1 Jennifer Hatfield FSPA Government Relations Consultant J. Hatfield & Associates, PL
2 Topics to cover: Pool & Spa Energy Code Requirements Residential Code Requirements Building (Public) Code Requirements Existing Pool & Spa Changes ADA requirements Misc. Code Requirements
3 How d we get here? State law requirement to provide pool and spa energy efficiency Florida Building Commission implemented state law with 2010 Code Went into effect March 15, 2012
4 Pool & spa energy efficiency requirements: FEEC, Section R403.9 for Residential, along with APSP-14 and APSP-15 FEEC, Section C404.7 for Commercial
5 Pipe Pump Setup Lower Energy Use
6 1 St APSP-5 Residential Pools 2 nd APSP-15 Energy Efficiency 3 rd APSP-7 Suction Safety
9 1 ½ hp two-speed 1 hp two-speed ¾ hp single-speed ½ hp single-speed No Yes Yes Yes NSPI-5 Select pump from database capable of gpm, or more, by using manufacturer s pump curves and calculated TDH from the project design specifications
10 1 St APSP-5 Residential Pools 2 nd APSP-15 Energy Efficiency 3 rd APSP-7 Suction Safety
12 Curve A 1 ½ hp two-speed 1 hp two-speed ¾ hp single-speed ½ hp single-speed No Yes Yes Yes Yes Yes APSP-15 Select any single-speed pump from database, or a multispeed with at least one flow listed for Curve A that is 36 gpm, or less.
13 1 St APSP-5 Residential Pools 2 nd APSP-15 Energy Efficiency 3 rd APSP-7 Suction Safety
15 1 ½ hp two-speed 1 hp two-speed ¾ hp single-speed ½ hp single-speed Maximum System Flow Rate APSP-7 The design points for APSP-5 and APSP-15 DO NOT APPLY to APSP-7. Use manufacturer s pump curve and calculated TDH.
16 Pool filtration pump can: Turnover pool in 12-hours or less Power to backwash filter Perform intended jobs Pipe sized so maximum design flow rate does not exceed: 8 feet-per-second in suction pipe 8 feet-per-second in return pipe
17 Pool filter pump sized for 6-to-12 hour* turnover Timer/controller Filtration pipe from pool-to-pump-to-pool 6 feet-per-second all suction pipe 8 feet-per-second all return pipe & backwash valve Filter Sized for 6-hour turnover, or maximum filtration/design flow rate, whichever is greater Cartridge (gpm/ft 2 ) Sand 15 (gpm/ft 2 ) Diatomaceous Earth 2 (gpm/ft 2 ) (*12 hour turnover for NSPI-5)
18 No drains, or VGB-2008 Suction Outlet fittings (drains) Select drains with flow ratings at or above the Maximum Operational/System Flow Rate of the pool and spa system Must assume all valves are open resulting in the lowest possible TDH for that pool or spa system Pipe size calculated and verified so maximum system (operational) flow rate does not exceed: 6 feet-per-second in dual-drain branch pipe 8 feet-per-second in main suction pipe
19 Pool gallons (to determine Curve A or C) Calculate filtration flow rate (pool gallons 360 minutes) Select pump from database any single-speed, or Multi-speed pump with Curve A or C listed flow rate <= calculated filtration flow rate
23 Applies only to Residential Pool Filtration Pumps & Pump Motors Does not regulate pumps used for other features, such as booster pumps for cleaners, waterfall pumps, etc. Only pumps that filter water for the main filter pump. Spa pumps are also not included Excludes auxiliary filters not used to maintain water quality, example: fountains, waterfalls
24 Per the Florida Code, the Residential Pool Pump & Motor provisions: Apply to all new construction Apply to existing construction IF code of job exceeds 30% of assessed value of pool structure
25 Prohibits split-phase, shaded-pole or capacitor start-induction run type pump motors. Requires pool pumps & pump motors with a total horsepower of 1HP or greater to have the capability of operating at two or more speeds.
