# FUME CUPBOARD PERFORMANCE CHECK

Save this PDF as:

Size: px
Start display at page:

## Transcription

1 WS2 FUME CUPBOARD PERFORMANCE CHECK This exercise is adapted from Appendices E & F of Australian Standard Safety in laboratories: Fume cupboards. 1. PURPOSE This exercise determines how well a fume cupboard is meeting Australian Standard specifications. 2. SUMMARY The face velocity of air through the cupboard window is measured with a vane anemometer, while the presence of turbulence is checked using a Dragar smoke tube. The three operational requirements to be tested are: an average face velocity of m/s for the fully opened window, with a maximum variation of 20% from average a minimum turnover of 5 cupboard volumes per minute no turbulence causing air to escape into the laboratory 3. REAGENTS & EQUIPMENT 3.1 Tape measure 3.2 Dragar smoke tube 3.3 Vane anemometer 4. PROCEDURE 4A. Face velocity measurements 4.1 Turn the fume cupboard on and allow one minute to stabilise. 4.2 Lift the window to fully opened. 4.3 Measure the dimensions of the opening. 4.4 Measure the face velocity at each point shown on the Results Sheet. The anemometer will take around 15 seconds to read correctly, and will fluctuate, so take an average reading over 10 seconds. 4B. Volumetric capacity 4.5 Measure the internal dimensions of the fume cupboard. Assume it is a regular shape do not attempt to compensate for small gaps/ledges etc. 4.6 Lower the window to fully closed. 4.7 Measure the dimensions of the opening. 4.8 Measure the face velocity at each point shown on the Results Sheet. 4C. Smoke test Record all results as in the table below. Good Satisfactory Dangerous Smoke travels straight to exhaust without reverse flows or eddies Reverse flows or eddies may be present but not to the extent that smoke escapes from the fume cupboard Reverse flows or eddies can escape from the fume cupboard

2 4.9 Lift the window to fully opened Release smoke around the perimeter of the opening Release smoke along the floor of the fume cupboard, starting at the front Release smoke around the internal walls Release smoke near any items in the fume cupboard Lower the window to half-way Release smoke around the perimeter of the opening Lower the window to fully closed Release smoke around the perimeter of the opening. 4D. Location of fume cupboards 4.18 Check the siting of the fume cupboard, based on the requirements of AS Section 4.1, excerpted in Appendix REQUIREMENTS Complete the Results Sheet provided. 6. REPORT Calculations 4A. Face velocity measurements calculate the average face velocity for the seven measurements with window fully open calculate the maximum variation in the individual measurements from the average 4B. Volumetric capacity calculate the area of the opening with the window fully open calculate the area of the opening with the window closed to minimum calculate the average face velocity based on the three measurements made with the window closed to minimum calculate the volumetric capacity (in m 3 /min) with the window fully open and fully closed calculate the internal volume of the fume cupboard calculate the number of cupboard air volume changes per minute fully open and fully closed Question Are the operating requirements met? Tabulate the results, requirements and a PASS/FAIL for each. WS2.2

3 WS2. Fume Cupboard Performance Check RESULTS SHEET Location of fume cupboard Serial or identification number Date tested Items in fume cupboard when tested 4a. Face velocity Window fully open Height Width WS2.3

4 4B. Volumetric capacity Internal dimensions of fume cupboard Height (m) Width (m) Depth (m) Window fully closed Height 4C. Smoke test Fully open Floor Walls Around items Half open Closed WS2.4

5 4D. Location of fume cupboards AS Section 4.1 Clause Satisfactory (Y/N)? Height of working surface Traffic routes Opposing bench tops Opposing walls Other fume cupboards Architectural obstacles Comments WS2.5

### Statesville, NC. Results of AM ASHRAE 110 Laboratory Fume Hood Performance Evaluations Venturi Hood

Statesville, NC Results of AM ASHRAE 11 Laboratory Fume Hood Performance Evaluations Venturi Hood January, 217 Prepared By: Exposure Control Technologies Inc. 231-C East Johnson Street Cary, NC 27513 Phone:

