/Face Wash Equipment

Product Manual B-Safety ClassicLine & PremiumLine Emergency Eyewash and Eye/Face Wash Equipment 1. Application Emergency eyewash and eye/face wash equipment are prescribed first aid installations for workplaces

Fountains & Watergardens Well Pumps & Water Systems Landscape Lighting & Irrigation Waste Water Pumps & Controls Swimming Pools & Spas Water Treatment & Filtration The Water System Experts Since 1972 IRRIGATION

OVERVIEW pg 3. Major Points to Consider pg 3 Minor Points to Consider pg 3. INSTRUCTIONS pg 4

TABLE OF CONTENTS OVERVIEW pg 3 Major Points to Consider pg 3 Minor Points to Consider pg 3 INSTRUCTIONS pg 4 How Does Nordic Freeze Work pg 4 How Long Will the Ice Plug Take to Form pg 4 How Do I Know

OTHER HOSES. Lances + Fittings. Hose, Hose Reels, TCF SPIRABEL MD SF SUCTION HOSE TUBCLAIR TRICOFUEL T TAPE LAY FLAT TRESS NOBEL RHS EVERFLOW.

TCF Meter 54S06-50 6mm ( /4") 50 0.9 54S08-25 8mm ( 5 /6") 25.02 54S0-25 0mm ( 3 /8") 25.22 54S2-25 2mm ( /2") 25.69 54S9-25 9mm ( 3 /4") 25 2.90 SPIRABEL MD SF SUCTION HOSE Coil 56M25-30 25mm (") 30 56M32-30

HOW TO DIG A TEST PIT

HOW TO DIG A TEST PIT An archaeological test pit is a small 1m by 1m trench dug in a series of layers, or spits, to a depth of approximately 1m. The archaeological materials collected from these layers

THERMAL POLITERM WALL AND POLITERM WALL FIX APPLICATION MANUAL. POLITERM WALL / POLITERM WALL FIX. Insulation & Chemicals Division

POLITERM WALL AND POLITERM WALL FIX superlight, thermal insulating aggregates for dry blowing into cavity walls THERMAL Insulation & Chemicals Division APPLICATION MANUAL. POLITERM WALL / POLITERM WALL

ambiente Installation Guide AmbiClip Systems more than underfloor Customer: Project: Project Reference: Date:

ambiente more than underfloor Customer: Project: Project Reference: Installation Guide AmbiClip Systems Date: AMBICLIP INSTALLATION GUIDE AMBICLIP FLOOR LAYING INSTRUCTIONS 1 Set up pipe decoiler and all

System Pressure Manager Standard & System Pressure Manager Plus

System Pressure Manager Standard & System Pressure Manager Plus Installation, Commissioning & Servicing Instructions Note: THESE INSTRUCTIONS MUST BE READ AND UNDERSTOOD BEFORE INSTALLING, COMMISSIONING,

CENTRAL GAS SUPPLY SYSTEMS : CYLINDER BATTERIES AND HIGH PRESSURE HOSES

P0170E-1.DOCX/08.16/MG CENTRAL GAS SUPPLY SYSTEMS : CYLINDER BATTERIES AND HIGH PRESSURE HOSES With a Central Gas Supply System, individual work places or gas take-off stations are supplied with gas through

Installation, Operation and Maintenance Instructions for Electronically Controlled Pressurisation Units

Installation, Operation and Maintenance Instructions for Electronically Controlled Pressurisation Units Models: EPS Single Pump EPT Twin Pump EPS-HP EPT-HP Single Pump High Pressure Twin Pump High Pressure

Latvin Luxury Shower Panel. Telephone Product Specification. ~ Minimum Working Pressure 1.0 bar ~ Maximum Working Pressure 3.