26 Pool pump motor controls for use with a two-speed or greater pump shall have the capability of operating the pool pump at a minimum of two speeds.
27 Maximum filtration flow rate : Depending on the volume of the pool, the pool filtration flow rate shall not be greater than the rate needed to turn over the pool water volume in six hours or 36 gpm, whichever is greater. Per Addenda A, this does not apply to single speed pumps.
28 This means that for pools of less than 13,000 gallons the pump shall be sized to have a flow rate of 36 gpm or less and for pools of greater than 13,000 gallons, the pump shall be sized using the following equation: Maximum Filtration Flow Rate (gpm) = Pool Volume (gallons) / 360
29 Residential pool filtration pumps shall be selected from the CEC Appliance Efficiency Database for Residential Pool Pumps, or the APSP Appliance Efficiency Pool Pump Database. Either database can be used to verifying compliance.
30 For multi-speed and variable-speed filter pumps, at least one speed shall have the flow listed for Curve (A or C) that is less than the maximum filtration flow rate. Curve A = 17,000 gallons or less Curve C = greater than 17,000 gallons
31 Filter Sizing: Filters must have a minimum area based on the 6-hour turnover filtration flow rate (pool gallons / 360 minutes): Cartridge (gpm/ft 2 ) Sand 15 (gpm/ft 2 ) Diatomaceous Earth 2 (gpm/ft 2 )
32 When used, filter backwash valves must be 2 inches or the diameter of the return pipe, whichever is greater.
33 Pool piping and pipe fittings must be sized so that the velocity of the water at maximum filtration flow rate does not exceed 8 feet per second in the return line & 6 feet per second in the suction line. Pipe Size 1.5" 2" 2.5" 3" 3.5" 4" 5" 6" Nominal 6fps Nominal 8fps EXCEPTION: Pipe and fittings do not include equipment connections or internal equipment piping of, but not limited to, suction safety systems, pumps, heaters, and sanitizing devices.
34 For pool filtration pumps a length of straight pipe that is at least 4 pipe diameters shall be installed before the pump. At least 18 inches of horizontal or vertical pipe shall be installed between the filter and the heater or dedicated suction and return lines, or built-in or built-up connections shall be installed to allow for the future addition of solar heating equipment.
35 Directional inlet fittings are required. Sweep elbows encouraged, not required.
36 Applies to Commercial & Residential Applies to new & existing (heaters sold and installed must meet minimum requirements) Minimum federal standards for heat pumps (4.0 COP) and gas (82% - as of 4/16/13) Heat pumps must meet AHRI 1160 and have a test report from an independent laboratory Gas heaters must meet ANSI Z 21.56
37 Pool heaters fired by natural or LP gas shall not have continuously burning pilot lights. All pool heaters shall have a readily accessible on-off switch that is mounted on the outside of the heater and that allows shutting off the heater without adjusting the thermostat setting.
38 Time switches shall be installed to control pool heaters and pumps that can automatically turn the heaters and pumps off and on according to a preset schedule. Heaters, pumps and motors that have built in timers shall be deemed in compliance with this requirement. Exceptions: Where public health standards require 24-hour pump operation. Where pumps are required to operate solar- and waste-heat-recovery pool heating systems. Where pumps are powered exclusively from onsite renewable generation (Residential only).
39 Heated swimming pools and in-ground permanently installed spas shall be equipped with a vapor-retardant cover on or at the water surface or a liquid cover or other means proven to reduce heat loss. Exception: Outdoor pools deriving over 70 percent of the energy for heating from site-recovered energy (such as a heat pump) or solar energy source computed over an operating season.
40 403.9 FEEC requires that portable spas comply with ANSI/APSP-14. Portable Spa Manufacturers will need to ensure compliance with APSP-14. Ask for certification from the manufacturer.
