# Product Catalogue MINICOMB. Switches for Pressure and Vacuum

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 Product Catalogue MINICOMB Switches for Pressure and Vacuum PL ATEX

2 2 DEFINITION OF PRESSURE A force applied uniformly over a certain area is called pressure: p = F / A (pressure = force / area) Pressure (P) besides temperature is one of the most frequently measured physical units. The unit Pascal (Pa) is the SI unit of pressure within the metric unit system. In Europe bar is the most commonly used (SI) unit. It roughly equals with the magnitude of the atmospheric pressure. 1 bar = 0,1 MPa = 0,1 N/m 2 = 10 5 Pa Particularly in the anglo-american influenced region psi (pounds per square inch) is the most common unit. The general term pressure is not always very clear: In technical usage several types of pressure are differentiated, mainly differences between two pressure points, which in general linguistic usage all are called pressure. To avoid confusion, the various types of pressure are distinguished according to their point of reference: Absolute Pressure (Pabs) Absolute pressure always refers to the absolute vacuum, i.e. the zero-point is the absolute vacuum. A pressure gauge with measuring range 0-10 bar absolute shows the current ambient pressure (Pamb) when in nonoperating state/not installed. Ambient Pressure (Pamb) The atmospheric pressure is the ambient pressure. Atmospheric Pressure Difference (Pe) The atmospheric pressure difference, also called positive pressure (Pe+) respectively negative pressure (Pe-) is the most commonly measured type of pressure in the technical field. It refers to atmospheric pressure (Pamb) and is the difference between the atmospheric pressure (Pamb) and absolute pressure (Pabs). Pe = Pabs - Pamb Pe becomes positive when the absolute pressure is higher than the athmospheric pressure; Pe becomes negative when the absolute pressure is lower than the atmospheric pressure. A pressure gauge with measuring range 0-10 bar relative shows 0 bar when in nonoperating state/ not installed. Differential Pressure (DP) Differential pressure is the pressure difference ( P) between to measured pressures (P1, P2). P = P1 - P2 Differential pressure instruments are universal, as they can be used to as a relative pressure instrument or for hydrostatic level measurement.

3 3 WHAT IS A PRESSURE SWITCH? Pressure switches are signal elements, that can be used for measuring pressure in pressure lines for gases, vapours or liquids. Once the switching contact is triggered, setted pressure values are transformed into electrical or pneumatic signals which are necessary for the In general pressure switches have one or more fixed or adjustable switching contacts. Each switching contact has a setpoint ( SP). This setpoint corresponds to a pressure value setted on the pressure switch. When rising above or falling below this value the switching contact within the pressure switch is triggered. Due to inaccuracy the re-set point ( BSP) does not exactly match the setpoint. The difference between setpoint and re-setpoint is called hysteresis or switching differential ( SD) control and regulation of processes, e.g. safety and alarm devices. WHAT IS A MINICOMB PRESSURE SWITCH? The MINICOMB pressure switch series is a very compact-sized pressure switch for measuring compressed air, low-viscous media and non-aggressive gases. It is based on a force-balance measuring system with bellows sensors actuating one switching contact. The MINICOMB pressure switch series is approved for applications where PLc (Performance Level according to ISO 13849) is at least required (PLr) as well as for applications within hazardous area (zone 2 / 22 according to ATEX Directive 94/9/EC). The force-balance measuring system with bellows sensors is friction-free and features high repeatability and very good longterm-stability. The MINICOMB is available with pressure range 0,2-16 bar, -0,9-0 bar or -0, bar. Sub-base mounting or female threads are availbe for connecting to the process, while 4-pin plug according to ISO 4400 or plug M12x1 are available for electrical connection.

4 4 MINICOMB Pressure Switch friction-free force-balance measuring system high repeatability very good longterm stability pressure ranges -0, (+1) bar or 0,2-16 bar process connection 1/4 ISO 228 female or subbase mounting electrical connection plug ISO 4400 or plug M12x1 approved for applications with PLr = PLc approved for ATEX zones 2 / 22 MINICOMB with sub-base mounting Description The MINICOMB Series is a very compact-sized pressure switch for measuring compressed air, low-viscous media and non-aggressive gases. Operating Principle The principle of operation is the balance of forces. The working force within each bellow is counter-balanced by adjustable steel springs. This system actuates a microswitch when the working pressure overcomes the opposing force. The measuring system operates without any pistons or diaphragms, thus completly friction-free, resulting in minimal wear and no maintenance. MINICOMB with 1/4 female ISO 228 thread Approvals PL ATEX Performance Level (ISO 13849) PLc ATEX-Directive 94/9/EC Zone 2 / Zone 22