### "LABORATORY SAFETY SERIES"

PRESENTER'S GUIDE "LABORATORY HOODS" Part of the "LABORATORY SAFETY SERIES" Quality Safety and Health Products, for Today...and Tomorrow OUTLINE OF MAJOR PROGRAM POINTS OUTLINE OF MAJOR PROGRAM POINTS

### IH Report: SUFMO 08/09-CC21 1/27/2009 Stanford University Gas Cabinet Installation and Performance Criteria

Stanford University Gas Cabinet Installation and Performance Criteria I. Application Gas cabinets are ventilated enclosures that are used to isolate hazardous gas cylinders from the surrounding work place.

Schools Badminton LESSON PLANS Learn to Win Schools Badminton LESSON PLANS Learn to Win Badminton World Federation 2011. First published November 2011. Overview 1. Introduction Learn to Win Before starting

### Customer Responsibilities

Thank you for purchasing an Agilent instrument. To get you started and to assure a successful and timely installation, please refer to this specification or set of requirements. Correct site preparation

### Module 15 : Grit Chamber. Lecture 20 : Grit Chamber

1 P age Module 15 : Grit Chamber Lecture 20 : Grit Chamber 2 P age 15.6 Square Grit Chamber The horizontal flow rectangular grit chamber faces the problem of sedimentation of organic matter along with

### ARCA Guidance Note. Guidance on Air Management in Asbestos Enclosures

Guidance on Air Management in Asbestos Enclosures 1 GUIDANCE ON AIR MANAGEMENT IN ASBESTOS ENCLOSURES 1. BACKGROUND 1.1 This guidance note is intended to clarify expectations with regard to air management,

### Appendix FRANCE Lyon Croix-Rousse Tunnel

Appendix 2.9 - FRANCE Lyon Croix-Rousse Tunnel 1. SUMMARY A NEW MULTIMODAL TUNNEL The Croix-Rousse tunnel is located in Lyons (France). The City of Lyons has about 475.000 inhabitants with 1,31 million

### Design a grit chamber for population with water consumption of 135 LPCD.

1 Example:1 Design a grit chamber for population 50000 with water consumption of 135 LPCD. Solution Average quantity of sewage, considering sewage generation 80% of water supply, is = 135 x 50000 x 0.8

### WIND LOADS / MOORING & FISH TAILING. Arjen Koop, Senior Project Manager Offshore Rogier Eggers, Project Manager Ships

WIND LOADS / MOORING & FISH TAILING Arjen Koop, Senior Project Manager Offshore Rogier Eggers, Project Manager Ships OVERVIEW Wind Loads Wind shielding Fish tailing? 2 WIND LOADS FOR OFFSHORE MARS TLP

### Outside Air Nonresidential HVAC Stakeholder Meeting #2 California Statewide Utility Codes and Standards Program

1 Outside Air Nonresidential HVAC Stakeholder Meeting #2 California Statewide Utility Codes and Standards Program Jim Meacham, CTG Energetics Agenda 2 In Situ Testing Results Reduced Ventilation after

### FINAL REPORT. Wind Assessment for: NEW OFFICE BUILDING AT ESSENDON FIELDS Essendon, Victoria, Australia

FINAL REPORT Wind Assessment for: NEW OFFICE BUILDING AT ESSENDON FIELDS Essendon, Victoria, Australia Prepared for: Essendon Fields Pty Ltd Essendon Fields House Level 2, 7 English Street Essendon Fields

### PUBLIC SPA CHECKLIST. Planning and Building Department City of Mississauga 300 City Centre Drive, 3th Floor Mississauga ON L5B 3C1

Planning and Building Department City of Mississauga 300 City Centre Drive, 3th Floor Mississauga ON L5B 3C1 PUBLIC SPA CHECKLIST This checklist is prepared for purposes of convenience only. For accurate

### Core Velocity 3.0. Different Ways To Connect & Setup The Core Velocity Belt The Safest and Most Effective Way Possible.