41 Residential swimming pool provisions have always been found in two code books, the Residential Codebook and the Building Codebook. Chapter 41of Residential (will become Chapter 42 in the 2013 code) Chapter 4, Section of Building (will become Section in the 2013 code)
42 There have been no major changes in the residential pool requirements (besides energy) since the adoption of the ANSI/APSP- 7 Suction Entrapment Standard in the 2007 Code. There have been other standards where new editions are now referenced: APSP-4 (aboveground standard) APSP-5 (inground standard) APSP-6 (portable spa standard)
43 Major provisions found within the code other than in the APSP standards include: Barrier provisions has stayed the same except for updates to conform with/reference the most recent edition of the UL pool alarm standard. Pools in flood hazard areas: R Flood hazard areas. Pools installed in flood hazard areas established in Section R322 shall comply with Section R (A Zones) or R in coastal high-hazard areas (V Zones).
44 Public/Commercial swimming pool requirements have always been found in two places: Building Code, Chapter 4, Section (will become Section in the 2013 code) Chapter 64E-9, FAC the public pool rule developed by the Department of Health Per legislation passed in 2012, this rule is being changed to remove all construction provisions, to eliminate duplication with the code. What will remain is maintenance, safety and water quality provisions.
45 Changes to (454.1) have always coincided with any 64E-9 rule changes. A change addressing fixtures was made in The 2013 Code will provide a number of changes to ensure consistency or to make sure construction provisions that may be taken out of 64E-9 due to the 2012 law, will be found in the Building Code.
46 Required fixtures. A clarification was made to prevent adding the building fixture count to the pool fixture count, when determining the number of fixtures required for commercial swimming pools that only serve a designated group of dwelling units and that is not for use by the general public.
47 NEW Exception: When a public swimming pool meets all of the following conditions the following shall apply: 1. the pool serves only a designated group of dwelling units, 2. the pool is not for the use of the general public, and 3. a building provides sanitary facilities; the fixture requirement for the building shall be determined and if it exceeds the requirement in Table then the building requirement shall regulate the fixture count, otherwise the fixture count shall be based on the requirement for the pool. Under no circumstances shall the fixture counts be cumulative.
48 The 2013 Code will also make a few changes to what has been the current practice in the following areas: Obstructed decking allowance Doored access points from public rooms to the pool Min. height above surface of pool for river rides Alternative underwater lighting systems if manufacturer specifications provide equivalency. Rinse showers must be provided within fence. Elimination of DOH reference.
49 Section 613: Residential Swimming Pools & Spas -Provides that any pool or spa component or system undergoing alterations (not repair) comply with Chapter 41 of the Residential Code (the residential pool chapter).
50 Section Exceptions: Installation of pavers or coating to an existing pool or spa deck, Retiling a pool or spa, Re-plastering or re-lining a pool or spa, except the drain cover must comply with the 2007 ASME A Standard, Installation of a water filtration or sanitization component or system, Installation of an automation or a time switch component or system, and Installation of a heating component or system.
51 Section Specifically requiring pool or spa circulation systems or components undergoing alteration to comply with Section 6 of the ANSI/APSP-7 Suction Entrapment Avoidance Standard. With the 30% assessed value rule for pool pumps/motors AND the 2012 declaratory statement, section 613 has limited applicability.
52 The 2010 code put in new section 613 for existing pools and spas, but this section will be removed in the 2013 code.
53 The 2010 ADA Standards for Accessible Design, a federal regulation, applies to public entities & public accommodations (commercial facilities) The 2010 revision applies to both new & existing commercial pool and spa facilities As of January 31, 2013 means of access must be provided in all existing pool and spa facilities.
54 FL law, Chapter 553, F.S, and the 2012 Florida Accessibility Code for Building Construction requires compliance with ADA provisions and provisions are consistent for pools/spas except that Florida also requires private clubs to comply. Accessible Means of Entry to Pools & Spas: found in Sections 242 and 1009 of both the 2010 ADA Standards & the FL Accessibility Code
55 The 2012 FL Accessibility Code for Building Construction requires new commercial pools or spas to comply with 2010 federal ADA Standards (including private clubs) effective March 15, 2012 The FL Accessibility Code does not appear to address existing commercial pools and spas and the FL DOH will simply reference the 2010 ADAAG.