5 5 Technical Data Standard Options Function Life Cycle Pressure Range Vacuum Range Pressure-/Vacuum Range) Overpressure Safety Vacuum Safety Enclosure Material mechanical pressure switch; force-balance measuring system with bellows sensor at least 10 mio switch cycles 0,2-16 bar -0,9-0 bar -0, bar 25 bar -1 bar Aluminium Wetted Parts Material Aluminium, Brass, NBR (Gasket) FKM (Gasket) Permissalbe Media Temperature Permissable Ambient Temperature C C Temperature Deviation approx. 1% per 20 C Factory Adjustment Temperature 20 C on request Switching Contact Adjustment Accuracy Switching Accuracy Repeatability 1 micro switch (SPDT) < 1,0% FS < 1,0% FS < 1,0% FS Switching Differential (Hysteresis) < 4,0% FS on request Process Connection (alternatively) Electrical Connection (alternatively) Weight Protection sub-base mounting; sub-base mounting CNOMO; 1/4 female ISO 228 thread; Stecker EN A (ISO 4400); Stecker M12x1 approx. 160 g IP65 (IP67 with plug M12x1) Schock Resistance (XYZ-Direction) 15 g (IEC ) Vibration Resistance (XYZ-Direction) 10 g ( Hz) (IEC )

6 6 DIMENSIONS (VERSION WITH PLUG ISO 4400) MINICOMB sub-base mounting and plug ISO 4400 MINICOMB sub-base mounting CNOMO and plug ISO 4400 MINICOMB 1/4 female ISO 228 thread mounting and plug ISO 4400

7 7 DIMENSIONS (VERSION WITH PLUG M12X1) MINICOMB sub-base mounting and plug M12x1 MINICOMB sub-base mounting CNOMO and plug M12x1 MINICOMB 1/4 female ISO 228 thread mounting and plug M12x1

8 8 ELECTRICAL DATA Category AC-12 / DC-12 Switching Capacity max. steady current I max [A] on inductive load Electrical Connection shown in zero pressure condition version with plug ISO4400 version with plug M12x1 U [V] 30V 48V 60V 125V 250V I [A] AC I [A] DC 2 0,55 0,4 0, I [A] AC I [A] DC plug ISO 4400 plug M12 reference switch cycle: 30/min reference temperature: +30 C AC = cos phi ca. 0,7 DC = L/R ca 10ms Switching Capacity max. steady current I max [A] on ohmic load U [V] 30V 48V 60V 125V 250V micro switch plug ISO4400 plug M12 +UB 1 1 normally closed 2 2 normally open 3 4 GND version with plug ISO4400 version with plug M12x1 I [A] AC I [A] DC 3 1,2 0,8 0,4 --- I [A] AC I [A] DC reference switch cycle: 30/min reference temperature: +30 C

9 9 ORDER-CODES most common options Pressure Range Electrical Connection Process Connection Remarks Order-Code Sub-base mounting 1 C0011F-199-PAO ATEX, 1 C0111F-199-PAO ISO 4400 Sub-base mounting CNOMO 1 C0011F-199-CAO 0,2-16 bar 1/4 female ISO 228 thread Sub-base mounting 2 C0051F-199-4AO ATEX, 2 C0151F-199-4AO 1 C0011F-199-PDO ATEX, 1 C0111F-199-PDO M12 Sub-base mounting CNOMO 1 C0011F-199-CDO 1/4 female ISO 228 thread 2 C0051F-199-4DO ATEX, 2 C0151F-199-4DO -0,9...0 bar ISO 4400 M12 Sub-base mounting 1/4 female ISO 228 thread Sub-base mounting 1/4 female ISO 228 thread 1 C0011F-300-PAO ATEX, 1 C0111F-300-PAO 2 C0051F-300-4AO ATEX, 2 C0151F-300-4AO 1 C0011F-300-PDO ATEX, 1 C0111F-300-PDO 2 C0051F-300-4DO ATEX, 2 C0151F-300-4DO -0, bar ISO 4400 M12 Sub-base mounting 1/4 female ISO 228 thread Sub-base mounting 1/4 female ISO 228 thread 1 C0011F-301-PAO ATEX, 1 C0111F-301-PAO 2 C0051F-301-4AO ATEX, 2 C0151F-301-4AO 1 C0011F-301-PDO ATEX, 1 C0111F-301-PDO 2 C0051F-301-4DO ATEX, 2 C0151F-301-4DO 1) Counter plug and installation screws within scope of delivery 2) Counter plug within scope of delivery

10 10 CONVERSION TABLE FOR PRESSURE UNITS

11 11 INQUIRY CHECKLIST PRESSURE SWITCHES (BY FAX TO )