Core Velocity 3.0 Different Ways To Connect & Setup The Core Velocity Belt The Safest and Most Effective Way Possible. Criss Cross Ideally the Criss Cross setup is designed for stationary exercises inside

### Permit-To-Work Guidance and Templates

Managing Contractors Policy - Appendix E Permit-To-Work Guidance and Templates This document has been constructed to provide guidance in how to use a permit to work correctly. The first part explains the

### CHAPTER 1 STANDARD PRACTICES

CHAPTER 1 STANDARD PRACTICES OBJECTIVES 1) Functions and Limitations 2) Standardization of Application 3) Materials 4) Colors 5) Widths and Patterns of Longitudinal Pavement Marking Lines 6) General Principles

### Purge Star & Ring Purge Systems

March 2013 Operator s Manual Purge Star & Ring Purge Systems Additional instruction for Purge Star Single Hose, Purge Star Double (bypass) Hose and Ring Purge with bypass hose and gas dump valve feature.

### Wind Flow Validation Summary

IBHS Research Center Validation of Wind Capabilities The Insurance Institute for Business & Home Safety (IBHS) Research Center full-scale test facility provides opportunities to simulate natural wind conditions

### PROCESS CONTROL HANDBOOK Z-6

Reversal Bath This step prepares the film for the color-developer step. In the reversal bath, a chemical reversal agent is absorbed into the emulsion. No chemical reaction takes place until the film enters

### Wind tunnel tests of a non-typical stadium roof

Wind tunnel tests of a non-typical stadium roof G. Bosak 1, A. Flaga 1, R. Kłaput 1 and Ł. Flaga 1 1 Wind Engineering Laboratory, Cracow University of Technology, 31-864 Cracow, Poland. liwpk@windlab.pl

### OPTIMISATION OF VENTILATION IN THE CASE OF A FIRE IN ROAD TUNNELS

- 51 - OPTIMISATION OF VENTILATION IN THE CASE OF A FIRE IN ROAD TUNNELS ABSTRACT Stosch R. 1, Wehner M. 1, Brandt R. 2 HBI HAERTER AG, Tunnel Ventilation Heidenheim 1, D and Zurich 2, CH The control of

### Netball. Developing the Right Sports Hall. Sports Data Sheets

Introduction The following sports data sheets are for use in conjunction with Sport England s Developing the Right Sports Hall (DRSH) main document. They relate to Step 5 Establishing the Project Brief

### Figure 1. Outer dimensions of the model trucks.

1 Standardisation of test method for salt spreader: Air flow experiments Report 3: Simulations of airflow patterns by Jan S. Strøm, Consultant Aarhus University, Engineering Centre Bygholm, Test and Development

### Laboratory Test Results Fire Safety Conveyor Belts

Laboratory Test Results Fire Safety Conveyor Belts ALEXANDRU MARIAN PULBERE* Inspectorate for Emergency Situations Tara Barsei Brasov county, 11 Mihai Viteazul Str., Brasov, Romania Testing of fire safety

### EXPERIMENTAL STUDY OF WIND PRESSURES ON IRREGULAR- PLAN SHAPE BUILDINGS

BBAA VI International Colloquium on: Bluff Bodies Aerodynamics & Applications Milano, Italy, July, 2-24 8 EXPERIMENTAL STUDY OF WIND PRESSURES ON IRREGULAR- PLAN SHAPE BUILDINGS J. A. Amin and A. K. Ahuja

### THE WAY THE VENTURI AND ORIFICES WORK

Manual M000 rev0 03/00 THE WAY THE VENTURI AND ORIFICES WORK CHAPTER All industrial combustion systems are made up of 3 main parts: ) The mixer which mixes fuel gas with combustion air in the correct ratio

### LINE FOLLOWING ENHANCED RULES. Allar Aasjõe

LINE FOLLOWING ENHANCED RULES Allar Aasjõe +372 5346 7363 allar.aasjoe@robotex.ee Content 1 Introduction... 3 2 The field... 3 3 The Robot... 3 4 The Competition... 4 5 Obstacles... 4 5.1 Line break...