56 Regardless of state enforcement, compliance is required by the federal government. Complaint driven statute Private lawsuits Existing pools/spas are to be in compliance effective January 31, 2013 unless: There is a historical nature of the facility or Compliance is not readily achievable (hard argument to make in most pool/spa applications)
57 What are the permitted means of access? Pool lifts, sloped entries (ramps), transfer walls, transfer systems, or stairs. The criteria that each of these means of access must meet can be found in chapter 10, section 1009, of the revised ADA guidelines or FL Accessibility Code, a link can be found on the FSPA website. What type of means of access that must be used and how many means of access required, depend on the structure.
58 Larger pools (greater than 300 linear feet of pool wall) require at least two means of access and smaller pools (less than 300 linear feet of pool wall) require at least one means of access. When providing only one means of access, it must either be a pool lift or sloped entry (ramp).
59 Panic and fire exit hardware. An exception to panic hardware requirements found in Chapter 10 of the Building Code: allowing outdoor gates from residential and commercial swimming pools or pool decks to go without such devices unless the pool deck serves as a portion of the means of egress of a building or has an occupant load of 300 or greater.
60 Removal of the GFCI exemption for certain pumps. The NEC applies = all hardwired and plug-in pumps must have GFCI protection installed. As of 5/28/11 it is a violation of UL 1081 for UL Listed pool pump motors not to include the GFCI requirements within the installation instructions.
61 For energy efficiency information go to: For ADA information go to: ADA.html All Government Regulation information go to: ions/
COURSE SYLLABUS Provider: Program for Resource Efficient Communities University of Florida PO BOX 110940 Gainesville, FL 32611-0940 Provider #: 0001129 Course Name: Florida Building Code Advanced Training:
Mecklenburg County Health Ordinance Rules Governing Residential Swimming Pools Mecklenburg County Health Department 700 N. Tryon Street, Suite 211 Charlotte, North Carolina 28202-2236 Phone (704) 336-5103
KERN COUNTY PUBLIC HEALTH SERVICES DEPARTMENT ENVIRONMENTAL HEALTH DIVISION 2700 M Street, Suite 300 Bakersfield, CA 93301 Phone (661) 862-8740 Fax (661) 862-8701 POOL DATA PUBLIC SWIMMING POOL, SPA, WADING
SWIMMING POOL / SPA PLAN REVIEW CHECKLIST This checklist must be submitted with a Building Permit Application for any SWIMMING POOL or SPA. Job Information Property Address: Suite # Contractor: Residential
4-10-1: COMPLIANCE REQUIRED: Chapter 10 SWIMMING POOLS It shall be unlawful to construct, maintain, install or enlarge any swimming pool in the City except in compliance with the provisions of this Chapter.
SWIMMING POOL, SPA, & HOT TUB GUIDELINES A. Adopted construction codes and installation requirements 1. 2015 edition of the International Residential Code and Appendix Q, 2. 2014 edition of the National
FINAL EXPRESS TERMS FOR PROPOSED BUILDING STANDARDS OF THE CALIFORNIA DEPARTMENT OF PUBLIC HELATH REGARDING PROPOSED CHANGES TO THE CALIFORNIA BUILDING STANDARDS, ADMINISTRATIVE CODE CALIFORNIA CODE OF
PROVINCE OF QUEBEC TOWN OF HAMPSTEAD BY-LAW NUMBER 816 BY-LAW CONCERNING SWIMMING POOLS, HOT TUBS AND SPAS WHEREAS Notice of Motion of the present By-law was given at the Council Meeting held on July 6
Pool Submittal & Inspection Packet Submit all applications online at www.mckinneytexas.org/css Residential Pool Plans Submittal Requirements 1. Pool permits are applied for online at www.mckinneytexas.org/css.