12 PINTER Mess- und Regeltechnik GmbH Kraichgaublick 17 Technologiepark Neckartal-Odenwald Obrigheim, Germany Phone Fax Internet All given information and/or technical data in this document have been prepared very carefully and reflect the state of the art when printed. Information and/or technical data may change without prior notice. All given information and/or technical data in this document are not binding and for information purposes only. Binding information and/or technical data can be obtained from our quotations and/or order confirmations. Please understand that we cannot be held responsible for the correctness of any given information and/or technical data in this document. When installing or maintaining PINTER products always refer to the corresponding operating manual and technical data sheet. All mentioned product names, product designations, product descriptions and logos are trademarks and property of their respective owners. CHEMSEAL, DIMIO, INDUSENS, INDUSWITCH, INTELLICOMB, MA- NOCOMB, MINICOMB are trademarks and/or registered trademarks of the PINTER Mess- und Regeltechnik GmbH and/or their affiliated companies in Germany, the European Union, Switzerland and/or other countries. The use of PINTER trademarks is prohibited if not clearly agreed otherwise. CATALOGUE.MINICOMB.12R3.EN

### Product Catalogue. P-SERIES Pressure Gauges

Product Catalogue P-SERIES Pressure Gauges 2 3 CONTENT INTRODUCTION PRESSURE GAUGES...4 P-SERIES (Gauges for Pressure and Vacuum)...6-25 P-SERIES Model P1 (Stainless Steel Bourdon-Tube Pressure Gauge)...6

### Electropneumatic Positioner and Pneumatic Positioner Type 3760 JIS

Electropneumatic Positioner and Pneumatic Positioner Type 3760 Application Single-acting positioners for direct attachment to pneumatic control valves. Supplied with an electric input signal of 4 to 20

### 1 Overview. Pressure Measurement Single-range transmitters for general applications. 1/16 Siemens FI US Edition

Siemens AG 206 Overview Design Device structure without explosion protection The pressure transmitter consists of a piezoresistive measuring cell with a diaphragm installed in a stainless steel enclosure.

### Bourdon tube pressure gauge for diaphragm seals

Bourdon tube pressure gauge for diaphragm seals and switch function, Type series BR42.. Features Bourdon tube pressure gauge for diaphragm seal and switch function Nominal range -1 3 bar to -1 15 bar,

### Compact differential pressure switch Flameproof enclosure Ex d Models DE, DEC

Mechatronic pressure measurement Compact differential pressure switch Flameproof enclosure Ex d Models DE, DEC WIKA data sheet PV 35.41 Process Compact Series Applications Differential pressure monitoring

### Pressure Switches Application Guideline

Pressure Switches Application Guideline Product Overview The Fema Pressure Switch product portfolio provides devices suitable for many applications. The portfolio contains Special functions and equipment

### Proportional pressure regulators VPPE

Proportional pressure regulators VPPE Proportional pressure regulators VPPE Product range overview Function Version Pneumatic connection Proportional pressure regulator Nominal size for pressurisation/

### Mass Flow Controller (MFC) for Gases

Mass Flow Controller (MFC) for Gases Bypass MFC with capillary technology for nominal flow rates from 5 ml N /min to 15 l N /min Applicable for aggressive gases Compact design and digital communication

### Mounting and Operating Instructions EB EN. Type Supply Pressure Regulator. with increased air capacity

Type 4708-45 Supply Pressure Regulator with increased air capacity Translation of original instructions Mounting and Operating Instructions EB 8546-1 EN Edition March 2016 Note on these mounting and operating

### Mechanical pressure switches

18 Technical features / Advantages Diecast aluminium housing IP 54 or IP 65 version also available Wall mounting or directly on the pressure line Switching element (microswitch) Lead sealable setpoint

### Gas Pressure Switch for DMV safety shutoff valves

Gas Switch for DMV safety shutoff valves GAO-A GMH-A GML-A UL Listed UL 353 File # MH 1668 CSA Certified CSA C. No. LR 53 File # 0157 FM Approved Class 3510, 3530 File # J.I. 1Y9A9.AF Commonwealth of Massachusetts

### Differential pressure gauge For the process industry Model , all-metal media chamber

Pressure Differential pressure gauge For the process industry Model 732.51, all-metal media chamber WIKA data sheet PM 07.05 for further approvals see page 4 Applications For gaseous and liquid aggressive

### How to specify a product. Process Sensors and Mechanical Instruments

How to specify a product Process Sensors and Mechanical Instruments Keep the overview. Here is some guideline information on how to specify our products. Intended as supplementary help to specification

### Pressure switch Type BCP

Data sheet Pressure switch Type BCP The BCP type is a series of dedicated switches for safety and monitoring of steam and hot water boilers. The BCP incorporates a single-pole changeover microswitch where

