1 RD(H)20/25 Pressure-Reducing Regulator User Manual Read the complete manual before installing and using the regulator.
2 2 Safe Product Selection When selecting a product, the total system design must be considered to ensure safe, trouble-free performance. Function, material compatibility, adequate ratings, proper installation, operation, and maintenance are the responsibilities of the system designer and user. WARNING Users must be trained and equipped for the handling, use, and servicing of pressure products and systems. Users must contact their gas or liquid supplier for specific safety precautions and instructions. Gaseous media should be free of excessive moisture to prevent icing at high flow. Always wear the appropriate protective clothing, including safety glasses, gloves, etc., if required. Follow the applicable safety and maintenance procedures. Obey specific local regulations. Do not exceed the maximum inlet and outlet pressure rating of the product or its accessories. Operate within the temperature limits and any other conditions specified for the product. Do not drop or damage the product in any other way. This may negatively affect the performance of the product which can cause the product to malfunction. Venting fluids and gases can be dangerous. Vent to a safe environment away from people. Ensure adequate ventilation.
3 3 Contents Introduction... 4 Overview... 4 Standard Features... 4 Additional Options... 4 Oxygen Service... 4 Installation... 5 Points of Attention Before Installation... 5 Installation... 5 Dome Pressure Control... 6 External Feedback... 9 Operation Required Tools for Operation Points of Attention Before Operation Adjusting the Set Pressure Maintenance Required Tools for Maintenance Points of Attention Before Removal from the System Removal from the System Assembly Reference Data Disassembly Points of Attention Before Reassembly Reassembly RD(H)20 Series: Standard RD(H)25 Series: Standard RD(H)10 and RD(H)15 Series: External Feedback Testing Seat Leak Test Shell Leak Test Troubleshooting... 21
4 4 Introduction Overview - The RD(H)20 and RD(H)25 series are dome-loaded pressure-reducing regulators designed for the regulation of high pressure, high flow gases and liquids. - For pressure and temperature rating information refer to the Pressure Regulators, RHPS Series catalog, MS Note that seat seal material selection can limit the regulator operational pressure at elevated temperatures. WARNING Check that system pressures and temperatures do not exceed those stated on the regulator as this could result in product failure. Standard Features - Bolted construction - Stainless steel as standard - Fully serviceable - Diaphragm sensing - Balanced poppet - Pilot regulator - Dynamic regulation Additional Options The regulator is available with the following options: - External feedback to main regulator - External feedback to pilot regulator - Anti-tamper pilot regulator Oxygen Service - For more information about hazards and risks of oxygen enriched systems see the Swagelok Oxygen System Safety technical report (MS-06-13). - Cleaning and packaging to ensure compliance with product cleanliness requirements stated in ASTM G93 Level C is available. Refer to the Pressure Regulators, RHPS Series catalog, MS , for additional information.
5 5 Installation CAUTION Do not use the regulator as a shutoff device. A level of leakage across the regulator seat can occur during normal operation. Points of Attention Before Installation This regulator can be equipped with different options and connections. Before installing the regulator you should fully understand the functions of the supplied options and the suitability of your particular regulator for the intended application. - The preferred mounting position of the regulator is horizontal with the dome facing upwards per Fig 1. Alternative mounting positions may increase the risk of component wear. - It may be necessary to remove the regulator from the system during maintenance or service. Ensure that this is possible. - The regulator is suitable for gases and liquids dependent on the options selected. For liquid applications a pilot regulator should not be used. Ensure compatibility between the regulator s materials of construction and the system media. - Swagelok recommends the use of a non-venting pilot regulator when the process media is hazardous or toxic. Installation - Verify that the regulator, the connections, and its accessories are undamaged. - Verify that the regulator and its accessories are suitable for the system operating pressure and temperature and have suitable connections. - At the time of delivery any gauge ports may be plugged with blind fittings. Remove these and connect gauges if desired. - If inlet/outlet fittings are being used, assemble them to the regulator, per the manufacturer s instructions, prior to installing the regulator in the system. CAUTION Ensure all upstream tubing/pipework is clean and free from debris. Any swarf, lint, wire, etc. may damage the regulator, resulting in a seat leak. - Verify the flow direction of the system and mount the regulator accordingly. - Securely make the appropriate connections to the regulator in accordance with the procedures recommended by the connection manufacturer. - Ensure that the tubing/pipework and the regulator are adequately supported and that there is no stress on the connections. - Upstream and downstream shutoff valves should be installed in the system to facilitate servicing, maintenance, and troubleshooting of the regulator. WARNING When using an RDH20 or RDH25 with an inlet pressure higher than 2900 psig (200 bar), a safety valve must be installed in the outlet line to ensure the outlet pressure does not exceed 2900 psig (200 bar), which could result in product failure.