### Forced or Mechanical Ventilation - which uses mechanical supply and/or extraction to provide fresh air and is controllable.

CITY AND COUNTY OF CARDIFF CODE OF GUIDANCE WORKPLACE VENTILATION All places where people work, be it an office, workshop, school, leisure centre, laboratory, home for the elderly, etc. need to provide

### Applied Biosystems 3400 DNA Synthesizer

Applied Biosystems 3400 DNA Synthesizer Site Preparation and Safety Guide April 3, 2003 2:09 pm, SPG_00_Title.fm Copyright 2003, Applied Biosystems. All rights reserved. For Research Use Only. Not for

### PROBLEMS ON VENTILATION IN COMPLEX CITY TUNNELS

- 15 - PROBLEMS ON VENTILATION IN COMPLEX CITY TUNNELS Sturm P.J. 1, Bacher M. 1, Pretterhofer G. 1 Kalz U., Maier J. 3 1 Graz University of Technology, Austria ASFiNAG Service Gesellschaft Nord; 3 Amt

### Validation of a Neutral Pressure Isolation Room

Validation of a Neutral Pressure Isolation Room Andrew Fletcher, William Booth and Blanca Beato Arribas BSRIA Ltd., UK Corresponding email: Andrew.Fletcher@bsria.co.uk SUMMARY The principles behind a new

### Gait Analyser. Description of Walking Performance

Gait Analyser Description of Walking Performance This brochure will help you to understand clearly the parameters described in the report of the Gait Analyser, provide you with tips to implement the walking

### Fire and Safety for Offshore drilling and production Ajey Walavalkar ANSYS Inc.

Fire and Safety for Offshore drilling and production Ajey Walavalkar ANSYS Inc. 1 ANSYS, Inc. September 12, Fire and safety related applications Gas Dispersion and Ventilation Formation of combustible

### Experiment 8: Minor Losses

Experiment 8: Minor Losses Purpose: To determine the loss factors for flow through a range of pipe fittings including bends, a contraction, an enlargement and a gate-valve. Introduction: Energy losses

### Appendix ITALY Valsassina Tunnel near Lecco (Lombardy)

Appendix 2.12 - ITALY Valsassina Tunnel near Lecco (Lombardy) 1. SUMMARY The Valsassina tunnel is located along the National Road 36 (SS36), from Milan towards Valsassina in the town of Lecco with about

### Gas flow calibrations performed at the National Metrology Institute of South Africa (NMISA)

Int. J. Metrol. Qual. Eng. 5, 303 (2014) c EDP Sciences 2014 DOI: 10.1051/ijmqe/2014012 Gas flow calibrations performed at the National Metrology Institute of South Africa (NMISA) D. Jonker and E.P. Tarnow

### BUCKET WHEEL RECLAIMERS. AUTHOR: MR. W KNAPPE MAN TAKRAF Fördertechnik GmbH

BUCKET WHEEL RECLAIMERS AUTHOR: MR. W KNAPPE MAN TAKRAF Fördertechnik GmbH Performance of Bucket Wheel Reclaimers (Method of Calculation in Principle) A: Introduction The objective of the following is

### Thermalling for Dummies. John J. Scott

Thermalling for Dummies John J. Scott Finding Thermals Where to Look: Remember how thermals develop. The suns UV rays heat the ground by radiation absorption and the ground then heats the air by convection.

### rpbsafety.com Samoset Rd Royal Oak, MI USA OF THE NOVA 3 ABRASIVE BLASTING SUPPLIED AIR RESPIRATOR

rpbsafety.com 1 866 494 4599 2807 Samoset Rd Royal Oak, MI 48073 USA OF THE NOVA 3 ABRASIVE BLASTING SUPPLIED AIR RESPIRATOR OBJECTIVE The objective of this study was to verify that the NOVA 3 Abrasive

### Advanced Code Requirements for Residential Construction Internet Course

Course Syllabus: Course Title: Number of Classroom Hours: Method of Presentation: Intended Target Group: Advanced Code Requirements for Residential Construction Internet Course 1; 1 CEU Online Course Florida