Whitehall Township Swimming Pool, Spa and Hot Tub Code Guide THIS IS A GUIDE ONLY! YOU MUST COMPLY WITH ALL APPLICABLE PROVISIONS OF THE ADOPTED EDITION OF THE INTERNATIONAL RESIDENTIAL CODE (IRC). FOR
ARCHITECT GUIDELINES 1000 T Architect Guidelines for SwimEx Installation Model 1000T General Layout Call SwimEx at 800-877-7946 to receive AutoCad Drawings of the SwimEx Model that you will be installing.
POOL AND SPA REPLASTERING AND/OR REMODELING REQUIREMENTS Effective January 1, 2017 PLAN SUBMITTAL Any person proposing to renovate, replaster, reconstruct or alter a public pool or its ancillary facilities,
Jackson County Department of Public Health 538 Scotts Creek Rd. Suite 100 Sylva, NC 28779 Tel: 828-586-8994 FAX: 828-586-3493 Shelley Carraway DIRECTOR Jackson County Department of Public Health Application
Building Code Guidelines For Home Pools KEEP YOUR POOL SAFE Department of Inspections 17140 Monument Circle Suite 100 Isle of Wight, Virginia 23397 757-365-6213/6215 CODE REQUIREMENTS FOR SWIMMING POOLS
1 2 4 5 TITLE XIV POOL AND SPA SAFETY SEC. 01. SHORT TITLE. This title may be cited as the Virginia Graeme Baker Pool and Spa Safety Act. SEC. 02. FINDINGS. Congress finds the following: (1) Of injury-related
Residential Above-Ground and In-Ground Swimming Pool, Hot Tub and Spa Construction June 2017 A City of Rochester Hills Building Department Guide to Installing A Residential Swimming Pool, Hot Tub, or Spa
PLANNING, PROPERTY AND DEVELOPMENT DEPARTMENT Swimming Pools, Spas & Hot Tubs Construction requirements for outdoor private swimming pools (in-ground and above-ground), spas and hot tubs November December
Safety Instructions Important Information Please read prior to installation ATTENTION! ELECTRICAL HAZARD FOR INGROUND POOLS AND ABOVEGROUND POOLS Installation and Operating Manual IMPORTANT Pool Owner,
CONSTRUCTION PLAN APPROVAL PROCEDURE For Public Swimming Pools and Spas Corona 2275 S. Main St #204 Corona, CA 92882 (951) 273-9140 Fax (951) 520-8319 Hemet 800 S. Sanderson Ave #200 Hemet, CA 92545 (951)
Contents General 1 Health 2 Technology 3 Equipment 4 Chemistry 7 Commercial 8 General HOW MUCH DOES THE CLEAR COMFORT SYSTEM COST? The residential pool system is available for purchase, while the commercial
APPLYING VARIABLE SPEED PRESSURE LIMITING CONTROL DRIVER FIRE PUMPS SEC Project No. 1803007-000 November 20, 2006 TABLE OF CONTENTS I. ABSTRACT...1 II. INTRODUCTION...1 III. HISTORY...2 IV. VARIABLE SPEED
Planning and Building Department City of Mississauga 300 City Centre Drive, 3th Floor Mississauga ON L5B 3C1 PUBLIC POOL CHECKLIST (This checklist is based on the Ministry of Municipal Affairs and Housing
the strength behind the products you trust Pentair Pool Products / Paragon aquatics / Acu-Trol / Stark / Sta-Rite / Berkeley / Aurora Pentair Water Pool and Spa, the world s leading manufacturer of swimming
EasyTouch Pool and Spa Control Systems By Pentair Water Pool and Spa Because automation makes it all so simple EasyTouch Pool and Spa Control Systems Who says pool automation has to be costly and complicated?