6 6 Dome Pressure Control The dome pressure of the regulator controls the outlet pressure. There are several methods available for supplying and controlling the dome pressure. - Integral pilot control. In this setup the dome-loaded regulator comes supplied with a pilot regulator as part of the assembly (Fig 1). The pilot regulator, fed from the system pressure, is manually operated to control the dome pressure (Fig 2). This setup is not suitable for liquid applications. - External dome control. In this setup the dome pressure is supplied from an independent source, such as a cylinder or main supply (Fig 3). This setup is suitable for liquid applications. - Electronic control. In this setup an electronic pilot regulator, fed from the system pressure, is used in conjunction with a pressure transducer to directly control the dome pressure (Fig 4). The outlet pressure of the main regulator will be limited by the outlet pressure of the electronic regulator. This setup is not suitable for liquid applications. - Ratio control. In this setup a ratio pilot regulator, fed from the system pressure, is used to control the dome pressure. The ratio pilot can be controlled by an electronic regulator and pressure transducer combination (Fig 5) or by an external dome feed. The ratio pilot outlet pressure is proportionally larger than its sensing pressure. This enables the main regulator to achieve full outlet pressure while being controlled from a low pressure supply. This setup is not suitable for liquid applications. The best performance will be achieved by allowing a small flow to continuously pass through the pilot regulator. This flow can either be vented through an orifice (Fig 3) or, in gas systems, fed back through an orifice into the downstream piping (Fig 2). This is usually referred to as dynamic regulation. NOTICE It is not recommended to place a gauge on the dome to set or check the outlet pressure. Because of forces in the regulator, the dome pressure will differ slightly from the outlet pressure. Place a gauge in the outlet line to set or check the outlet pressure. Integral Pilot Assembly Fig 1
7 7 Integral Pilot Control Schematic Pilot regulator Dynamic Regulation venting to the outlet line Dome regulator Fig 2 External Dome Control Schematic Pilot regulator Dynamic Regulation venting to atmosphere Dome regulator Cylinder or mains supply Fig 3
8 8 Electronic Control Schematic Electronic pilot regulator 4-20mA/0-10V 4-20mA/0-10V Pressure transducer Dome regulator Fig 4 Ratio Control Schematic Electronic pilot regulator 4-20mA/0-10V 4-20mA/0-10V Ratio regulator Pressure transducer Dome regulator Fig 5
9 9 External Feedback The purpose of external feedback is to provide a more accurate and stable regulation of the outlet pressure. This is achieved by sensing the outlet pressure downstream of the regulator and feeding it back to the regulator s sensing element. - The external feedback line is to be connected in a turbulence-free zone in the downstream piping, at a maximum distance of 5x the outside diameter of the downstream tubing/piping (Fig 6). - The tube size of the external feedback should be 3/8 in. or 1/2 in. or the metric equivalent. CAUTION When using a regulator with external feedback, ensure that the outlet line is connected to the external feedback port before applying pressure to the regulator. Failing to do so may lead to damage and non-functioning of the regulator and no pressure regulation will occur. CAUTION Never connect the external feedback line downstream of a shut-off valve. Doing so may lead to damage and non-functioning of the regulator and no pressure regulation will occur. External Feedback Schematic Dome pressure External feedback line Shutoff valve Shutoff valve O.D Inlet pressure Max. 5X O.D. Outlet pressure Fig 6
10 10 Operation Required Tools for Operation No tools are required for changing the set pressure on a standard regulator. Points of Attention Before Operation CAUTION The product can be hot or cold, depending on the environmental temperature and the process media temperature. Take the necessary precautions before operating or touching the product. - Stopping flow through the regulator by closing a downstream shutoff valve may result in a rise in outlet pressure above the set pressure. This is usually referred to as lock-up. This phenomenon does not indicate a problem with the regulator. - A decrease of the flow rate may result in a rise of the outlet pressure. An increase of the flow rate may result in a fall of the outlet pressure. This is usually referred to as droop. This phenomenon does not indicate a problem with the regulator. - A decrease of the inlet pressure may result in a rise of the outlet pressure. An increase of the inlet pressure may result in a fall of the outlet pressure. This is usually referred to as inlet dependency or Supply Pressure Effect (SPE). This phenomenon does not indicate a problem with the regulator. Adjusting the Set Pressure - The set pressure is the desired outlet pressure of the regulator. - To set the regulator, ensure that the supply pressure is greater than the required set pressure but does not exceed the maximum rating of the regulator. - The regulator must be able to flow in order for it to reduce the outlet pressure. 1. Partially open any downstream valve. This will allow minimal flow through the regulator when adjusting the set pressure, reducing media consumption during this process. 2. Ensure there is zero pressure in the dome. 3. Steadily open the supply valve to allow inlet pressure to the regulator. 4. To operate the regulator, turn the pilot adjustment knob clockwise to increase the set pressure. Turn the knob counterclockwise to reduce the set pressure. 5. To obtain the most accurate set pressure, final adjustment must be made while increasing the set pressure. If the desired outlet pressure is exceeded, reduce the pressure below this value then increase up to it. 6. Fully open the downstream valve to allow full flow during operation. 7. Once under flow conditions make any final set pressure adjustments per steps 3 and 4 if required. NOTICE The pilot regulator knob assembly is retained by a C-ring. When backing off the knob do not attempt to continue to unwind the knob once it has stopped. Doing so may damage the C-ring.