### Glass tube flowmeters Series 2000 Variable area flowmeter for low flows of liquids and gases

Glass tube flowmeters Series 2000 Variable area flowmeter for low flows of liquids and gases Short mounting length and compact construction, especially indicated for control panels Easy installation. No

### Old documentation - Only for your information! Product is not available anymore!

Double solenoid valve Regulator and safety combination Infinitely variable floating operation DM-EF 07-7. Printed in Germany Rösler Druck Edition 0.0 Nr. 9 Flanges, pressure switches, line sockets, pulse

### MANUAL KPS Pressure Control Valve

TetraTec Instruments GmbH Gewerbestrasse 8 71144 Steinenbronn Deutschland E-Mail: info@tetratec.de Tel.: 07157/5387-0 Fax: 07157/5387-10 MANUAL Pressure Control Valve *** VERSION 1.0 *** Update: 17.11.2006

### Pressure switch and Thermostat KPS

Data sheet Pressure switch and Thermostat KPS The KPS Series consists of a series of pressure and temperature controlled switches. In this series, special attention has been given to meeting demands for

### SITRANS. Pressure transmitter SITRANS P, Z series for gauge and absolute pressure. Introduction. Safety instructions 2.

Introduction 1 Safety instructions 2 SITRANS Pressure transmitter SITRANS P, Z series for gauge and absolute pressure 7MF1564 Description 3 Assembly and connection 4 Technical data 5 Dimensional drawings

### Gas Pressure Regulator HON 300

Product information serving the gas industry worldwide Applications, characteristics, technical data Applications direct acting gas pressure regulator, for systems in accordance with DVGW working instruction

### GasMultiBloc Combined regulating and safety valve Infinitely variable air/gas ratio control mode MB-VEF B01

GasMultiBloc Combined regulating and safety valve Infinitely variable air/gas ratio control mode MB-VEF 407-42 B0 7.27 Flange, line sockets, pulse lines and screw unions are not contained in the scope

### Pressure Measurement Single-range transmitters for general applications

Siemens A 207 Overview Application The SITRANS P Compact pressure transmitter is designed for the special requirements of the food, pharmaceutical and biotechnology industries. The use of high-grade materials

### Operating instructions Safety Rope Emergency Stop Switches ZB0052 / ZB0053 ZB0072 / ZB0073

Operating instructions Safety Rope Emergency Stop Switches UK ZB0052 / ZB0053 ZB0072 / ZB0073 7390878 / 02 03 / 2011 Contents 1 Safety instructions...3 2 Installation / set-up...4 2.1 Applications...4

### GasMultiBloc Combined regulator and safety valve Infinitely variable air/ gas ratio control mode MBC-300-VEF MBC-700-VEF MBC-1200-VEF

GasMultiBloc Combined regulator and safety valve Infinitely variable air/ gas ratio control mode MBC-00-VEF 7.03 Max. operating pressure 30 mbar Compact design High flow values Low weight Low power consumption

### SCH. Mechanical Pressure Switches. for overpressure, vacuum pressure and differential pressure

Mechanical Pressure Switches for overpressure, vacuum pressure and differential pressure measuring monitoring analysing SCH P3 OO Switching range: -1... + 0.1 bar - 250... +100 mbar, 1... 16 mbar a 16...

### Pressure switches and thermostats, type KPS

Description KPS units are pressure-controlled switches. The position of the contacts depends on the pressure in the inlet connection and the set scale value. In this series, special attention has been

### Pressure Switch for gas and air

Switch for gas and air GAO-A4 GMH-A4 GML-A4 UL Listed UL 353 File # MH 16628 CSA Certified CSA C22.2 No. LR 53222 Certification file # 201527 FM Approved Class 3510, 3530 File # J.I. 1Y919.AF Commonwealth

### Hand lever valves VHER

Hand lever valves VHER Hand lever valves VHER Key features Powerful Flexible Practical -M- Flow 170 3800 l/min 4/3-way valve mid-position closed mid-position exhausted mid-position pressurised Connections:

### DM01. Battery Powered Precision Digital Gauge. Stainless Steel Sensor. class 0.05

Battery Powered Stainless Steel Sensor class 0.05 Nominal pressure from 0 00 mbar up to 0... 00 bar Special characteristics modular sensor concept data logger graphic display stainless steel housing Ø

### Self-operated Pressure Regulators Type 2405 Pressure Reducing Valve

Self-operated Pressure Regulators Type 2405 Pressure Reducing Valve ANSI version Application Pressure reducing valve for set points from 0.075 to 150 psi (5 mbar to 10 bar) Valve size NPS ½ to 2 1) (DN

### Contents. Operating instructions. Pressure switch, heavy-duty version Model PSM-520

Operating instructions Contents EN Pressure switch, heavy-duty version Model PSM-520 1. General information 2. Design and function 3. Safety 4. Transport, packaging and storage 5. Commissioning, operation