Product Specification ~ Minimum Working Pressure 1.0 bar ~ Maximum Working Pressure 3.0 bar Latvin Luxury Shower Panel ~ Fixing Centres 150mm +/- 10mm ~ Outlet size 1/2" Bottom Outlet Always maintain a

Instructions For: Installing McGregor s Small Animal Garden Fence

Instructions For: Installing McGregor s Small Animal Garden Fence A hybrid barrier/electric fence Height: 18 Inches Includes directions on how to augment an existing barrier fence with an electric one

BIMBAR INFLATABLE PACKERS AND ACCESSORIES

BIMBAR INFLATABLE PACKERS AND ACCESSORIES Geopro supplies a complete range of inflatable packers in nine different diameters from 28 up to 170mm. All our packers made of BIMBAR rubber technology are reinforced

bathrooms.com Concentric Thermostatic Shower Mixers Cleaning and Care Installation Manual Contents

bathrooms.com Concentric Thermostatic Shower Mixers Contents Page 3 - General Information & Safety Page 4 - Installation Page 5 - Concentric Valve Set-up Page 6 - Exposed ﬁtting of Concentric Mixer Valves

TECHNICAL DATA. Trimpac 251a. Spetember 16, 2013

Spetember 16, 2013 Trimpac 251a 1. DEsCrIpTION DESCRIPTION TRIMPAC Model B-6 and B-6B is a factory assembled trim package for a double interlocked preaction system with an electric/pneu-lectric release

Inflatable Packer Single & Double. Single & Double Packer Dimension. Wireline Packer. Water Testing Packer (WTP) Packer

Inflatable Packer Single & Double Single & Double Packer Dimension Wireline Packer Water Testing Packer (WTP) Packer Packer Working Pressure & Depth Chart Packer Water Hand Pump Packer Air Driven Pump

PRESSURISED PAINT CONTAINER

PRESSURISED PAINT CONTAINER MODEL NO: CPP2B PART NO: 3082115 OPERATION & MAINTENANCE INSTRUCTIONS GC0913 INTRODUCTION Thank you for purchasing this CLARKE Pressurised Paint Container. Before attempting

Pressure Compensating (PC) Spray Stakes

N E T A F I M U S A Pressure Compensating (PC) Spray Stakes Automated Watering Systems for Large Container Production Improve Plant Quality and Conserve Resources 1 or More Good Reasons to Choose Netafim

ECONORESS ELECTRONIC EPS & EPT - ENHANCED PRESSURISATION SET INSTALLATION OPERATION & MAINTENANCE DOCUMENTATION

ECONORESS ELECTRONIC EPS & EPT - ENHANCED PRESSURISATION SET INSTALLATION OPERATION & MAINTENANCE DOCUMENTATION OCT2010 STOKVIS ENERGY SYSTEMS 96R WALTON ROAD EAST MOLESEY SURREY KT8 0DL TEL: 020 87833050

Rapidmain Installation Guide

Rapidmain Installation Guide Aluminium Compressed Air Pipe Work Installation Guide Trafalgar Court, Waterloo Ind Estate, Widnes Cheshire. UK. Ref: Rapidmain installation guide 4b Index 1. Rapidmain fittings:

COUNTER CURRENT UNIT. Instruction Manual

COUNTER CURRENT UNIT Instruction Manual 1 Introduction: Congratulations on your purchase of a new Certikin counter current swimming unit. This unit has been developed and built by qualified personnel especially

PRO SINK -R 1 and 2. Dilution system CONTENTS

PRO SINK -R 1 and 2 Dilution system CONTENTS 1.0 Product description 2 2.0 Warnings.. 3 3.0 Installation procedure 4 4.0 Plumbing connections 4 5.0 Technical features.. 5 6.0 Maintenance... 6 7.0 Troubleshooting......6

REVERSE OSMOSIS WATER FILTRATION SYSTEM MODEL EWR 4075 INSTRUCTION MANUAL

REVERSE OSMOSIS WATER FILTRATION SYSTEM MODEL EWR 4075 INSTRUCTION MANUAL Excalibur Water Systems 142 Commerce Park Drive, Unit M & N Barrie, Ontario L4N 8W8 CANADA www.excaliburwater.com 2013.05.7446