11 11 Maintenance WARNING Incorrect or improper repair or servicing of this product can cause serious personal injury and property damage. - All repairs, servicing, and testing of this product must be performed by competent personnel. - Following any maintenance of the regulator, it is recommended that the product be tested for operation and leakage. - The product should be checked periodically for proper and safe operation. It is the user s sole responsibility to determine the frequency of maintenance based on the application. - To reduce maintenance related system downtime to a minimum, either during commissioning or normal operation, Swagelok recommends having maintenance kits readily available on site. The need for maintenance kits is particularly important during the commissioning phase of a system installation due to residual assembly debris remaining in the system. Such debris can cause a seat leak in the regulator, resulting in components needing to be replaced. Required Tools for Maintenance Smooth-jawed vise Calibrated torque wrench up to 52 lbf ft (70 N m) 46 mm socket Appropriate open-ended wrenches for disassembling tube fittings Seat Mounting Tool RHPS-20-SEAT-TOOL RHPS-25-SEAT-TOOL Lubricant (included in kit) WL-8 1 Krytox 240 AC 2 10 mm hex drive Liquid leak detector C-ring pliers 1 Standard cleaned assemblies 2 ASTM G93 or SC11 cleaned assemblies Table 1
12 12 Points of Attention Before Removal from the System - Swagelok recommends removing the regulator from the system for servicing and maintenance. - Follow all local system safety and maintenance procedures when removing the regulator. WARNING Before removing a regulator from the system, to avoid personal injury, you must: Depressurize the system and dome. Purge the system to remove any residual system media left in the regulator. Always vent to a safe environment away from people and ensure there is adequate ventilation. CAUTION Check if the process media is hazardous or toxic. If required, take the necessary safety precautions to ensure a safe workspace and your personal safety. CAUTION The product can be hot or cold, depending on the environmental temperature and the process media temperature. Take the necessary precautions before operating or touching the product. Removal from the System 1. Isolate the regulator from all pressure sources by closing all appropriate upstream valves in the system. 2. With the pilot regulator set, open all appropriate downstream valves to allow pressure to vent from the regulator. WARNING Ensure all pressure on the inlet, outlet and dome has been fully vented. The accidental release of residual trapped pressure can cause serious personal injury. 3. Ensure appropriate lifting equipment is available to enable the regulator to be supported and handled once disconnected from the system. 4. Ensure that any external dome feed or external feedback connection is disconnected. 5. Disconnect and remove the regulator from the system.
13 13 Assembly Reference Data Item Component Name Kit Type(s) Torque Recommended Lubrication lbf ft (N m) (included in kit per Table 1) 1 Body plug C1, C2 52 (70) Lubricate threads 2 Body plug O-ring B1, B2, C1, C2 3 Poppet spring C1, C5 4 Poppet backup ring 1 A1, A2, B1, B2, C1 5 Poppet guide ring 2 B1, B2, C1, C2 6 Poppet O-ring A1, A2 1, B1, B2, C1, C2 2 Lubricate 7 Poppet A1, A2, B1, C1 RD(H)20-15 (20) 8 Seat A1, B1, C1 RD(H)25-18 (25) Lubricate threads 9 Seat O-ring A1, B1, B2, C1 10 Body N/A 11 Body plate C1 12 Body plate outer O-ring B1, B2, C1 13 Body plate inner O-ring B1, B2, C1 Lubricate 14 Retaining ring C1 15 Conical spring C1 16 Diaphragm plate C1 17 Diaphragm B1, B2, C1, C3 18 Dome plate N/A 19 Dome N/A 20 BSP blind plug O-ring B1, B2, C1 Wrap threads in 2 layers of NPT: 15 (20) 21 Blind plug N/A PTFE tape. Lubricate tape. BSP: 26 (35) Lubricate threads 22 Washer E1 23 Cap screw E1 52 (70) Lubricate threads 24 Parallel gasket B1, B2, C1 25 Bleed fitting (reduced orifice) N/A Per manufacturer instructions 26 Tube fitting N/A Per manufacturer instructions 27 Bleed tube N/A 28 Feed tube N/A 29 Pilot regulator N/A 30 Dome tube N/A 1 RD(H)20 series only 2 RD(H)25 series only Table 2 For more information on RHPS series maintenance kits, refer to the Pressure Regulators, RHPS Series catalog, MS
14 14 RD(H)20, RD(H)25 Series Exploded View Fig 7