### ED 701 Hygenic Pressure Transmitter

ED 701 Hygenic Pressure Transmitter Hygienic process connections Complete range of electrical connections 4... 20 ma and Voltage outputs Accuracy: 0.1%, 0.2% and 0.4% FS Quick response time < 25 ms (Option

### Gas Pressure Switch for DMV safety shutoff valves

Gas Switch for DMV safety shutoff valves GAO-A GMH-A GML-A UL Listed UL 353 File # MH 1668 CSA Certified CSA C. No. LR 53 File # 0157 FM Approved Class 3510, 3530 File # J.I. 1Y9A9.AF Commonwealth of Massachusetts

### Precision pressure regulators LRP/LRPS

Precision pressure regulators LRP/LRPS q/w Worldwide: Superb: Easy: Festo core product range Covers 80% of your automation tasks Always in stock Festo quality at an attractive price Reduces procurement

### Mounting and Operating Instructions EB 3009 EN. Self-operated Regulators. Type RS Check Valve (backflow protection)

Self-operated Regulators Type 42-10 RS Check Valve (backflow protection) Type 42-10 RS Check Valve (backflow protection) Mounting and Operating Instructions EB 3009 EN Edition December 2015 Definition

### ETd 04. Battery Powered Precision Digital Gauge. Stainless Steel Sensor. Type: ETd 04. class 0.05

Battery Powered Stainless Steel Sensor class 0.05 Nominal pressure from 0 100 mbar up to 0... 400 bar Special characteristics modular sensor concept data logger graphic display stainless steel housing

### Bourdon tube pressure gauges with glycerine filling, for chemical applications EN 837-1

Application For aggressive gaseous and liquid media which are not highly viscous and do not crystallize. Suitable for use in corrosive atmospheres. For measurement in areas subject to high vibration levels

### Pressure & Temperature Switches

Pressure & Temperature Switches The User Friendly Generation General Bulletin TEMPERATURE SWITCHES BETA TEMPERATURE SWITCH The BETA Temperature Switch is a pressure switch incorporating a sealed 2-phase

### ATM.1ST. Pressure transmitters CUSTOMER BENEFITS

Pressure transmitters ATM.1ST CUSTOMER BENEFITS High precision pressure sensor over the whole temperature range Electronic compensation Modular sensor structure (any process and electrical connections

### High-speed pressure sensor Model CPT6140

Calibration technology High-speed pressure sensor Model CPT6140 WIKA data sheet CT 25.11 Applications Testing technology Calibration technology Laboratories and maintenance shops Leak and burst applications

### Pressure Measurement

Pressure Measurement Manometers Sensors, Transducers Ashish J. Modi Lecturer, Dept. of Mech.Engg., Shri S.V.M. inst. Of Technology, Bharuch Pressure Pressure is a force per unit area exerted by a fluid

### Gas Pressure Regulator HON 200

Product information serving the gas industry worldwide Applications, characteristics, technical data Application Gas supply to municipal, industrial and individual consumers Regulator for low-load rails

### Pressure Measurement Single-range transmitters for general applications

Siemens AG 07 Overview Function U const. p U I EM Sensor Connection for auxiliary power supply Vent pipe with humidity filter Protective conductor connection/ Equipotential bonding Diaphragm The pressure

### Safety Shut-Off Valve RMG 711

Safety Shut-Off Valve RMG 711 Product information serving the gas industry worldwide Application, Features, Technical Data Application safety device for gas pressure regulating stations suitable for natural

### Pressure gauges EN All stainless steel construction PBX100, PBX150 (1.18) Functional and constructive characteristics

Pressure gauges FT PBX 100-150-E-9.02 All stainless steel construction PBX100, PBX150 (1.18) EN 837-1 These instruments are designed for use in food, beverage, pharmaceutical, cryogenics, chemical and

### Programmable pressure and temperature transmitters PTM/RS485

Programmable pressure and temperature transmitters PTM/RS485 Version: 26.06.2014 Technical Specifications Pressure measuring range (bar) 0.1... 0.5 > 0.5 2 > 2 25 Overpressure 3 bar 3 x FS ( 3 bar) 3 x

### Self-operated Pressure Regulators Type 2405 Pressure Reducing Valve

Self-operated Pressure Regulators Type 2405 Pressure Reducing Valve Application Pressure reducing valve for set points from 5 mbar to 10 bar Nominal size DN 15 to 50 Nominal pressure PN 16 to 40 Suitable

### safety Shut-Off Valve HON 721

safety Shut-Off Valve HON 7 product information serving the gas industry worldwide safety shut-off valve HON 7 safety shut-off valve HON 7 Application, Characteristics, Technical Data Application safety