### 3-Person Officiating System for Basketball

3-Person Officiating System for Basketball By: Cody Poder, English 202C Throughout the many levels of basketball that are played throughout the world, the officiating is scrutinized much more than any

### Measurement LESSON ONE - Metric and Imperial Lesson Notes

0 1 2 Measurement Introduction Introduction to Measurement a) Complete the following table: Unit Length Multiplying (in metres) Factor Referent mm cm dm m dam hm km b) Indicate which measuring tool is

### Layout Guidelines. Overview

TECHNICA RESOURCES ayout Guidelines Included are the design layout guidelines for evaporative cooling products in several situations typically encountered by designers. These guidelines represent minimum

### Lab 3 Introduction to Quantitative Analysis: Pumps and Measurements of Flow

Georgia Institute of Technology School of Earth and Atmospheric Sciences EAS 4641, Spring 2008 Lab 3 Introduction to Quantitative Analysis: Pumps and Measurements of Flow Purpose of Lab 3: 1) To gain a

### AIRFLOW AROUND CONIC TENSILE MEMBRANE STRUCTURES

AIRFLOW AROUND CONIC TENSILE MEMBRANE STRUCTURES A. M. ElNokaly 1, J. C. Chilton 2 and R. Wilson 1 1 School of the Built Environment, University of Nottingham, Nottingham, NG7 2RD, UK 2 School of Architecture,

### Advanced Test Equipment Rentals ATEC (2832)

Established 1981 Advanced Test Equipment Rentals www.atecorp.com 800-404-ATEC (2832) DOCUMENT NO: STP 2203 VERSION: 2008-07-01 Page 1 of 6 1.0 PURPOSE This test procedure is used by the Electrical Safety

### INTERNATIONAL IKA FORMULA KITE CLASS RULES 2017

INTERNATIONAL IKA FORMULA KITE CLASS RULES 2017 The IKA Formula Kite Class was adopted as an World Sailing international class in 2013 INDEX IKA FORMULA KITE COURSE RACING COMPETITIONS PART I ADMINISTRATION

### Effects of seam and surface texture on tennis balls aerodynamics

Available online at www.sciencedirect.com Procedia Engineering 34 (2012 ) 140 145 9 th Conference of the International Sports Engineering Association (ISEA) Effects of seam and surface texture on tennis

Adaptations of Desert Plants Topic The shape and surface area of a leaf are related to its ability to gain and release water. Introduction Deserts are biomes that present great difficulties to their inhabitants.

### Occupational Health & Safety

Personal Development Level 3 Occupational Health & Safety Any injury particularly workplace injury is a major cause of concern for all involved in Occupational Health and Safety (OHS). The factors which

### POOL AND SPA REPLASTERING AND/OR REMODELING REQUIREMENTS

POOL AND SPA REPLASTERING AND/OR REMODELING REQUIREMENTS Effective January 1, 2017 PLAN SUBMITTAL Any person proposing to renovate, replaster, reconstruct or alter a public pool or its ancillary facilities,

### Swimming pool barriers. Schedule 1 - Modifications to the Standard... 5 MP 3.4 SWIMMING POOL BARRIERS. Table of Contents

Table of Contents Purpose... 2 Commencement... 2 Application... 2 Referral Agency... 2 Compliance with the QDC... 2 Relationship between the Standard and this part... 2 Associated Requirements... 2 Referenced

### Aerodrome Design Manual

Doc 9157 AN/901 Aerodrome Design Manual Part 4 Visual Aids Approved by the Secretary General and published under his authority Fourth Edition 2004 International Civil Aviation Organization 8-12 Aerodrome

### PHYS 101 Previous Exam Problems

PHYS 101 Previous Exam Problems CHAPTER 14 Fluids Fluids at rest pressure vs. depth Pascal s principle Archimedes s principle Buoynat forces Fluids in motion: Continuity & Bernoulli equations 1. How deep

### Measuring range Δp (span = 100%) Pa

4.4/ RLE 5: Volume-flow controller, continuous How energy efficiency is improved Enables demand-led volume flow control for the optimisation of energy consumption in ventilation systems. Areas of application