Cool Springs and Clarksville store call Cookeville store call Bowling Green store call

Welcome to the Pool & Spa Depot family! The following guide is to help you understand what's involved in building your new above ground pool. Your above ground pool installation will require the following

TECHNICAL DATA. Trimpac 244a. September 16, 2013

September 16, 2013 Trimpac 244a 1. DEsCrIpTION DESCRIPTION TRIMPAC Model B-1 and B-1B is a factory-assembled trim package with an electric release module in a metal enclosure. The standard trim normally

EFLOW GUIDE. IRRIGATE UP TO 200m 2 SUITS DOMESTIC ONSITE APPLICATIONS

EFLOW GUIDE IRRIGATE UP TO 200m 2 SUITS DOMESTIC ONSITE APPLICATIONS > eflow : Water Reuse Dispersal System eflow is a complete dripperline diversion package specifically developed For onsite domestic

SIMPLAIR PIPING TOOL. JXT Company

SIMPLAIR PIPING INGERSOLL-RAND SIMPLAIR PIPING With push-in fittings and lightweight anodized aluminum pipe, a SimplAir system provides ideal connection throughout your entire air distribution system.

LEVEL 3 CERTIFICATE IN AUTOMATIC TURF IRRIGATION SYSTEMS ASSESSMENT SCHEDULE

NPTC Registered Charity No. 1096429 STONELEIGH PARK, WARWICKSHIRE CV8 2LG Tel: 024 7685 7300 Fax: 024 7669 6128 Email: information@nptc.org.uk LEVEL 3 CERTIFICATE IN AUTOMATIC TURF IRRIGATION SYSTEMS ASSESSMENT

Installation Guide For Spillways & LED Light Bars

Installation Guide For Spillways & LED Light Bars *A pdf copy can be obtained via www.iearth.com.au/downloads 1 TABLE OF CONTENTS A1. Size Availability.. Page 3 B1. Type of Spillway Effects. Page 3 1.

Exercise 2-3. Flow Rate and Velocity EXERCISE OBJECTIVE C C C

Exercise 2-3 EXERCISE OBJECTIVE C C C To describe the operation of a flow control valve; To establish the relationship between flow rate and velocity; To operate meter-in, meter-out, and bypass flow control

Installation, Operation and Maintenance Instructions for Electronically Controlled Pressurisation Units

Installation, Operation and Maintenance Instructions for Electronically Controlled Pressurisation Units Micro-S / Micro-S Digital Wall Hung Unit Please fulfil all listed requirements prior to and during

Replacement of Interchangeable Membrane

Replacement of Interchangeable Membrane Replacement of Expansion Vessel Membrane 100+ Capacity 1. Firstly, before disconnecting the vessel, bear in mind that you must isolate the vessel from the system

FILTER REGULATORS MODEL NO: CAT155 & CAT156 FITTING & MAINTENANCE INSTRUCTIONS PART NO: & ORIGINAL INSTRUCTIONS

FILTER REGULATORS MODEL NO: CAT155 & CAT156 PART NO: 3120169 & 3120170 FITTING & MAINTENANCE INSTRUCTIONS ORIGINAL INSTRUCTIONS GC0117 INTRODUCTION Thank you for purchasing this CLARKE Filter/Regulator.

Data sheet Pressure switch type CS December 2001 DKACT.PD.P10.A B1119

Pressure switch type CS December 2001 DKACT.PD.P10.A2.02 520B1119 Introduction Pressure switch type CS is part of the Danfoss pressure control range. All CS pressure switches have a built-in pressure-operated,

High Performance BSP Dial Up Pattern Pressure Reducing Valve

See our full range online at: www.vip-ltd.co.uk High Performance BSP Dial Up Pattern Pressure Reducing Valve VIP Product Code 31/0103 FUNCTION Pressure reducing valves are devices which, when installed

ambiente Installation Guide AmbiPlate more than underfloor Customer: Project: Project Reference: Date:

ambiente more than underfloor Customer: Project: Project Reference: Installation Guide AmbiPlate 0 0 Date: Ambiplate installation guide AmbiPlate Series Contents Designed for joisted/battened floors Maximum