15 15 Integral Pilot Regulator Assembly Exploded View Fig 8
18 18 Disassembly - The following instructions describe how to fully disassemble the regulator for the purposes of maintenance and repair. - Note that not all components listed appear in all regulator configurations. - Only disassemble the regulator as far as is required to replace the components supplied in the maintenance kit. - Discard all components being replaced. 1. If present remove the feed tube (28), dome tube (30), bleed tube (27), and pilot regulator (29). 2. Remove the body plug (1), poppet spring (3), and poppet (7) from the body (10). 3. Remove the body plug O-ring (2), poppet O-ring (6) and, if present, poppet backup ring (4) and guide ring (5) from the body plug (1) and poppet (6). 4. Using the seat insertion tool, remove the seat (8) and seat O-ring (9). 5. Remove the cap screws (23) to remove the dome (19), dome plate (18), diaphragm (17), and diaphragm plate (16). 6. Remove the retaining ring (14) to remove the body plate (11). For external feedback regulators remove the inner (13) and outer (12) body plate O-rings. Points of Attention Before Reassembly - Visually inspect all components for abnormal wear or damage. Replace components in case of doubt. - All parts must remain clean and undamaged before starting assembly. - Maintenance kit components will be supplied preassembled where practicable to aid reassembly. - Swagelok recommends replacing all O-rings removed during disassembly. - Swagelok recommends that dynamic O-rings should be lightly lubricated per Table 2. NOTICE All threaded components must be lightly lubricated per Table 2 before reassembly to avoid galling of threads.
19 19 Reassembly RD(H)20 Series: Standard 1. Fit the body plate (11) into the body (10) and retain with the retaining ring (14). 2. Fit the seat O-ring (9) into the body (10) and ensure that it is seated all the way round. 3. Lightly lubricate the seat threads (8) then insert the seat (8) into the body (10) using the seat insertion tool. Torque to 11 lbf ft (20 N m). Take care not to pinch the seat O-ring (9) or damage the seat (8) with the tool. 4. Fit the poppet O-ring (6) and, if present, backup ring (4) onto the poppet (7). Ensure they are oriented correctly per Fig Lightly lubricate the poppet O-ring (6) then insert the poppet (7) through the seat (8) and body plate (11). Take care not to damage either the seat (8) or poppet (7). 6. Place the poppet spring (3) into the poppet (7). 7. Fit the body plug O-ring (2) onto the body plug (1) and lightly lubricate the body plug threads. 8. Insert the body plug (1) into the body (10) over the poppet spring (3). Torque to 52 lbf ft (70 N m). 9. Place the diaphragm plate (16) onto the poppet (7). 10. Place the diaphragm (17) onto the diaphragm plate (16) and locate it in the body (10). 11. Place the dome plate (18) centrally onto the diaphragm (17) then cover with the dome (19). Orient the dome ports per Fig Lightly lubricate the cap screw threads (23) then use them and the washers (22) to secure the dome (19) to the body (10). Torque to 52 lbf ft (70 N m). 13. Install the feed tube (28), dome tube (30) and pilot regulator (29) into the ports on the inlet side of the body (10) per Fig Install the bleed tube (27) into the ports on the outlet side of the body (10) per Fig 8. Note that the bleed fitting (25) can be identified by its reduced internal orifice. 15. Make up all tube fittings (25, 26) per the manufacturers recommendations. RD(H)25 Series: Standard 1. Follow steps 1 and 2 of the RD(H)20 series standard reassembly procedure. 2. Lightly lubricate the seat threads (8) then insert the seat (8) into the body (10) using the seat insertion tool. Torque to 18 lbf ft (25 N m). Take care not to pinch the seat O-ring (9) or damage the seat (8) with the tool. 3. Fit the poppet O-ring (6) and guide ring (5) into the body plug (1). 4. Follow steps 5 through 15 of the RD(H)20 series standard reassembly procedure. RD(H)10 and RD(H)15 Series: External Feedback 1. Fit the inner (13) and outer (12) body plate O-rings onto the body plate (11). Lightly lubricate the inner body plate O-ring (13). 2. For size 20 regulators follow the RD(H)20 series standard reassembly procedure. 3. For size 25 regulators follow the RD(H)25 series standard reassembly procedure.