### Ionising Radiations Code of Practice & Guidance Contingency Arrangements

Ionising Radiations Code of Practice & Guidance Contingency Arrangements Where any radiation user uses a source of ionising radiations, which may for example include working with sealed (closed) sources,

### Lecture 10 : Sewer Appurtenances

1 P age Module 8 : Sewer Appurtenances Lecture 10 : Sewer Appurtenances 2 P age The structures, which are constructed at suitable intervals along the sewerage system to help its efficient operation and

### Mechanical Wind Recorder

THE WORLD OF WEATHER DATA - THE WORLD OF WEATHER DATA - THE WORLD OF WEATHER DATA Instruction for Use 021186/11/06 Mechanical Wind Recorder 4.3900.20.000 ADOLF THIES GmbH & Co. KG Hauptstraße 76 37083

### Vickers. Flow Controls. Flow Controls FN, F(C)G, FRG. Released 6/94

Vickers Flow Controls Flow Controls FN, F(C)G, FRG Released 6/94 685 Table of Contents FN03/06/10 Model Series Application Data...............................................................................

### The Effect of Von Karman Vortex Street on Building Ventilation

The Effect of Von Karman Vortex Street on Building Ventilation P.Praveen Kumar Abstract This paper deals with the utilisation of the von Karman vortex street principle to maximise air flow into buildings.

### Mine Foreman Training Ventilation Unit 7 Part 2 Ventilating A Mine. Program developed by Wayne Collett Office of Mine Safety & Licensing 2006

Mine Foreman Training Ventilation Unit 7 Part 2 Ventilating A Mine Program developed by Wayne Collett Office of Mine Safety & Licensing 2006 1 The purpose of mine ventilation is to provide a safe and productive

### Annex B: Range Specification Requirements

Annex B: Range Specification Requirements The following Range Specification Requirements are issued and relate to the requirements for the approval of firearm ranges and galleries to be operated in Tasmania:

### The primary purpose of laboratory fume hoods is to keep toxic or irritating vapors out of the general laboratory working area.

Introduction Welcome to the Biosafety Cabinets and Fume Hoods Training Course (OHS_BIO304). This training is required for anyone that will be conducting work and/or research that requires the use of a

### Power curves - use of spinner anemometry. Troels Friis Pedersen DTU Wind Energy Professor

Power curves - use of spinner anemometry Troels Friis Pedersen DTU Wind Energy Professor Spinner anemometry using the airflow over the spinner to measure wind speed, yaw misalignment and flow inclination

### TRAFFIC ACCOMMODATION IN WORK AREAS

TRAFFIC ACCOMMODATION IN WORK AREAS TRAFFIC ACCOMMODATION IN WORK AREAS Copyright 2005 All rights reserved. Reproduction of this document in whole or in part by any means is prohibited, unless authorized

### Control of Allergies to Laboratory Animals

Health and Safety Policy Control of Allergies to Laboratory Animals UHSP/21/CALA/03 This document sets out in more detail the arrangements for compliance with University Health and Safety Policy at Budget

### Techniques to achieve wind comfort & wind loads on buildings and appurtenances

Vipac Engineers & Scientists Techniques to achieve wind comfort & wind loads on buildings and appurtenances including shades, verandahs, hoardings and walls. Mr Ian Jones, Managing Director Dr Seifu Bekele,

### Alberta Police Recruit Selection Standards

Alberta Police Recruit Selection Standards SUPPLEMENTAL VISION REPORT FORMS For Police Constable Applicants Alberta Solicitor General and Public Security Police Recruit Selection Standards Corneal Refractive

### Wind action on small sky observatory ScopeDome

Wind action on small sky observatory ScopeDome A.Flaga a, G. Bosak a, Ł. Flaga b, G. Kimbar a, M. Florek a a Wind Engineering Laboratory, Cracow University of Technology, Cracow, Poland, LIWPK@windlab.pl

### HOW TO HOLD THE SHOT

HOW TO HOLD THE SHOT Balance the shot in his hand so it is resting at the point where the fingers are connected to the palm of the hand. Keep their fingers together and allow their thumb to gently rest