### Proportional Throttle Cartridges, Size 16

Proportional Throttle Cartridges, Size 16 Q max = 5 l/min, p max = 5 bar, Q N max = 14 l/min at p 1 bar Two-Stage, with Seat-Valve Shut-Off 1 Description Normally closed Seat-valve shut-off from 1 Compact

### Types and approvals. Page 1/6. Data Sheet

Page 1/6 Panel-mounting Thermostats EM Series as: Protection temperature monitor STW (STB) Protection temperature limiter STB tested to DIN 3440 and Pressure Equipment Directive 97/23/EC Brief description

### SPD Pressure Sensor Families

DATASHEET SPD Pressure Sensor Families 1/7 Introduction to the principals of Smart Pressure Devices 1 Basic principles Pressure sensors are based on the principle of bending a membrane caused by the pressure

### Relative pressure switch type 521

Relative pressure switch type 521 Pressure range 0... 2.5 600 bar The compact type 521 pressure switch is based upon the Huba Control developed thick film technology where the pressure measuring cell is

### Solenoid valve type EVR for Hydrocarbons

MAKING MODERN LIVING POSSIBLE Technical brochure Solenoid valve type EVR for Hydrocarbons EVR for Hydrocarbons is a direct or servo operated solenoid valve especially designed for liquid, suction, and

### Level transmitter LT 100

KROHNE 09/2001 7.02363.21.00 GR/PRINTO Level transmitter LT 100 Status: 10/99 Variable area flowmeters Vortex flowmeters Flow controllers Electromagnetic flowmeters Ultrasonic flowmeters Mass flowmeters

### sitrans p Operating Instructions (de/en) Edition 03/2004

(de/en) Edition 03/2004 sitrans p Messumformer für Food, Pharma und Biotechnik Transmitters for food, pharmaceuticals and biotechnologgy 7FM8010 Contents Information for the operator...27 Important security

### Pressure measurement. Pressure gauges

Pressure gauge Pressure measurement There are four types of pressure measurements: Measurement of absolute pressure : Measurements are made with respect to absolute pressure, for example as with atmospheric

### Ratio Regulator Zero Governor. FRG/6 Series

Ratio Regulator Zero Governor FRG/6 Series CSA Certified ANSI Z21.18 / CSA 6.3 CSA Requirement # 5.01 Zero Governor and Gas/Air Regulator File # 157406 US and Canadian Models FRG 705/6 FRG 707/6 FRG 710/6

### Chapter 1: Basic Concepts of Pneumatics

Right of authorship: the content of the training (wording, drawings, pictures) are owned by the author. Any utilization except for individual use is allowed only after permission of the author. What is

### KTE6000 / KTU6000 Series OEM pressure transmitters for industrial media

FEATURES 50 mbar to 400 bar, 5 to 6000 psi gage or absolute pressure For many industrial gases and liquids 00, 0545, 05, 6 or 40 ma output Field interchangeable EMC according to EN 66-8 MEDIA COMPATIBILITY

### DSL, DSH: Specially designed pressure limiter

Product data sheet 11.1 23.770 DSL, DSH: Specially designed pressure limiter How energy efficiency is improved Control and monitoring according to needs and with no auxiliary energy. Features Switching

### Safety Shut-Off Valve HON 720

Safety Shut-Off Valve HON 70 Product information serving the gas industry worldwide Application, Characteristics, Technical Data Application main safety device for gas pressure regulating stations suitable

### Hydraulic hand test pump Models CPP700-H and CPP1000-H

Calibration technology Hydraulic hand test pump Models CPP700-H and CPP1000-H WIKA data sheet CT 91.07 for further approvals see page 2 Applications Simple test pressure generation on site, in the laboratory

### Mounting and Operating Instructions EB 3007 EN. Self-operated Pressure Regulators. Differential Pressure Regulators (opening) Type Type 42-25

Self-operated Pressure Regulators Differential Pressure Regulators (opening) Type 42-20 Type 42-25 Type 42-20 Differential Pressure Regulator Type 42-25 Differential Pressure Regulator Mounting and Operating

### Mounting and Operating Instructions EB 9520 EN. Differential Pressure and Flow Meter Media 05

Differential Pressure and Flow Meter Media 05 Fig. 1 Media 05, indicating unit with differential pressure cell, with valve block and pressure gauge (right) Mounting and Operating Instructions EB 9520 EN

### XML Electromechanical Pressure Switches

Selection Guide Industrial Switches Type of installation ontrol circuits Applications Media controlled Type of operation Air, water, hydraulic oils, corrosive fluids, viscous products Fixed differential:

### 3-Way Safety Block DSV

3-Way Safety Block DSV DSV 10 - M DSV 10 - M - T-ball DSV 10 - EY 1. Description 1.1. GENERAL The 3-way safety block is used to shut off and discharge hydraulic accumulators or consumers. It complies with