Installation and Training Manual

AirForce1 Tower Kit Installation and Training Manual FuturEnergy Limited Ettington Park Business Centre Stratford upon Avon CV37 8BT +44 (0)1789 451070 Table of Contents Safety Notes... 3 Parts Supplied

Gas Welding Hoses and connections, the weak link

Gas Welding Hoses and connections, the weak link By Leif Andersen, Technical Product Manager Welding, WSS Regulators with flashback arrestors and the shank with its welding or cutting attachment are made

To purchase replacement parts and accessories, or to obtain technical assistance, visit:

IMPORTANT Read this guide and follow all instructions carefully before assembling or using this product. To purchase replacement parts and accessories, or to obtain technical assistance, visit: www.splasharoundpools.com

Irrigation System Winterization and Pressurization Procedures

Irrigation System Winterization and Pressurization Procedures Introduction Any time that an irrigation system is filled and pressurized, or when the system is drained and water flushed from the system,

Intro: by firechim on October 3, 2013

by firechim on October 3, 2013 Intro: Step 1: Guide for installing chimney liners with a tee connection This guide is to give you step by step instructions to install a chimney liner that utilizes a tee

TECHNICAL DATA. TRIMPAC Model B-5 & B-5B

September 16, 2013 Trimpac 250a 1. DESCRIPTION DEsCRIPTIoN is a factory assembled trim package for a ed an electric/pneumatic release module in a metal enclosure. The standard trim normally required on

Troyer s Gourd Rack 8 unit F R H O P

B E A D I M-N L Vertical Parts F R H O P Horizontal Parts C G J Updated 11/16 Parts List A: Top of Pole B: Bottom of Pole C: 48 Ground Stake D: Top Perch rods 48 long E: Hub F: Rope Winder w/ attached

Bottle Rocket Launcher P4-2000

WWW.ARBORSCI.COM Bottle Rocket Launcher P4-2000 BACKGROUND: The Bottle Rocket Launcher allows for the exploration of launching rockets using commonly available materials such as plastic soda bottles and

Dry Hydrants. The installation of a non-pressurized pipe system into local water sources provides a ready means of supplying water to fire engines.

Dry Hydrants What is a Dry Hydrant? A dry hydrant is a non-pressurized pipe system permanently installed in existing lakes, ponds and streams that provides a suction supply of water to a fire department

WORKHOLDING APPLICATION BOOKLET

WORKHOLDING APPLICATION BOOKLET Applications and advantages of using minibooster hydraulic pressure intensifiers MINIMUM SIZE MAXIMUM POWER B-GB Workholding 2018.04 1 of 20 2 of 20 B-GB Workholding 2018.04

Budget Range Operators Handbook

Budget Range Operators Handbook BAMBI AIR COMPRESSORS LTD 152 Thimble Mill Lane Heartlands Birmingham B7 5HT United Kingdom Tel: 0121 322 2299 Fax: 0121 322 2297 Email: sales@bambi-air.co.uk www.bambi-air.co.uk

K-Line Irrigation Pod Packs

K-Line Irrigation Pod Packs Five Pod, Farm Pack or Three Pod Pack Installation and user manual September 2016 RX PLASTICS LTD PO Box 360 Ashburton Phone +64 3 307 9081 Email sales@rxplastics.co.nz www.rxplastics.co.nz

AIR GAP (AG) Low Hazard High Hazard

AIR GAP (AG) On Low Hazard and High Hazard applications, Air Gap (AG) is used for the physical separation (vertical distance) between the lowest opening point from any pipe or outlet supplying water and

TEMPERATURE STABILISED THERMOSTATIC SHOWER PANEL

Product Support Guarantee This product is guaranteed against faulty materials and workmanship for 12 months from date of purchase. For the guarantee to be valid, the unit must be installed by a competent