S. T. Brady, CDR, Chief, Engineering Division References: a. Except as provided below, all vessels need to meet CFR 56.50-50 (bilge and ballast piping) and 56.50-55 (bilge pumps). b. Tankships (Subchapter
EN[Type text]vironmental HEALTH DEPARTMENT OF PUBLIC HEALTH Kathleen Grassi, R.D., M.P.H. Director Ron Rowe, R.E.H.S., M.P.A. Environmental Health Director ENVIRONMENTAL HEALTH DIVISION POOL SAFETY 2017
JAN 2018 Swimming Pool Construction Guidelines Building Inspections Staff Eddie Wilson, CBO Building Official 817-503-1057 email@example.com Kelly Minor Permit Technician 817-503-1031 firstname.lastname@example.org
PREFACE The growing popularity of home swimming and related activities has led to an increase in the number of swimming pools, spas, hot tubs and hydromassage bathtubs in use. Each of these products has
Design Manual Chapter 4 - Water Mains 4C - Facility Design 4C-1 Facility Design A. General Water mains and appurtenances, including hydrants and valves, should be provided along all streets including connections
RESIDENTIAL POOL, SPA AND HOT TUB PERMIT REQUIREMENTS The following guidelines are intended to assist with the permit acquisition process with regards to Pool, Spa and Hot Tub installation. Not all information,
December 6, 2010 Foam 14a 1. The Viking Low Flow Foam/Water proportioning system, is a UL Listed and FM Approved system, for use with Viking supplied foam concentrates. This system consists of a standard
Pool fencing guidelines Interpreting swimming pool fence requirements Third edition March 2008 Further information For more specific information about pool fencing requirements, contact your local council
ANSI / ISEA Z358.1-2014 Compliance Checklist INTRODUCTION The selection of emergency eyewash and shower equipment is often a complicated process. In addition to addressing design and engineering issues,
Table of Contents Purpose... 2 Commencement... 2 Application... 2 Referral Agency... 2 Compliance with the QDC... 2 Relationship between the Standard and this part... 2 Associated Requirements... 2 Referenced
For In-ground and Aboveground Pools Vessel Installation and Operating Manual Important Safety Information Please read this manual prior to installation. Nature 2 Express is designed to sanitize in-ground
DENVILLE DIVISION OF HEALTH 1 St. Mary s Place Information Denville, NJ 07834 (973) 625 8300, Ext. 260 Public Recreational Bathing Definitions: Public Recreational Bathing Place: Any bathing beach, hot
1 1 1 1 1 1 1 1 0 1 Title DEPARTMENT OF HEALTH AND MENTAL HYGIENE Subtitle 1 [SWIMMING POOLS AND SPAS] AQUATIC FACILITIES AND VENUES Chapter 01 [Public Swimming Pools and Spas] Aquatic Facilities and Venues
RESIDENTIAL SWIMMING POOLS INFORMATION CHECKLIST POOL PERMIT APPLICATION FORM MUST BE COMPLETED IN FULL COPY OF CONTRACT OR PURCHASE ORDER SUBMIT (4) FOUR SETS OF SIGNED AND SEALED PLANS BY A FLORIDA LICENSED
RECOMMENDED RULES FOR SIZING THE WATER SUPPLY SYSTEM Because of the variable conditions encountered, it is impractical to lay down definite detailed rules of procedure for determining the sizes of water
References: a. 46 CFR Part 54 Pressure Vessels S. T. Brady, CDR, Chief, Engineering Division b. ASME Boiler and Pressure Vessel Code (BPVC), Section VIII, Division 1, (1998 Edition) c. Navigation and Inspection