20 20 Testing Swagelok recommends that the regulator be tested for seat and shell leakage to atmosphere. A well performing regulator will not show any indication of leaking. If any evidence of a leak is identified this must be rectified. Any damaged components must be replaced. Seat Leak Test 1. Ensure there is sufficient supply pressure to the regulator to be able to perform the tests. 2. Ensure that there is zero pressure in the dome. 3. Maintain an inlet pressure of approximately 14.5 psig (1 bar) on the regulator and close the downstream shutoff valve. 4. Monitor the outlet pressure. An increase in pressure over time indicates a seat leak. 5. Repeat the procedure with the highest inlet pressure applicable for the regulator and system. Shell Leak Test 1. Maintain an inlet pressure of approximately 29 psig (2 bar) on the regulator and close the downstream shutoff valve. 2. Increase the outlet pressure to approximately 14.5 psig (1 bar). 3. Using liquid leak detector, check for bubbles at the dome to body interface and the body plug to body interface. 4. Repeat the procedure with the highest inlet and outlet pressure applicable for the regulator and system.
21 21 Troubleshooting Symptom Cause Remedy The outlet pressure creeps up, without adjusting dome pressure. A damaged poppet or seat. Replace the poppet and/or seat. Leakage around the body plug. A damaged O-ring. Replace the O-ring. Leakage between the body and the dome. Controlled pressure drops off sharply even when the flow is within regulator capabilities. The required outlet pressure cannot be reached. The outlet pressure rises too much when going from a dynamic to a static situation. The outlet pressure does not drop when the pressure in the dome is lowered. The outlet pressure has changed without adjusting the dome pressure. No pressure regulation occurs with an external feedback regulator. A damaged diaphragm. Insufficient torque on the cap screws. The system filter element is clogged. The inlet pressure to the regulator is not high enough. There is too much flow in the dynamic situation. The regulator is non-venting. Changes to the inlet pressure may result in changes to the outlet pressure. Changes to the flow may result in changes to the outlet pressure. The outlet line has not been connected to the external feedback port. Replace the diaphragm. Tighten the cap screws per Table 2. Replace the system filter. Ensure that the inlet pressure to the regulator is equal to or greater than the desired set pressure. A larger regulator or parallel regulator is required. Review application flow capacity and contact your local authorized sales and service center. A shutoff valve in the outlet line must be opened to reduce the outlet pressure. Maintain a constant inlet pressure to the regulator. See Points of Attention Before Operation about dependency. Maintain a constant flow through the regulator. See Points of Attention Before Operation about droop. Connect the outlet line to the external feedback port. See External Feedback for installation details. Table 3
24 Warranty Information Swagelok products are backed by The Swagelok Limited Lifetime Warranty. For a copy, visit swagelok.com or contact your authorized Swagelok representative. Swagelok, Snoop - TM Swagelok Company Krytox TM The Chemours Company 2018 Swagelok Company March 2018, Rev B MS-CRD-0182
PRS(TC)4,8 USER MANUAL Read the complete manual before installing and using the regulator. WARNING INCORRECT OR IMPROPER USE OF THIS PRODUCT CAN CAUSE SERIOUS PERSONAL INJURY AND PROPERTY DAMAGE. Due to
Installation, Operation and Maintenance Manual for Back Pressure Regulator Model 8860 2009 Groth Corporation IOM-8860 Rev. B 12541 Ref. ID: 95565 Page 2 of 13 Table of Contents I. INTRODUCTION 3 II. DESIGN
Installation, Operation, and Maintenance Manual Welker Constant Pressure Cylinder With Welker Magnetic Indicator (With Gravity Mixer) Model The information in this manual has been carefully checked for
1800C and 1800C-HC Series Service Regulators Installation Instructions www.elster-americanmeter.com General Information: The 1800C and 1800C-HC Regulators are available as Full Capacity Internal Relief
Model GP-2000 PRESSURE REDUCING VALVE Installation & Operation Manual Please read this bulletin thoroughly before using the pressure reducing valve, so that you may do so correctly and safely. Please carefully
Installation, Operation, and Maintenance Manual Welker Constant Pressure Cylinder With Welker Magnetic Indicator (Non-mixer) Model The information in this manual has been carefully checked for accuracy