INSTALLING AN INEXPENSIVE AIR LINE TO MEASURE WATER DEPTHS IN WELLS

INSTALLING AN INEXPENSIVE AIR LINE TO MEASURE WATER DEPTHS IN WELLS Joe Henggeler Extension Agricultural Engineer-Irrigation An inexpensive, yet highly accurate, device to measure the depth to water in

Sterisil Ac+ Installation & Operating Manual

Sterisil Ac+ Installation & Operating Manual 719 622 7200 Sterisil.com Arbor Dental Associates 2 Table of Contents Introduction 4 Sterisil Ac + Features 5 Installation Instructions 6 Maintenance 10 Troubleshooting

Mounting and Operating Instructions EB EN. Type Supply Pressure Regulator. with increased air capacity

Type 4708-45 Supply Pressure Regulator with increased air capacity Translation of original instructions Mounting and Operating Instructions EB 8546-1 EN Edition March 2016 Note on these mounting and operating

No. 9192 REGISTRATION EXAMINATION, NOVEMBER 2015 LICENSED PLUMBER ANSWER SCHEDULE Plumbers, Gasfitters and Drainlayers Board, 2015. All rights reserved. No part of this publication may be reproduced by

Halsey Taylor Owners Manual 4410 Freeze Resistant Tubular Fountain STOP!

Halsey Taylor Owners Manual 4410 Freeze Resistant Tubular Fountain STOP! PLEASE READ THE FOLLOWING INFORMATION. ITALLATION ITRUCTIO FOR THE 4410FR FTN. WITH 97243C SINGLE VALVE CONTROL ASSEMBLY ARE LOCATED

book : t95575.fm Seite 1 Mittwoch, September 20, :10 AM. Avensys. Exposed Single Lever Mixer

955751.book : t95575.fm Seite 1 Mittwoch, September 20, 2000 10:10 AM Avensys Exposed Single Lever Mixer 33 389 33 396 Installation Instructions and Operating Guide Please leave this document with the

The Glockemann Pump Site & Installation Guide

GLOCKEMANN PECK ENGINEERING PTY LTD P.O. Box 357 West Ryde NSW 1685 Telephone/Fax: (02) 9708 0900 Email: glocpump@zip.com.au Internet: www.gpe-waterpumps.com The Glockemann Pump Site & Installation Guide

User's Manual. MixRite TF 10. Edition 05.08

User's Manual MixRite TF 10 Edition 05.08 1 Tefen MixRite TF 10 fertilizer and chemicals Injector Congratulations on your purchase of one of Tefen s high quality products. To get the best results from

Pressure switches for air and water CS

Data sheet Pressure switches for air and water CS CS pressure switches have a built-in pressure operated, three-pole switch. The contact position of which depends on the pressure in the connector and the

TECHNICAL BENEFITS OF CJS / RAISE HSP. Technical Advantages

TECHNICAL BENEFITS OF CJS / RAISE HSP Technical Advantages The HSP is designed for low- to mid- volume applications at flow rates of 1 cubic meter to 30 c. m per day. The benefits are in the details. The

Consult with manufacturers concerning permeation of the pipe walls, jointing materials, valve seats, etc.

Design Manual Chapter 4 - Water Mains 4C - Facility Design 4C-1 Facility Design A. General Water mains and appurtenances, including hydrants and valves, should be provided along all streets including connections

Reverse Osmosis System Installation Guide and Operation Manual.