### AMS 2710 PCB pressure sensor module with V output

FEATURES Universal pressure sensor module with 0.. 10 V voltage output Fully calibrated and temperature compensated sensor module Variants for (bidirectional) differential, gage, absolute and barometric

### Programmable pressure and temperature transmitters PTM/RS485

Programmable pressure and temperature transmitters PTM/RS485 Version: 03-28-2012 Technical Specifications Pressure measuring range (bar) 0.1... 0.5 > 0.5 2 > 2 25 Overpressure 3 bar 3 x FS ( 3 bar) 3 x

### 9700 Transmitter Submersible hydrostatic level transmitter

Specification sheet IP0078 October 2007 Level 9700 Transmitter Submersible hydrostatic level transmitter Description The 9700 series hydrostatic level transmitter is designed to perform in the most arduous

### Gas pressure regulator RSP 254 / RSP 255. Product information. Regulator R / R / R Actuator AS 254 / AS 255

Gas pressure regulator RSP 254 / RSP 255 Regulator R 70-10 / R 70-20 / R 70-100 Actuator AS 254 / AS 255 Product information Subject to modifications! Reprint prohibited! Table of Contents Application,

### HUMOR 20. High-precision Humidity Calibrator HUMOR 20. Operation

High-precision Humidity Calibrator The role of humidity calibrations that are accurate, reproducible, and documentable is becoming more and more important. ISO quality guidelines and regulations according

### Parametrable / Programmable Pressure Transmitter

Parametrable / Programmable Pressure Transmitter PTM/RS485 CUSTOMER BENEFITS High flexibility due to scalalbe pressure range Digital (RS485) and analogue (4-20mA) output signal in one sensor Available

### JUMO dtrans p30 Pressure Transmitter

609 Fulda, Germany Postal address: 605 Fulda, Germany Phone: +49 661 600-0 Fax: +49 661 600-607 Phone: +44 179 6 55 Data Sheet 40466 Page 1/6 JUMO dtrans p0 Pressure Transmitter General application Pressure

### Proportional pressure regulators VPPM

Key features LED indicators Control elements Display Plug socket with cable Venting at both ends Manifold block Sub-base valve Assembly repositionable by 180 In-line valve H-rail mounting Compressed air

### HON 219 Pressure Reducer (D119a)

Product information serving the gas industry worldwide Applications, characteristics, technical data Applications For industrial and process application Suitable for gases in accordance with DVGW Worksheet

### Pressure gauges Product range overview

Pressure gauges Pressure gauges Product range overview Type Pneumatic connection Nominal size Display unit Red/ Outer scale Inner scale green bar MPa psi bar MPa psi range Page/ Internet Pressure gauge

### E8AA. Pressure Sensor of Stainless Steel Construction Is Ideal for a Wide Range of Applications. Pressure Sensor (Stainless Steel Diaphragm)

Pressure Sensor (Stainless Steel Diaphragm) CSM DS_E_3_1 Pressure Sensor of Stainless Steel Construction Is Ideal for a Wide Range of Applications Incorporates double diaphragms consisting of SUS316L stainless

### Types ACE95 and ACE95Sr Tank Blanketing Valves

Types ACE95 and ACE95Sr Tank Blanketing Valves Bulletin 74.1:ACE95 May 2010 W9133 W8155 Figure 1. Type ACE95 Tank Blanketing Valve Figure 2. Type ACE95Sr Tank Blanketing Valve Features Fully Balanced Pilot

### The M-Series Eletta Flow Meter High accuracy DP Flow Meter with multiple functions

The M-Series Eletta Flow Meter High accuracy DP Flow Meter with multiple functions Flow Meter with multiple functions for gases and liquids M3 The M-series Flow Meter, with its versatile and user-friendly

### KMT. Thermal Mass Flowmeter. for compressed air and gases. Measuring range: Nm³/h Nm³/h

Thermal Mass Flowmeter for compressed air and gases measuring monitoring analysing KMT Measuring range: 0.32... 63 Nm³/h - 263.4... 263350 Nm³/h Accuracy: ± 1.5% of reading + 0.5% of full scale ( DN 50)

### Air service units series K G1/8, G1/4

Air service units series K Series FK Filter 12.011 Series RK Pressure regulator 12.012 Series FRK Filter/regulator 12.013 Series OK Lubricator 12.014 Series FROK Two piece air service unit 12.015 Series

### Relative pressure transmitter type 520

Relative pressure transmitter type 520 Pressure range -1... 9 bar / 0... 2.5 1000 bar The compact type 520 pressure transmitter is based upon the Huba Control developed thick film technology where the