The optimal functioning of the Control valve not only exists of sufficient body & seat tightness, but more important, the total "performance" of the valve and its controls! For an accurate and reliable
RECOMMENDED RULES FOR SIZING THE WATER SUPPLY SYSTEMS Because of the variable conditions encountered, it is impractical to lay down definite detailed rules of procedure for determining the sizes of water
Dry 131h 1. DESCRIPTION The Viking Model G-1 Maintenance Air Compressor is an electric motor-driven, aircooled, single-stage, oil-less compressor. The unit is equipped with a check valve and provides a
SWIMMING POOL PERMITS ARE ABOUT HEALTH AND SAFETY Swimming Pool Booklet Washington County, Maryland Published 2004 Revised 03/10/05 Revised 02/10/06 Department of Permits & Inspections 80 West Baltimore
Procedure Number: H2 Revision Date: 10/07/2014 K. B. FERRIE, CDR, Chief, Hull Division Purpose The purpose of this Plan Review Guideline is to provide the submitter with general guidance and information
Air Amplifiers & SYSTEMS We Accept VISA, MasterCard and American Express Air Amplifiers Point-of-Use Air Solutions Maximator air amplifiers are designed to boost plant air pressure or increase the supply
C. J. Robuck, LCDR, Chief, Engineering Division References a. Title 46 CFR 34.15 (Subchapter D) b. Title 46 CFR 76.15 (Subchapter H) c. Title 46 CFR 95.15 (Subchapter I) d. Title 46 CFR 108.431 (Subchapter
SIZING AND CAPACITIES OF GAS PIPING A.1 General piping considerations. The first goal of determining the pipe sizing for a fuel gas piping system is to make sure that there is sufficient gas pressure at
DATA SHEET Horizontal Bladder Tanks Features UL Listed and FM Approved for use with various ANSUL proportioners and foam concentrates 175 psi (12.1 bar) maximum allowable working pressure (design pressure)
my SYSTEM A guide to common applications in water distribution systems WWW.SINGERVALVE.COM INDEX This short guide is intended to offer guidance on some of the common problems, applications and questions
DATA SHEET Vertical Bladder Tanks Features UL Listed and FM Approved for use with various ANSUL proportioners and foam concentrates 175 psi (12.1 bar) maximum allowable working pressure (design pressure)
CIF A Tyco International Company 1 Foam Concentrate CIF 3% AFFF -UL Listed -UL Canada Listed 6% AFFF 6 parts AFFF concentrate to 94 parts water -UL Listed- Foam Liquid -UL Canada Listed 3% FLUOROPROTEIN
Cristal -Flo II Filter OwnerÕs Manual IMPORTANT SAFETY INSTRUCTIONS READ AND FOLLOW ALL INSTRUCTIONS SAVE THESE INSTRUCTIONS Table of Contents SECTION I. How Your Filter Works...3 SECTION II. Installation...4,
ETV Platinum Plus R C O R P O R A T I O N Electronic Tempering Valve DOMESTIC HOT WATER TEMPERATURE CONTROL with SAFEGUARD Conforms to the following: ASSE 1017 California Lead Free Plumbing Law CSA B 125.3
N E T A F I M U S A Pressure Compensating (PC) Spray Stakes Automated Watering Systems for Large Container Production Improve Plant Quality and Conserve Resources 1 or More Good Reasons to Choose Netafim
SEP 100 D.E. SEPARATION TANK INSTALLATION AND USER S GUIDE IMPORTANT SAFETY INSTRUCTIONS READ AND FOLLOW ALL INSTRUCTIONS SAVE THESE INSTRUCTIONS ii CUSTOMER SERVICE / TECHNICAL SUPPORT If you have questions
Set Up Instructions for DRS4 Series Single Tank Inspect the packaging of the equipment to confirm that nothing was damaged during shipping. (Figure 1) Remove the resin tank(s) and valve(s) from the packaging.