### 628 Differential Pressure Decay Leak Tester

628 Differential Pressure Decay Leak Tester The 628 puts Uson s industry leading differential pressure decay sensitivity in your hands and in your budget with no compromise in quality, reliability, and

### AIR FLOW ANEMOMETER INSTRUCTION MANUAL

AIR FLOW ANEMOMETER INSTRUCTION MANUAL Thank you for purchasing our company Air Flow Anemometer. This manual provides relative information on how to use the Air Anemometer and warning in operation Please

### APPENDIX J HYDROLOGY AND WATER QUALITY

APPENDIX J HYDROLOGY AND WATER QUALITY J-1 Technical Report on Airport Drainage, Northern Sector Airport and Ordinance Creek Watershed / Preliminary Creek Constructed Natural Channel Culvert J-2 Preliminary

### WIND DATA REPORT. Vinalhaven

WIND DATA REPORT Vinalhaven January - December, 2003 Prepared for Fox Islands Electric Cooperative by Anthony L. Rogers May 12, 2004 Report template version 1.1 Renewable Energy Research Laboratory 160

### Agilent Dimension Software for ELSD User Manual

Agilent Dimension Software for ELSD User Manual Agilent Dimension Software for ELSD User Manual Agilent Technologies Notices Agilent Technologies, Inc. 2011 No part of this manual may be reproduced in

SPORTS & ORTHOPAEDIC SPECIALISTS Pre-Return to Throwing Protocol 2. Concentrate on all phases of proper throwing mechanics throughout the program. -Set Scapula -Elbow up -Stay on top of the ball -Perform

### Read this first. Zetasizer nano series Self installation and Quick start guide MRK825-02

! Read this first Zetasizer nano series Self installation and Quick start guide I N S T R U M E N T S MRK825-02 Zetasizer Nano series Self installation and Quick start guide MAN0383 Issue 1.1 July 2007

### On the Go Swing System Instruction Manual

On the Go Swing System Instruction Manual WARNING READ ENTIRE MANUAL BEFORE USE. THIS SWING IS NOT A TOY. THIS SWING IS ONLY TO BE USED BY TRAINED PERSONNEL, SUCH AS AN OCCUPATIONAL THERAPIST, PHYSICAL

### Water Rescue Course (Surface- and Swift- Levels I&II) Task Book

Water Rescue Course (Surface- and Swift- Levels I&II) Course Dates: Students Name: Lead Instructor: 2 Water Rescue Course (Surface and Swift Levels I&II) Course Completion At the end of the course, the

### Optimized Local Exhaust Solution for Working Place

Optimized Local Exhaust Solution for Working Place Case Study Dr. Daniel Gubler, AFC Air Flow Consulting AG Ventilation 2006 Conference Chicago, May 2006 AFC Air Flow Consulting AG Weinbergstrasse 72 CH-8006

### Surface Mount NTC Thermistors. Link: RT Tables. NST Series

FEATURES NEGATIVE TEMPERATURE COEFFICIENT FAST RESPONSE TO TEMPERATURE VARIATIONS MAKE THEM IDEALLY FOR TEMPERATURE SENSORS AND COMPENSATORS RoHS STANDARD EIA 0201, 0402, 0603 AND 0805 SIZES Compliant

### SURROGATE POWDER AND ASHRAE-110 TESTING OF A MULTI-PURPOSE ENCLOSURE FOR WEIGHING/SIEVING/FLUID BED DRYER APPLICATIONS

SURROGATE POWDER AND ASHRAE-110 TESTING OF A MULTI-PURPOSE ENCLOSURE FOR WEIGHING/SIEVING/FLUID BED DRYER APPLICATIONS By Chris Mento, Geoff Williams, Bryan Prince, Ray Ryan, Flow Sciences, Inc. Introduction

### University of Cambridge - Safety Office. Radioactive Substances (Unsealed Sources) Audit - complete checklist

SO Reference: IR/16-18 University of Cambridge - Safety Office Radioactive Substances (Unsealed Sources) Audit - complete checklist Department: Date of visit: People present: Senior RPS: Other RPSs: Head