Reverse Osmosis System Installation Guide and Operation Manual. Table of Contents 1 Introduction...2 2 Installation...3 2.1 Feed water connection...3 2.2 Permeate and concentrate plumbing...3 2.3 Electrical

Appendix B Harris County Standard Operating Procedure for Determining In Situ Hydraulic Performance of High Flow Rate Bioretention Media

Objective Appendix B Harris County Standard Operating Procedure for Determining In Situ Hydraulic Performance of High Flow Rate Bioretention Media Provide as-built confirmation of proper installation and

Warning: NEVER ALTER TEST EQUIPMENT

PAGE 1 OF 6 General: Pressure Testing Shop Built Tanks Pressure testing tanks with either positive pressure or vacuum can be a very dangerous exercise. It is important to understand the equipment involved

Apricot Kitchen Sink Tap

Apricot Kitchen Sink Tap Installation Instructions & User Guide Please keep these instructions for future reference and request of replacement parts Contents Thank you for choosing Bristan, the UK s leading

Gas Check. Short testing time, with automatic start-up if no leakage was detected from previous operation.

Quality Products at Competitive Prices Gas Check Automatic testing of the down-stream installation to check that all valves are closed and that pipework and fittings are gas tight before each system start-up.

Calcium Reactor. CalcFeeder PRO. User Manual 1.1a. Model. CalcFeeder AC1 PRO CalcFeeder AC2 PRO CalcFeeder AC3 PRO CalcFeeder AC4 PRO

Calcium Reactor CalcFeeder PRO User Manual 1.1a Model CalcFeeder AC1 PRO CalcFeeder AC2 PRO CalcFeeder AC3 PRO CalcFeeder AC4 PRO Page 1 Dear Customer, Thank you for purchasing an Pacific Sun CalcFeeder

RB70 Automatic Diluent Valve Maintenance Manual. Version 1.1 November 2006 Written by Tino de Rijk. Page 1 of 23

RB70 Automatic Diluent Valve Maintenance Manual Version 1.1 November 2006 Written by Tino de Rijk Page 1 of 23 Table of Contents 1. Introduction... 3 2. ADV diagram and parts list (Pre June 2006)... 4

Materials : Brass body dezincification-resistant up to DN1 1/4

Size : Ends : Min Temperature : Max Temperature : DN 1/2" to 2" Male, Male BSP + 5 C + 65 C Max Pressure : 10 Bars Specifications : Brass body dezincification-resistant up to DN1 1/4 Controlable With male

THERMOSTATIC MIXING VALVES

THERMOSTATIC MIXING VALVES D1088 & D1089 INTRODUCTION Are self-acting Thermostatic Mixing Valves designed to blend hot and cold water, to ensure a constant, safe outlet temperature and prevent scalding.

AIR HAMMERS MODEL NO: CAT138/CAT139 OPERATING & MAINTENANCE INSTRUCTIONS PART NO: / GC064

AIR HAMMERS MODEL NO: CAT138/CAT139 PART NO: 3120152 /3120153 OPERATING & MAINTENANCE INSTRUCTIONS GC064 INTRODUCTION Thank you for purchasing this CLARKE Air Hammer. Before attempting to use this product,

North American Orifice Metering System

Combustion North American Orifice Metering System 8697 and M8697 Metering Orifices accurately measure gas flows to industrial burners. They are compact, inexpensive, and can be installed in individual

Installation, Operating, Maintenance and Safety Instructions for. Pressurised water systems for boats

FLOMAX-SYSTEM DOC532/11 Installation, Operating, Maintenance and Safety Instructions for FLOMAX-SYSTEM Pressurised water systems for boats CW343A FloMax System 12 volt d.c. CW344A FloMax System 24 volt

Installation Guide Wall Mounted Angled Flagpole

Installation Guide 1.5m - 4m Angled Flagpole Dimensions Flagpole Dimensions Wall Bracket Dimensions 2m Aluminium 76mm Glassfibre 114.3mm angle from vertical 2000mm 250mm 300mm 1715mm Backplate thickness

SIZING OF WATER PIPING SYSTEM

SIZING OF WATER PIPING SYSTEM (This appendix is informative and is not part of the code.) SECTION AP101 GENERAL AP101.1 Scope. AP101.1.1 This appendix outlines two procedures for sizing a water piping