Installation Instructions BGA Series Issue Date October 3, 2017 BGA158, BGA171 and BGA110 Series Shutoff Gas Valve Applications The BGA Series shutoff gas valve is an electrically operated gas valve that
3 GALLON, OILLESS PANCAKE COMPRESSOR INSTRUCTIONS Item #31289 The EASTWOOD 3 GALLON, OILLESS PANCAKE COMPRESSOR, with an Integral Air Regulator, efficiently supplies all compressed air requirements for
Emergency Shower & Eyewash Training Guide No matter how many precautions employees take, accidents sometimes happen. In these situations quick action is essential, and if the incident involves a hazardous
ICC-ES Report ESR-3868 Reissued 10/10/2017 This report is subject to renewal 05/2018 EVALUATION SUBJECT: FIBERGLASS ONE-PIECE SWIMMING POOL SHELLS DIVISION: 13 00 00 SPECIAL CONSTRUCTION SECTION: 13 11
GEN-1e CO2 Generator Custom Automated Products offers economical and safe carbon dioxide generators. They produce CO2 by burning either propane or natural gas. We have designed our CO2 generator to allow
3119-600 Series Environmental Chambers Challenges in Non-Ambient Testing Testing at non-ambient temperatures adds another layer of challenges to your testing laboratory. Ensuring you get accurate and stable
1 2 3 The enthalpy of saturated vapor and the enthalpy of saturated liquid is evaluated at the fully accumulated relief device set pressure (P=P set * 1.1 + 14.7). Set Pressure (psig) h fg (Btu/lbm) 150
Operations: HSE Health and Industrial Hygiene Laboratory Safe Work Practice Page 2 of 8 AMENDMENT RECORD Amendment Date Revision Number Revision Number 08/11/2016 4 Authority: Health Manager Custodian:
B A C K Y A R D P L A N N I N G G U I D E Step-by-Step Planning Guide Whether you are considering purchasing a Michael Phelps Signature Swim Spa by Master Spas, or can t wait for yours to be delivered,
ADA & Public Rights of Way Overview of Current and Up-coming Requirements FDOT Design Training Expo 2012 Orlando, FL Dean Perkins, RA - ADA Coordinator Florida Department of Transportation Office of Design,
Installation Instructions BGA158 Issue Date August 24, 2011 BGA158 Series CE Approved Class A Shutoff Gas Valve Applications The BGA158 Series shutoff gas valve is an electrically operated gas valve that
Design Requirements for Eyewash and Safety Shower Units Application: Eyewash Stations must be provided in the following areas. Laboratories Plumbed emergency eyewash equipment shall be installed in every
SECTION 25 TESTING AND DISINFECTING WATER MAINS 25-1.01 Scope 25-1 General This section describes the requirements for pressure and leak testing, and disinfecting of water mains and appurtenances, including
TROUBLESHOOTING GUIDELINES PROBLEM: Performance 1. The most common problem in this area comes from inadequate flow to the LAKOS Separator(s). All LAKOS Separators operate within a prescribed flow range
CATALINA SWIM SPAS OLYMPIC 400 SERIES DEALER PRICE LIST 11/1/2015-11/1/2016 12.6 REGATTA MODEL DESCRIPTION ELEC PUMPS DIMENSIONS PRICE C400-Bronze 12.6 Portable BP3 (1) 5 HP & (2) 4 HP Pumps 90 x 151 x
SAVE THESE INSTRUCTIONS Pentair Pool Products P/N 99223000 12 Rev. E 2-22-02 Sand Dollar Filter Owner s Manual IMPORTANT SAFETY INSTRUCTIONS READ AND FOLLOW ALL INSTRUCTIONS SAVE THESE INSTRUCTIONS Table
Hoffman Specialty Regulators Regulators Pressure and/or Temperature Operated Regulators Series 2000 The Hoffman Specialty Series 2000 consists of main valves, pilot valves, wells and hardware kits. They
Installation Instructions Issue Date September 17, 2008 G92 Series BASOTROL Automatic Pilot Gas Valve Installation IMPORTANT: Only qualified personnel should install or service BASO Gas Products. These
Jacuzzi J-SS40 Salt System Installation and Operating Instructions IMPORTANT SAFETY INSTRUCTIONS WARNING: Before installing this product. Read and follow all warning notices and instructions accompanying
Disclaimer: NARHA recommends that you obtain a copy of the ADAAG as well as accessibility regulations set by your state before you design, construct or alter your facility. Mounting Ramps The necessity
Your consent to our cookies if you continue to use this website.