### TF- & DM-Series. Turbineflowmeter

Turbineflowmeter .. are the ideal solution for measuring applications in liquids when high accuracy, very fast response times, compact design, high reliability are also required in continuous operation

### On the Go Swing System Instruction Manual

On the Go Swing System Instruction Manual WARNING READ ENTIRE MANUAL BEFORE USE. THIS SWING IS NOT A TOY. THIS SWING IS ONLY TO BE USED UNDER ADULT SUPERVISION. CONSULT WITH A CHILD S THERAPIST ON HOW

### Building 21 Roof Safety Assessment. Multi Story Building with large metal roof areas Exteral access required for window cleaning UOW01613

Roof Safety Survey GENERAL INFORMATION CAMPUS: Wollongong Campus BUILDING: 21 Early Start Facility DESCRIPTION: RISK ASSESSMENT # ROOF ACCESS: Multi Story Building with large metal roof areas Exteral access

### Old-Exam.Questions-Ch-14 T072 T071

Old-Exam.Questions-Ch-14 T072 Q23. Water is pumped out of a swimming pool at a speed of 5.0 m/s through a uniform hose of radius 1.0 cm. Find the mass of water pumped out of the pool in one minute. (Density

### Intramural Sports. Field Hockey Rules

Field Hockey Rules INCIDENTAL CONTACT IS POSSIBLE IN FIELD HOCKEY AND INJURIES ARE A POSSIBILITY. JAMES MADISON UNIVERSITY RECREATION ASSUMES NO RESPONSIBILITIES FOR INJURIES. BASIC FIRST-AID AND CPR WILL

### Americans with Disabilities Act and Curb Ramps

Americans with Disabilities Act and Curb Ramps Katherine Smutzer Standards Engineer, INDOT Purdue Road School Wednesday March 9, 2016 Two Items to Remember All curb ramps, sidewalks and sidewalk driveway

### Components for air preparation and pressure adjustment. OUT port position ( ) connected Rear side. of IN port. Air tank. directly.

Components preparation and pressure adjustment ABP Overview ABP is a component that enables boosting by s only up to twice primary pressure (.0MPa max.) in combination with using air tank but not using

### UHSE. Bath University HR Department UHSE. Safe Use of Fume Cupboards. Document Information

Bath University HR Department UHSE Document Information Author Revised By Debbie Robarts N/A Date 13-09-2016 Version 1 Status Approved UHSC 13-09-16 Copyright University of Bath This document can be used

### WRO University Regular Category WRO Bowling Game rules

WRO University Regular Category WRO Bowling Game rules Copyright World Robot Olympiad Association Ltd. 2015. 1. Game Description The name of this year s university regular category is WRO Bowling. This

### fermacell AESTUVER fire-protection boards

fermacell AESTUVER fire-protection boards Classification of the fire resistance of structural steel members R0498b Datum: P.O. Box 554-2665 ZN Bleiswijk Brandpuntlaan Zuid 16-2665 NZ Bleiswijk The Netherlands

### Design of a Solid Wall Transonic Wind Tunnel

Design of a Solid Wall Transonic Wind Tunnel David Wall * Auburn University, Auburn, Alabama, 36849 A solid wall transonic wind tunnel was designed with optical access from three sides to allow for flow

### A STUDY OF SIMULATION MODEL FOR PEDESTRIAN MOVEMENT WITH EVACUATION AND QUEUING

A STUDY OF SIMULATION MODEL FOR PEDESTRIAN MOVEMENT WITH EVACUATION AND QUEUING Shigeyuki Okazaki a and Satoshi Matsushita a a Department of Architecture and Civil Engineering, Faculty of Engineering,

### Customer Responsibilities. Important Customer Information Series Q-TOF LC/MS Systems Site Preparation Checklist

Thank you for purchasing an Agilent system. To get you started and to assure a successful and timely installation, please refer to this specification or set of requirements. Correct site preparation is