Product Manual CVS Type 1301F and CVS Type 1301G Regulator Introduction This CVS Controls product manual includes instructions for the installation, adjustment, maintenance and parts ordering of the CVS
Before installation these instructions must be fully read and understood Installation and maintenance instructions for Series 93 Positive Pressure Pilot Operated Safety Relief Valves (POSRV). The intent
INSTALLATION INSTRUCTIONS CVS 67CFR Pressure Reducing Instrument Supply Regulator INTRODUCTION The CVS Controls 67CFR Filter regulator is a pressure reducing supply regulator typically used for pneumatic
172-65205MA-03 (DC5A) 19 June 2015 ISO 9001/ ISO 14001 Manufacturer Kakogawa, Japan is approved by LRQA LTD. to ISO 9001/14001 Cyclone Separator Trap for Air DC5A Copyright 2015 by TLV Co., Ltd. All rights
DS05C,D,G Dial Set Pressure Regulating Valves APPLICATION The Honeywell DS05C,D,G Dial Set Pressure Regulating Valve is a high quality pressure regulating valve that maintains a constant outlet pressure
Model VR6 System Installation, Operation & Maintenance General: All Archer Instruments chlorination systems are carefully designed and tested for years of safe, accurate field service. All Archer Instruments
II stage R2 Ice/ Special, II stage R 1 Pro DOWNSTREAM 2 nd STAGE REGULATOR Service and Repair Manual Introduction Safety Precautions...4 General Procedures, Maintenance Schedules...5 Initial Inspection
Outstanding performance in extremely low pressure and low pressure ranges from 0.003 to. Realizing high performance, energy saving, and compact size. Realize precise pressure control in a pressure range
Fisher Controls Instruction Manual Type S301 & S302 Gas Regulators October 1981 Form 5180 WARNING Fisher regulators must be installed, operated, and maintained in accordance with federal, state, and local
Self-operated Pressure Regulators Differential Pressure Regulators (opening) Type 42-20 Type 42-25 Type 42-20 Differential Pressure Regulator Type 42-25 Differential Pressure Regulator Mounting and Operating
INSTRUCTION MANUAL HPB25 Hydraulic Paving Breaker Read and understand all of the instructions and safety information in this manual before operating or servicing this tool. Register this product at www.greenlee.com
Oxygen Usage Best Practice Guide 1. Introduction Oxygen enriched systems possess a risk of fire and explosion since ignition and combustion hazards are present in all oxygen systems, and oxygen related
Installation Sheets Manual 121 Gas Combustion Combination Controls and Systems Section G Technical Bulletin GM Issue Date 0297 GM Series Dual-Block Multi-Function Gas Control Valves Figure 1: GM Series
Models 461-S, 461-8S and 461-12S Regulators R-1330 Rev. 7 461-S, 461-8S and 461-12S Regulators The Sensus Models 461-S, 461-8S and 461-12S are balanced valve, spring type regulators designed for distribution
HAYWARD FLOW CONTROL Series PBV Back Pressure Valve and Series RPV Pressure Relief Valve INSTALLATION, OPERATION, AND MAINTENANCE INSTRUCTIONS Page 1 of 20 Page 2 of 20 TABLE OF CONTENTS Safety Warnings
Reduce pressure zone device suitable for high and medium hazard rated applications BSP screwed connections Features General application The RP03 provides protection from both backsiphonage and backpressure
CONTENTS Float Operated Level Controllers IM0015 Nov. 2014 PAGE Introduction 1 Scope 1 Description 1 Specification 1 Control Installation 2 INTRODUCTION Side Mount Back Mount Prior to installing, the instructions
D05T Compact Design Pressure Regulating Valves FEATURES PRODUCT DATA Non-corroding unitized cartridge contains all working parts and is easily replaceable. Includes built-in strainer and thermal bypass.
Model B1 Accelerator with Integral Accelo-Check Bulletin 323 Rev. E Bulletin 323 Rev. E Instructions for Installation, Operation, Care and Maintenance Features 1. Quickens the operation of dry pipe valves.
December 4, 2009 Dry Systems 123a 1. DESCRIPTION The Anti-flood Device is required when Viking accelerators are installed on dry systems according to Viking Model E-1 Accelerator Trim Charts. In the SET
WW-720 Pressure Reducing Control Valve (Size Ranges: 2-4 and 6-14 ) Installation Operation & Maintenance Page 1 of 6 1. DESCRIPTION The Model 720 Pressure Reducing is an automatic control valve (powered
Serial No. H-V024-E-7 Needle valve User s Manual Contents (1) Be sure to read the following warranty clauses of our product 1 (2) General operating instructions 2 (3) General instructions for transportation,
Instruction Sheet Pressure Dump Valve Service Kit for Series 00 Units. Overview The Nordson pressure dump valve is used to relieve hydraulic pressure instantly in Series 00 applicator tanks when the unit