Technical Data Sheet TI-F50 Locking Units series KFH

English translation of German original Locking Units series KF Further important practical advice is given in Operating Manual BA-F50., Rod diameter 18 mm 50 mm øz 8 L 2 6 x 6 0 min. 4x30 KF 18 to KF 32,

AutoDrill s OUTSTANDING FEATURES

PRODUCTION DRILLING & TAPPING SOLUTIONS Reduce Your Costs and Increase Your Production The Affordable, Powerful, Compact Solution AutoDrill s OUTSTANDING FEATURES Self Feeding with Air or Oil Thrust Capacity

Squeegee Unit for MRS Multi-Recovery System

En Operating Instructions Squeegee Unit for MRS Multi-Recovery System Translation of the original operating instructions Squeegee - MRS Table of Contents Safety Recommendations Technical Data - MRS Booth

NEXT GENERATION FLEX FENCE

NEXT GENERATION FLEX FENCE Area To Be Fenced.. With Next Generation Flex Fence any post that is not in a straight line with another post must be braced. Layout your fence installation. Determine all end

HERZ-Motorised flow controler

HERZ-Motorised flow controler Control and regulating valve Data sheet 46, Issue 214 Dimensions in mm 4 close dimension 9,35 M DN G H1 H2 H2 + Actuator B1 B2 1 2 M 1 46 11 15 3/4 G 66 59 73 134 49 63 48

K-LINE Irrigation Farm Packs

K-LINE Irrigation Farm Packs 3 Pod, 4 Pod and 5 Pod Farm Packs with 32mm K.PIPE and Naan 5022 Sprinklers Installation and user manual RX PLASTICS LTD PO Box 360 Ashburton Phone +64 3 307 9081 Email sales@rxplastics.co.nz

GYROSTATIC DELIVERY TECHNIQUE By Macka Jensen

GYROSTATIC DELIVERY TECHNIQUE By Macka Jensen Knowledge dispels fear 1. INTRODUCTION Gyrostatic technique: The application of these factors in the gyrostatic delivery technique is based on the principle

Manual Actuated Boiler Blowdown Valves

Manual Actuated Boiler Blowdown Valves Installation and Maintenance Instructions 1. Safety information 2. General product information 3. Installation 4. Operation 5. Maintenance 6. Spare parts p.1 1. Safety

Engineered Air Nozzles reduce noise levels and air costs.

Air Nozzles Engineered Air Nozzles reduce noise levels and air costs. " Go Green" by upgrading your blowoff, cooling, and drying operation to the award winning Super Air Nozzles! What Are Air Nozzles?

INSTRUCTION MANUAL CZ 630/631

INSTRUCTION MANUAL CZ 630/631 Before handling the air rifle read this manual carefully and observe the following safety instructions. Improper and careless handling of the air rifle could result in unintentional

www.firsttunnels.co.uk/quality Overhead Irrigation Installation Guide DOM Copyright First Tunnels Ltd 2012. Warnings General Please keep children and pets away from the work area. If any holes are not

Hyquest Solutions Pty Ltd

INSTRUCTION MANUAL BUBBLERS MODELS HS23SL / HS23DL / HS23DO QUALITY SYSTEM ISO: 9001 CERTIFIED HYQUEST SOLUTIONS PTY LTD PO BOX 332, LIVERPOOL B.C NSW 1871, AUSTRALIA Phone:(Int.) 612 9601 2022 Fax: :(Int.)

ambiente Installation Guide AmbiScreedboard system more than underfloor Customer: Project: Project Reference: Date:

ambiente more than underfloor Customer: Project: Project Reference: Installation Guide AmbiScreedboard system Date: AmbiSCREEDBOARD installation guide AmbiSCREEDBOARD Series Contents Slimline 18mm board

Components for air preparation and pressure adjustment. OUT port position ( ) connected Rear side. of IN port. Air tank. directly.

Components preparation and pressure adjustment ABP Overview ABP is a component that enables boosting by s only up to twice primary pressure (.0MPa max.) in combination with using air tank but not using