### Relative and differential pressure module type 698

Relative and differential pressure module type 698-5... 5 mbar / 0... 1 10000 mbar The pressure modules type 698 are suitable for monitoring pressure and flow in air conditioning systems and in the laboratory

### Pressure regulator with solenoid valve VAD Air/gas ratio control with solenoid valve VAG Variable air/gas ratio control with solenoid valve VAV

Pressure regulator with solenoid valve Air/gas ratio control with solenoid valve Variable air/gas ratio control with solenoid valve VAV Product brochure GB 3 Edition 05.12 AGA All-purpose servo regulator

### PRO-50 Instrument Supply Regulator

Features CRN Approved The PRO-50 Regulator has been granted a Canadian Registration Number. Sour Service Capability Available in NACE configurations that comply with NACE MR0175/MR0103. Environmental limits

### Ambient Capacitance Gauge

Ambient Capacitance Gauge KJLC ACG Operating Manual Incl. EU Declaration of Conformity tkna57e1 (2017-03) 1 Product Identification In all communications with Kurt J. Lesker Company, please specify the

### Digital pressure gauge Model CPG500

Calibration technology Digital pressure gauge Model CPG500 WIKA data sheet CT 09.01 Applications Calibration service companies and service industry Measurement and control laboratories Quality assurance

### LGP. Application example. Pneumatic 2-Finger Parallel Gripper Universal Gripper. Sizes. Gripping force 26 N 1090 N. Weight 0.03 kg 1.

LGP Sizes 8 4 Weight.3 kg 1.6 kg 26 N 19 N Stroke per finger 2 mm 13 mm Workpiece weight.13 kg 4.2 kg Application example Pneumatic double transfer unit 2-Finger Parallel Gripper LGP Universal Rotary Actuator

### Expert Hydrostatic Level Transmitters

Expert Hydrostatic s General Features MJK Expert hydrostatic level transmitters are designed for level measurement by submerging the transmitter in open channels, drains and tanks. Expert hydrostatic level

### V248 Series 3-Way Pressure-Actuated. Water-Regulating Valves for High-Pressure

V248 Series 3-Way Pressure-Actuated Water-Regulating Valves for High-Pressure Refrigerants The V248 Series 3-Way Pressure-Actuated Water-Regulating Valves for High-Pressure Refrigerants regulate water

### Series INTELLIGENT PRESSURE- AND LEVEL TRANSMITTERS For all industries. Description ALL STAINLESS DESIGN

INTELLIGENT PRESSURE- AND LEVEL TRANSMITTERS For all industries Series 2000 ALL STAINLESS DESIGN EASY CALIBRATION WITHOUT TEST PRESSURE BY 3 PUSH BUTTONS ACCURACY 0,1% 4-20 ma AND HART PROTOCOL ATEX II

### Climatic Independent Level Sensor LAR

3 JAHRE GEWÄHRLEISTUNG SENSORS FOR FOOD AND BIOPHARMA. Product Information LAR-361 LAR-761 FOOD Climatic Independent Level Sensor LAR Application / Specified usage Hydrostatic level measurement in humid

### APG. Intrinsically Safe, Heavy Duty Pressure Transducer Series: PT-400

Intrinsically Safe, Heavy Duty Pressure Transducer Series: PT-400 C US The PT-400 offers high accuracy and reliability over a wide range of pressures. The small size, integrated electronics, wide operating

### Electrically Operated Pressure-Relief Cartridge, Size 10

Electrically Operated Pressure-Relief Cartridge, Size 1 Q max = 14 l/min (37 gpm), p max = bar (5 psi) seated pilot stage, spool-type design, with remote contral port Z Series WUVPOC-2, WUVPLC-2 1 Description

### SKP Series SKP25 U.. Pressure Regulating Gas Valve Actuator with Safety Shut-off Function

SKP Series SKP25 U.. Pressure Regulating Gas Valve Actuator with Safety Shut-off Function Technical Instructions Document No. 155-752 SKP25 U.. Description Only when assembled to Series VG Gas valves SKP25

### UNIK 5600/5700 Marine Certified Pressure Sensing Platform

GE Measurement & Control UNIK 5600/5700 Marine Certified Pressure Sensing Platform The new UNIK 5600/5700 carries marine certification for most zones on-board ship, as well as Intrinsically Safe certifications.

### Pneumatic dead-weight tester Model CPB3500

Calibration technology Pneumatic dead-weight tester Model CPB3500 WIKA data sheet CT 31.22 Applications Primary standard for calibrating the scale in a pneumatic range from -1... 120 bar / -14.5... 1,600

### Pressure switch, Differential pressure switch and Thermostat RT-E

Data sheet Pressure switch, Differential pressure switch and Thermostat RT-E The RT-E series consist of pressure and differential pressure switches as well as thermostats. The units are designed for industrial