CARTRIDGE FILTERS TECHNICAL MANUAL MT 080 Installation, commissioning and maintenance instructions 08/02 Edition 1 2 CONTENTS 1.0 PAGE INTRODUCTION 1.1 MAIN FEATURES 1.2 OPERATION 1.3 CLOSING OF HEAD WITH
Model 420-HY Pressure Regulating Hydrant Valve INSTALLATION OPERATION MAINTENANCE 1. Safety First BERMAD believes that the safety of personnel working with and around our equipment is the most important
172-65260m-05 (S-COS/S-COSR Pressure Reducing Valve) 27 October 2008 ISO 9001/ ISO 14001 Manufacturer Kakogawa, Japan is approved by LRQA LTD. to ISO 9001/14001 Pressure Reducing Valve for Steam S-COS-16
Welker Pitot Probe Model PP-1, PP-1W, PP-2, & PP-3 The information in this manual has been carefully checked for accuracy and is intended to be used as a guide for the installation, operation, and maintenance
Hoffman Specialty Regulators Regulators Pressure and/or Temperature Operated Regulators Series 2000 The Hoffman Specialty Series 2000 consists of main valves, pilot valves, wells and hardware kits. They
Siemens Industry, Inc. INSTALLATION AND SERVICE INSTRUCTION SD40H Rev 10 June 2012 Supersedes Rev 9 Model 40H Nullmatic Pressure Regulators INTRODUCTION The Model 40 Nullmatic Pressure Regulator, shown
INLET PRESS TAP WHITE-RODGERS 36E93-304 Delay-Opening Combination Gas Valve INSTALLATION INSTRUCTIONS Operator: Save these instructions for future use! FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY
Halsey Taylor Owners Manual 4410 Freeze Resistant Tubular Fountain STOP! PLEASE READ THE FOLLOWING INFORMATION. ITALLATION ITRUCTIO FOR THE 4410FR FTN. WITH 97243C SINGLE VALVE CONTROL ASSEMBLY ARE LOCATED
P/N 126905-01 Rev. B 11/2016 INSTALLATION INSTRUCTIONS MANUAL ON/OFF SAFETY VALVE/PILOT KIT MODEL GA9050A-1 (F0235) For All Single, Dual and Triple Burner Natural and Propane/LP Gas Logs P126905-01 For
FAILURE TO READ AND FOLLOW ALL INSTRUCTIONS CAREFULLY BEFORE INSTALLING OR OPERATING THIS CONTROL COULD CAUSE PERSONAL INJURY AND/OR PROPERTY DAMAGE. DESCRIPTION The 36H series combination gas valve is
Instruction Manual - Diaframless TM Ejector Chlorine, Sulfur Dioxide and Ammonia - 1-122.6010.6 These instructions describe the installation, operation and maintenance of the subject equipment. Failure
Dive Rite RG 1200 Regulator Service and Repair Manual Page 1 Text and Photography by Pete Nawrocky Copyright ( ) 1999-2000, Lamartek, Inc., dba Dive Rite RG1200 Service and Repair Manual First Stage.........................................
1181250/1 IM-P118-05 ST Issue 1 PV4 and PV6 Piston Valves Installation and Maintenance Instructions 1. Safety information 2. General product information 3. Installation 4. Commissioning 5. Operation 6.
COMBINATION AIR RELEASE DEGASSING (CARD) VALVES INSTALLATION AND MAINTENANCE MANUAL SPECIFICATIONS: The CARD series air valves are available in 3 pipe sizes, 1, 2 and 4 NPT or socket. Maximum inlet pressure
Page 1 of 10 1. PRODUCT DESCRIPTION The Viking Model E-1 Accelerator is a quick-opening device. When installed with the required external Anti-flood Device, the assembly is designed to increase the operating
Un-Pressurized Orefice Fittings FIO EZ Parts List and Operation Instructions TECHNICAL MANUAL Dn 2-6 Class 150-600 Lbs US US 2 FIO EZ - MT 108-US - 05-2016 FIO EZ Important Instructions US Pietro Fiorentini
STORAGE INSTRUCTIONS Until it is time to install a new or reconditioned valve on the car, the valve must be kept in its original packaging in order to protect it from dirt and damage. INSTALLATION INSTRUCTIONS
ADI 1219-M Certified ISO 9000 1600 Series Dual-Range Flowmeters INSTALLATION AND OPERATION INSTRUCTIONS Before Installing or Operating, Read and Comply with These Instructions Controls Corporation of America
Page 1 of 13 1. Description The Viking 2 Model G-2000 Dry Valve Riser Assembly consists of a small profile, light weight, pilot operated valve that is used to separate the water supply from the dry sprinkler
0685255/1 IM-P068-47 ST Issue 1 TD45 Thermodynamic Steam Trap Installation and Maintenance Instructions 1 General safety information 2 General product information 3 Installation 4 Commissioning 5 Operation
Installation Instructions S65-135 (Circular) S65-136 (Semi-Circular) Air Valve Retrofit For Non-Sectional Classic Washfountain Table of Contents.......................2-6 Metering Air Valve Parts List....................6
250C-IG COMPRESSOR KIT 12V PART NO. 25050 250C-IG COMPRESSOR KIT 24V PART NO. 25058 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual
NATURAL GAS TO PROPANE CONVERSION KIT ALPKT57- INSTALLATION INSTRUCTIONS PROPANE CONVERSION KIT SAFETY... INSTALLATION REQUIREMENTS... Tools and Parts... LP Gas Requirements... Table of Contents INSTALLATION
250C-IG COMPRESSOR KIT 12V PART NO. 25050 250C-IG COMPRESSOR KIT 24V PART NO. 25058 IMPORTANT: It is essential that you and any other operator of this product read and understand the contents of this manual
INSTRUCTION MANUAL CVS P37 LP Gas Reducing Regulator The CVS Controls P37 Regulator is a non-relieving, pressure reducing regulator suitable for use in LP gas applications (Natural Gas and Propane). As
5041050/3 IM-P504-04 CH Issue 3 ML3M Monnier Miniature Compressed Air Lubricator Installation and Maintenance Instructions 1. Safety information 2. General product information 3. Installation and commissioning
48011HW NATURAL GAS TO PROPANE CONVERSION KIT 58HDX, 359AAV, PG9YAB, PG9YAA Installation Instructions SAFETY REQUIREMENTS Installing and servicing heating equipment can be hazardous due to gas and electrical
Catalogue No. YT30 090 HW Operation and Maintenance Manual ABOUT THE ZERO HEAD SPACE EXTRACTOR The Millipore Zero Head Space Extractor (ZHE) meets the U.S. EPA'S Toxicity Characteristics Leaching Procedure
ADI 0453A Certified ISO 9001:2000 453 Series Steam Heated Vaporizing Regulator INSTALLATION AND OPERATION INSTRUCTIONS Before Installing or Operating, Read and Comply with These Instructions Controls Corporation
MMR Air Mask With with Quick-Connect Hose Upgrade Kits P/N 10025120 Slide to Connect P/N 10050038 Slide to Connect w/ Solid Cover P/N 10038666 Push To Connect P/N 10050037 Push To Connect w/ Solid Cover
Instructions Parts List STAINLESS STEEL, WATERBASE COMPATIBLE Back Pressure Regulator 308401E For use in circulating systems to provide regulated back pressure to spray gun(s) and to maintain proper system
Instruction Manual D100343X012 Type 1367 November 2017 Type 1367 High-Pressure Instrument Supply System with Overpressure Protection TYPE 252 FILTER 2ND-STAGE TYPE 67CF FILTER-STYLE REGULATOR INLET TYPE
INSTRUCTION MANUAL Inert Air (N2) Systems Manual N2-MANUAL 2.10 READ AND UNDERSTAND THIS MANUAL PRIOR TO OPERATING OR SERVICING THIS PRODUCT. GENERAL INFORMATION Positive pressure nitrogen gas pressurizing
September 25, 2013 Pressure Regulation 537a 1. Description The Model B-3 Pilot Operated Pressure Control Valve is a factory assembled unit. The unit consists of a Model J-2 Halar coated Flow Control Valve,
APCO ARV CLEAN WATER AIR RELEASE VALVES Model 50A Instruction D12013 February 2017 Instructions These instructions provide installation, operation and maintenance information for APCO ARV Clean Water Air
Air Consumption 70% Down New Product Precision Regulator Air Saving Type RPE Series PRECISION REGULATOR RPE SERIES Large Air Saving CC-1072A Air Consumption 70% Down. New Type Eco-friendly Precision Regulator
Model 0 PFM Series Regulator Technical Bulletin Model 0 PFM Series Regulator 0 Elster American Meter The 0 PFM Series regulators are designed to control natural gas, air, nitrogen, carbon dioxide, propane
January 6, 2012 Preaction 348a 1. Description Viking supervised Surefire Preaction Systems utilize the Viking G-6000P Valve. The small profile, lightweight, pilot operated Viking G-6000P Valve comes complete
ADI 3202C Certified ISO 9001 623 Series Dome Load Regulators INSTALLATION AND OPERATION INSTRUCTIONS This Equipment is intended to be installed and operated by trained personnel. Before Installing or Operating,
PULSAR 5000 SERIES OPERATING & INSTALLATION INSTRUCTIONS SERIES 5000 PLEASE READ CAREFULLY BEFORE INSTALLING Please Note: Ranges above 500mbar are designed and manufactured in accordance with sound engineering
Installation Instructions GM-7000 Issue Date November 9, 2012 GM-7000 Series CE Approved Gas Control Valve Installation IMPORTANT: These instructions are intended as a guide for qualified personnel installing
38467.03 www.caleffi.com Pre-adjustable filling units Copyright 01 Caleffi 3 Series Function The automatic filling valve is a device consisting of a pressure reducing valve with compensating seat, visual
EXD SERIES PRESSURE DIFFERENTIAL SWITCHOVER SYSTEM INSTALLATION AND OP ER A TION IN STRUC TIONS Before Installing or Operating, Read and Comply with These Instructions IMD0611B 6.2012 Certified ISO 9001
Installation Instructions For Flat Seated Bolted Type RAH Series Disk Holders RA Series Rupture Disks 1. WARNING a) Read the complete instructions before attempting to install the rupture disk and holder
Your consent to our cookies if you continue to use this website.